Air lock problems often occur when one is trying to recommission a system after it has been deliberately (for servicing) or accidentally emptied. Take, for example, a central heating system using a circulating pump to pump water through radiators. When filling such a system, air is trapped in the radiators. This air has to be vented using screw valves built into the radiators. Depending on the pipe layout – if there are any upside down 'U's in the circuit – it will be necessary to vent the highest point(s). Otherwise, air lock may cause waterfall flow where the loss of hydraulic head is equal to the height of airlock; If the hydraulic grade line drops below the output of the pipe, the flow through that part of the circuit would stop completely. Note that circulating pumps usually do not generate enough pressure to overcome air locks.