The psychrometric chart depicts the changes of the cycle to the standard air conditioning cycle. First, the end state point 4 for air from the wheel represents a latent ratio increase (moisture removal) to about 45%, as opposed to the 25% of the typical coil shown. Secondly, the air quality delivered by the cycle is much dryer, about 55% RH (state point 4), rather than 98% with the standard coil (state point 4'). Third, this is accomplished with a higher average evaporator temperature. Compare the midpoint of the evaporator's temperature, line 1 to 4’, to the midpoint of the Cromer cycle's evaporator's temperature, line 2 to 3. These lines represent the work done by the coil on the air stream (its change in enthalpy). This is significant because, given a constant condenser temperature and equivalent change in enthalpy, the higher the evaporator coil temperature, the more efficient is the Carnot refrigeration cycle and the greater the energy efficiency a particular system can deliver.