Carefully. Flammable Refrigerant Used.''.  fire and the steps to use flammable
                                                                     (f) Attach on the exterior of the           refrigerants safely.
                                                                      refrigeration equipment: ``This           Room occupants should evacuate the space
                                                                      equipment is intended for use in           immediately following the accidental
                                                                      commercial, industrial, or institutional   release of this refrigerant.
                                                                      occupancies as defined in the Safety      Personnel commissioning, maintaining,
                                                                      Standard for Refrigeration Systems, ANSI/  repairing, decommissioning and
                                                                      ASHRAE 15''.                               disposing of appliances with this
                                                                     (g) Attach on the exterior of the           refrigerant should obtain training and
                                                                      shipping carton: ``CAUTION--Risk of Fire   follow practices consistent with Annex
                                                                      or Explosion. Dispose of Properly In       HH of UL 60335-2-40.3 5
                                                                      Accordance With Federal Or Local          CAA section 608(c)(2) prohibits
                                                                      Regulations.''.                            knowingly venting or otherwise
                                                                     (h) The instructions shall include the      knowingly releasing or disposing of
                                                                      following warnings as necessary:.          substitute refrigerants in the course
                                                                     a. ``WARNING: Ensure all ventilation        of maintaining, servicing, repairing or
                                                                      openings are not obstructed.''.            disposing of an appliance or industrial
                                                                                process refrigeration.
                                                                                Department of Transportation
                                                                                requirements for transport of flammable
                                                                                gases must be followed.
                                                                                Flammable refrigerants being recovered
                                                                                or otherwise disposed of from
                                                                                residential and light commercial air
                                                                                conditioning appliances are likely to
                                                                                be hazardous waste under the Resource
                                                                                Conservation and Recovery Act (RCRA)
                                                                                (see 40 CFR parts 260 through 270).
                                                                          b. ``WARNING: Do not use mechanical
                                                                           devices or other means to
                                                                           accelerate the defrosting process,
                                                                           other than those recommended by the
                                                                           manufacturer.''.
                                                                     c. ``WARNING: Do not damage the
                                                                      refrigerant circuit.''.
                                                                     Equipment must have distinguishing red
                                                                      (Pantone[supreg] Matching System (PMS)
                                                                      #185 or RAL 3020) color-coded hoses and
                                                                      piping to indicate use of a flammable
                                                                      refrigerant. The laboratory equipment
                                                                      shall have marked service ports, pipes,
                                                                      hoses and other devices through which
                                                                      the refrigerant is serviced. Markings
                                                                      shall extend at least 1 inch (25mm) from
                                                                      the servicing port and shall be replaced
                                                                      if removed.
                                                                     Equipment must use no more than 150 g of
                                                                      R-1150 in each refrigerant circuit using
                                                                      this refrigerant.
--------------------------------------------------------------------------------------------------------------------------------------------------------
\1\ The Director of the Federal Register approves this incorporation by reference (5 U.S.C. 552(a) and 1 CFR part 51). You may inspect a copy at the
  U.S. EPA or at the National Archives and Records Administration (NARA). Contact the U.S. EPA at: EPA Docket Center, WJC West Building, Room 3334, 1301
  Constitution Avenue NW, Washington, DC 20004, www.epa.gov/dockets,<PHONE_NUMBER>. For information on the availability of this material at NARA, email
  [email protected], or visit www.archives.gov/federal-register/cfr/ibr-locations.html.

\2\ You may obtain this material from: American Society of Heating, Refrigerating and Air-Conditioning Engineers (ASHRAE), 180 Technology Parkway NW,
  Peachtree Corners, Georgia 30092; phone:<PHONE_NUMBER>; website: www.ashrae.org.
\3\ You may obtain this material from: Underwriters Laboratories Inc. (UL) COMM 2000; 151 Eastern Avenue; Bensenville, IL 60106; phone:<PHONE_NUMBER>;
  email: 2000.com">[email protected]2000.com; website: https://ulstandards.ul.com/ or www.comm-2000.com.
\4\ ANSI/ASHRAE Standard 15-2019. Safety Standard for Refrigeration Systems, including all addenda published as of July 28, 2022.
\5\ UL 60335-2-40, Standard for Household And Similar Electrical Appliances--Safety--Part 2-40: Particular Requirements for Electrical Heat Pumps, Air-
  Conditioners and Dehumidifiers, 3rd edition, Dated November 1, 2019.
\6\ UL 61010-2-011, Safety Requirements for Electrical Equipment for Measurement, Control, and Laboratory Use--Part 011: Particular Requirements for
  Refrigerating Equipment, 2nd edition, dated May 13th, 2021.

