当前位置：网站首页 > 新闻中心 > 行业新闻
  • 排烟防火阀和防火阀的区别
  • 本站编辑：杭州逸捷暖通设备有限公司发布日期：2019-11-23 21:45 浏览次数：


Difference between smoke fire damper and fire damper


(1) smoke and fire damper:


It is installed on the pipe of smoke exhaust system, which is generally closed at ordinary times. It is opened manually or electrically in case of fire, which plays the role of smoke exhaust. When the flue gas temperature in the exhaust pipe reaches 280 ℃, its electric smoke opening function is usually commanded by the control center or a simple smoke detector. Simply put: the fire control valve is normally open, and the temperature in the air duct is too high to set the closing valve to prevent the fire spreading.


The smoke fire damper is normally closed. When the smoke in the zone exceeds the standard, the control device instructs it to open the smoke exhaust. When the temperature in the smoke exhaust pipe exceeds 280oc, the fire cannot be discharged to other zones, so the valve will automatically "re close" to avoid the fire leading to other zones.


(2) fire damper:


The fire damper is applicable to the ventilation and air conditioning system. In addition to the fire damper used in the kitchen exhaust system of public buildings, the operating temperature is 150 ℃, and the operating temperature of the fire damper used in the general ventilation and air conditioning system is 70 ℃.


The fire damper is applicable to the pipes of ventilation, air conditioning or smoke exhaust system.



When selecting valves, attention shall be paid to the functions of the valves, such as normally open or normally closed, automatic close open, manual close open, manual reset, remote control, etc.


If the valve is linked with the fan, double micro switch device shall be selected.


Guangzhou kangmeifeng is a professional manufacturer of fire damper production line. It has developed and produced fire damper production line that meets 3C requirements and uses fire damper made by kangmeifeng fire damper production line. We promise to ensure that it passes 3C certification of fire damper.


Author: air duct manufacturer: Guangzhou kangmeifeng


Link: https://www.jianshu.com/p/c545a212cc1f


Source: Jianshu


The copyright belongs to the author. For commercial reprint, please contact the author for authorization. For non-commercial reprint, please indicate the source.