To operate in this cycle, the desiccant is required to absorb moisture from air coming off of the coil that is colder and about 98% RH and to desorb moisture to air that is warmer and at a lower RH. The desiccant is regenerated by the vapor pressure differential inherent in the RH differences rather than heat or temperature difference. Desiccants that have a moisture sorption isotherm of the type shown in Figure 3 (Type III) are common, such as many formulations of silica gel. Type III desiccants absorb little moisture below 70% RH but many will take up more than their own weight in water from the air when presented with over 90% RH. The absorption isotherm is very steep between 90 and 100% RH. Desiccants of Type III have plenty of potential for the cycling of moisture from the air off of the coil, around 98% RH, over to the return air stream, typically around 50% RH.