                                 Fire Suppression and Explosion Protection Agents--Acceptable Subject to Use Conditions
--------------------------------------------------------------------------------------------------------------------------------------------------------
             End-use                     Substitute              Decision                   Use conditions                    Further information
--------------------------------------------------------------------------------------------------------------------------------------------------------
1. Total Flooding................  2-BTP.................  Acceptable Subject    Acceptable only for use in normally  This fire suppressant has a
                                                            to Use Conditions.    unoccupied spaces under 500 ft\3\.   relatively low GWP of 0.23-0.26
                                                                                and a short atmospheric lifetime
                                                                                of approximately seven days.
                                                                                This agent is subject to a TSCA
                                                                                section 5(a)(2) SNUR.
                                                                                For establishments manufacturing,
                                                                                installing and maintaining
                                                                                equipment using this agent, EPA
                                                                                recommends the following:
                                                                                This agent should be used
                                                                                in accordance with the safety
                                                                                guidelines in the latest edition
                                                                                of NFPA 2001, Standard on Clean
                                                                                Agent Fire Extinguishing Systems;
                                                                                \1\
                                                                                In the case that 2-BTP is
                                                                                inhaled, person(s) should be
                                                                                immediately removed and exposed
                                                                                to fresh air; if breathing is
                                                                                difficult, person(s) should seek
                                                                                medical attention;
                                                                                Eye wash and quick drench
                                                                                facilities should be available.
                                                                                In case of ocular exposure,
                                                                                person(s) should immediately
                                                                                flush the eyes, including under
                                                                                the eyelids, with fresh water and
                                                                                move to a non-contaminated area;
                                                                                Exposed persons should
                                                                                remove all contaminated clothing
                                                                                and footwear to avoid irritation;
                                                                                and medical attention should be
                                                                                sought if irritation develops or
                                                                                persists;
                                                                                Although unlikely, in
                                                                                case of ingestion of 2-BTP, the
                                                                                person(s) should consult a
                                                                                physician immediately;
                                                                                Manufacturing space
                                                                                should be equipped with
                                                                                specialized engineering controls
                                                                                and well ventilated with a local
                                                                                exhaust system and low-lying
                                                                                source ventilation to effectively
                                                                                mitigate potential occupational
                                                                                exposure; regular testing and
                                                                                monitoring of the workplace
                                                                                atmosphere should be conducted;
                                                                                Employees responsible for
                                                                                chemical processing should wear
                                                                                the appropriate PPE, such as
                                                                                protective gloves, tightly sealed
                                                                                goggles, protective work
                                                                                clothing, and suitable
                                                                                respiratory protection in case of
                                                                                accidental release or
                                                                                insufficient ventilation;
                                                                                All spills should be
                                                                                cleaned up immediately in
                                                                                accordance with good industrial
                                                                                hygiene practices; and
                                                                                Training for safe
                                                                                handling procedures should be
                                                                                provided to all employees that
                                                                                would be likely to handle
                                                                                containers of the agent or
                                                                                extinguishing units filled with
                                                                                the agent.
                                                                                Safety features that are
                                                                                typical of total flooding systems
                                                                                such as predischarge alarms, time
                                                                                delays, and system abort switches
                                                                                should be provided, as directed
                                                                                by applicable OSHA regulations
                                                                                and NFPA standards.\1\ Use of
                                                                                this agent should also conform to
                                                                                relevant OSHA requirements,
                                                                                including 29 CFR 1910.160 and
                                                                                1910.162.
                                                                                See notes 1 through 5 to this
                                                                                table.

2. Streaming.....................  2-BTP.................  Acceptable, Subject   Acceptable only for use in non-      This fire suppressant has a
                                                            to Use Conditions.    residential applications, except     relatively low GWP of 0.23-0.26
                                                                                for commercial home office and       and a short atmospheric lifetime
                                                                                personal watercraft.                 of approximately seven days.
                                                                                This agent is subject to a TSCA
                                                                                section 5(a)(2) SNUR.
                                                                                For establishments manufacturing,
                                                                                installing and maintaining
                                                                                equipment using this agent, EPA
                                                                                recommends the following:
                                                                                This agent should be used
                                                                                in accordance with the safety
                                                                                guidelines in the latest edition
                                                                                of NFPA 10, Standard for Portable
                                                                                Fire Extinguishers; \1\
                                                                                In the case that 2-BTP is
                                                                                inhaled, person(s) should be
                                                                                immediately removed and exposed
                                                                                to fresh air; if breathing is
                                                                                difficult, person(s) should seek
                                                                                medical attention;
                                                                                Eye wash and quick drench
                                                                                facilities should be available.
