One that the most typical problems in household electric circuits is the overloading of the electric outlets. The variety of electrical outlets on a 15-amp circuit is restricted for safety and security reasons and also according come the maximum loading capacity of 15-amp breakers. So, how numerous outlets exactly can you have on a 15-amp circuit?

You have the right to install a best of 8 electrical outlets top top a single 15-amp circuit. The National electrical Code, or NEC, boundaries the constant load volume to 80% the the rated total load of a breaker. This limitation works out to a general dominion of 1 outlet every 1.5-amps of the circuit breaker.

You are watching: How many outlets can you put on a 15 amp breaker

A circuit breaker the keeps tripping indicates that the load on the circuit above the breaker’s capacity. The NEC boundaries the number of outlets on any circuit, 15-amps or otherwise. Let’s venture into the thinking behind the number of outlets enabled on a 15-amp circuit and also why you need to stay within this boundaries.


To check out this video clip please allow JavaScript, and also consider upgrading come aweb browser thatsupports HTML5 video

Why home Inspections room Important
How numerous Outlets have the right to You have Per Circuit?

The NEC walk not enable for a circuit to operation at the complete capacity the the circuit breaker continuously due to the fact that this amount of current going through the wiring every the time deserve to pose some serious safety and security risks.Running at complete capacity will cause the wiring in the circuit heating up, bring about the insulation about wires melt or coming to be compromised. The consequence of this is that brief circuits have the right to result, leading to fire or life-threatening electric shock.You are permitted to operation your circuits for brief periods at the maximum volume of the circuit breaker, yet not continuously. Typically, the NEC refers to a brief time together being 3-hours or less; much longer than this, you will be contravening the electric code and taking unnecessary threats with her home and your family.

Another factor that the border is 80% of the complete capacity of the circuit breaker is that the NEC accounts for world who overload electrical outlets to increase the variety of devices powered from a solitary outlet.Using the following formula, you can determine how countless outlets you have the right to have ~ above a 15-Amp circuit to continue to be within the 80% pack limit ~ above the circuit.(15-Amps x 0.8) / 1.5 = 8 OutletsSome multi-plug or extender plug manufacturers put safety mechanisms right into their multi-plugs, but others don’t. This plugs deserve to overload a circuit and break the electrical code by to run a continuously higher amperage 보다 the regulated 80% capacity v the circuit breaker.

How to recognize You are Overloading the Circuit

https://www.youtube.com/watch?v=h6d7VeRpSJgVideo can’t be loaded since JavaScript is disabled: How plenty of Lights ~ above a 15A Circuit Breaker? calculate Wattage for 15 Amp Circuit & variety of Fixtures (https://www.youtube.com/watch?v=h6d7VeRpSJg)

Besides the evident symptom that a typically tripping 15-amp circuit breaker, exactly how do you know if you overload the circuit with too plenty of devices running simultaneously?You deserve to ascertain the price by law some straightforward math. The unit Amps equates to Watts split by Volts. In many of ours homes, we room running 120-volts AC, therefore the voltage is known. Usage the adhering to formula to identify the maximum number of Watts that we should be running on the circuit.15-Amps = watt / 120-VoltsWatts = 15-Amps x 120-volts

Maximum watt = 1800-WattsThis formula provides us the preferably wattage pack for a solitary circuit. However, we space not allowed to exceed 80% the the capacity of the circuit breaker. You can calculate this as:1800 x 0.8 = 1440-WattsOur calculation shows that the preferably wattage ~ above the circuit for an extended time is 1440-Watts. If you include up the watt of every an equipment connected to each outlet on the circuit, the complete wattage need to be less than 1440-Watts.

Each outlet should not be drawing an ext than 1.5-Amps the current, therefore the wattage on every outlet have the right to be figured out as follows.Watts = 1.5-Amps x 120-VoltsMaximum watts per outlet should be 180-WattsExceeding this maximum wattage on an individual outlet will conveniently increase the current demand top top the circuit breaker over the 80% capacity regulation.

Does 15 or 20 Amp Have much more Outlets?

The same principles apply to calculating a 20-Amp circuit. A 20-Amp circuit is merely rated come handle more current throughput than a 15-Amp circuit.The same 80% that the maximum capacity of the circuit breaker applies to the 20-Amp circuit, which means that the maximum variety of outlets that deserve to be top top this circuit is 10. Therefore a 20-Amp circuit have the right to have an ext outlets than a 15-Amp circuit.Using the exact same rule-of-thumb guideline of 1 outlet because that each 1.5-Amps that the circuit breaker rating, you deserve to conclude that:(20-Amps x 0.8) / 1.5 = 10 Outlets

Can You have Outlets and Lights on The exact same Circuit?

Technically, that is possible to location outlets and lights top top the very same circuit. The circuit breaker does no distinguish in between outlets and also light fittings; the sees just the present draw.If you include light fittings top top an outlet circuit, you must diminish the number of outlets you placed on the circuit through the number of light fittings friend add. Because that example, if you add two irradiate fittings to a 15-Amp circuit, the maximum variety of outlets you have the right to have on the circuit would be 6.Even despite you can add light fittings ~ above an outlet circuit, the is normally not an embraced practice because that the circuit breaker panel’s business purposes and also safety. It becomes a safety issue if you do not understand which outlets and lights space on which circuit.For this reason, the wiring for dwellings generally remains with the rule of keeping outlets ~ above one circuit and also light fittings on a different circuit.

In particular instances, the NEC’s infringement is to have actually outlets and also lights on the very same circuit. Because that example, in bathrooms and also for above-counter outlets in kitchens intended for little kitchen appliances.While you have the right to wire lights to an outlet circuit, you will require to examine the NEC and also your regional stipulations for this practice before you carry out this configuration. As mentioned, over there are restrictions to this practice, relying on the room wherein you desire to have this done.The basic feeling is that mixing outlets and also lights unnecessarily complicates the wiring system, which is no encouraged.


The variety of electrical outlets on a 15-Amp circuit is a preferably of 8 to save within the restrictions of the electric code, which claims that the circuit breaker must not be operation at much more than 80% that capacity.The same 80% volume rule applies to 20-Amp circuits, wherein the maximum number of outlets is 10. If friend are came to that the number of outlets on a circuit is more than these limitations, you must consult a default electrician come verify the compliance of her circuit.

See more: One Disadvantage Of A Database System Over Previous Data Management Approaches Is Increased Costs

ReferencesHow numerous Outlets top top a 15 Amp Circuit Breaker?Can girlfriend mix lights and receptacles on the same circuit?keolistravelservices.com is owned and operated by hobtration Miles is a participant in the Amazon services LLC Associates Program, an affiliate declaring program design to administer a way for sites come earn proclaiming fees by advertising and linking to Amazon.com. Keolistravelservices.com also participates in affiliate program with various other affiliate sites. Hobtration Miles is compensated because that referring traffic and business to this companies.