An economizer display takes advantage of the fact that refrigeration systems have increasing efficiencies at increasing pressures and temperatures. The power the gas compressor needs is strongly correlated to both the ratio and the difference, between the discharge and the suction pressures (as well as to other features like the refrigerant's heat capacity and the type of compressor). Low temperature systems such as freezers move less fluid in same volumes. That means the compressor's pumping is less efficient on low temperature systems. This phenomenon is notorious when taking in account that the evaporation temperature for a walk-in freezer at −20 °F (−29 °C) may be around −35 °F (−37 °C). Systems with economizers aim to produce part of the refrigeration work on high pressures, condition in which gas compressors are normally more efficient. Depending on the application, this technology either allows smaller compression capacities to be able to supply enough pressure and flow for a system that normally would require bigger compressors, increases the capacity of a system that without economizer would produce less refrigeration, or allows the system to produce the same amount of refrigeration using less power.