When the outside air's dry- and wet-bulb temperatures are low enough, a water-side economizer can use water cooled by a wet cooling tower or a dry cooler (also called a fluid cooler) to cool buildings without operating a chiller. They are historically known as the strainer cycle, but the water-side economizer is not a true thermodynamic cycle. Also, instead of passing the cooling tower water through a strainer and then to the cooling coils, which causes fouling, more often a plate-and-frame heat exchanger is inserted between the cooling tower and chilled water loops.