This same meter has been modified or installed in modified sockets and used for two wire, 120 volt services (relabeled as 2W on the meter face). The modification places the two half coils in series such that a full coil is created. In such installations, the single element meter is Blondel compliant. There is also a three wire 240/480 volt version that is not Blondel compliant. Also in use are three phase meters that are not Blondel compliant, such as forms 14S and 15S, but they can be easily replaced by modern meters and can be considered obsolete.