                                                                                In case of ocular exposure,
                                                                                person(s) should immediately
                                                                                flush the eyes, including under
                                                                                the eyelids, with fresh water and
                                                                                move to a non-contaminated area;
                                                                                Exposed persons should
                                                                                remove all contaminated clothing
                                                                                and footwear to avoid irritation;
                                                                                and medical attention should be
                                                                                sought if irritation develops or
                                                                                persists;
                                                                                Although unlikely, in
                                                                                case of ingestion of 2-BTP, the
                                                                                person(s) should consult a
                                                                                physician immediately;
                                                                                Manufacturing space
                                                                                should be equipped with
                                                                                specialized engineering controls
                                                                                and well ventilated with a local
                                                                                exhaust system and low-lying
                                                                                source ventilation to effectively
                                                                                mitigate potential occupational
                                                                                exposure; regular testing and
                                                                                monitoring of the workplace
                                                                                atmosphere should be conducted;
                                                                                Employees responsible for
                                                                                chemical processing should wear
                                                                                the appropriate PPE, such as
                                                                                protective gloves, tightly sealed
                                                                                goggles, protective work
                                                                                clothing, and suitable
                                                                                respiratory protection in case of
                                                                                accidental release or
                                                                                insufficient ventilation;
                                                                                All spills should be
                                                                                cleaned up immediately in
                                                                                accordance with good industrial
                                                                                hygiene practices; and
                                                                                Training for safe
                                                                                handling procedures should be
                                                                                provided to all employees that
                                                                                would be likely to handle
                                                                                containers of the agent or
                                                                                extinguishing units filled with
                                                                                the agent.
                                                                                See notes 1 through 5 to this
                                                                                table.

3. Total Flooding................  EXXFIRE[supreg].......  Acceptable Subject    Acceptable only for use in normally  Use of this agent should be in
                                                            to Use Conditions.    unoccupied spaces.                   accordance with the safety
                                                                                guidelines in the latest edition
                                                                                of the NFPA 2001, Standard on
                                                                                Clean Agent Fire Extinguishing
                                                                                Systems.\1\
                                                                                For establishments manufacturing,
                                                                                installing and maintaining
                                                                                equipment using this agent, EPA
                                                                                recommends the following:
                                                                                In the case that
                                                                                EXXFIRE[supreg] is inhaled,
                                                                                person(s) should be immediately
                                                                                removed and exposed to fresh air.
                                                                                Eye wash and quick drench
                                                                                facilities should be available.
                                                                                In case of ocular exposure,
                                                                                person(s) should immediately
                                                                                flush the eyes with water for a
                                                                                minimum of 15 minutes.
                                                                                In the case of dermal
                                                                                exposure, the SDS recommends that
                                                                                person(s) should remove large
                                                                                grain particles, rinse with water
                                                                                for a minimum of 15 minutes, and
                                                                                remove all contaminated clothing.
                                                                                Manufacturing space
                                                                                should be equipped with
                                                                                engineering controls,
                                                                                specifically an adequate exhaust
                                                                                ventilation system, to
                                                                                effectively mitigate potential
                                                                                occupational exposure.
                                                                                Employees responsible for
                                                                                chemical processing should wear
                                                                                the appropriate personnel
                                                                                protective equipment (PPE), such
                                                                                as protective gloves, tightly
                                                                                sealed goggles, protective work
                                                                                clothing, and suitable
                                                                                respiratory protection in case of
                                                                                accidental release or
                                                                                insufficient ventilation.
                                                                                All spills should be
                                                                                cleaned up immediately in
                                                                                accordance with good industrial
                                                                                hygiene practices.
                                                                                Training for safe
                                                                                handling procedures should be
                                                                                provided to all employees that
                                                                                would be likely to handle
                                                                                containers of the agent or
                                                                                extinguishing units filled with
                                                                                the agent.
                                                                                Safety features that are
                                                                                typical of total flooding systems
                                                                                such as predischarge alarms, time
                                                                                delays, and system abort switches
                                                                                should be provided, as directed
                                                                                by applicable OSHA regulations
                                                                                and NFPA standards.\1\
                                                                                See notes 1 through 5 to this
                                                                                table.
4. Total Flooding................  Powdered Aerosol H....  Acceptable Subject    Acceptable only for use in normally  Use of this agent should be in
                                                            to Use Conditions.    unoccupied spaces.                   accordance with the safety
                                                                                guidelines in the latest edition
                                                                                of NFPA 2010, Standard for Fixed
                                                                                Aerosol Fire Extinguishing
                                                                                Systems.\1\
                                                                                For establishments manufacturing,
                                                                                installing, and maintaining
                                                                                equipment using this agent, EPA
                                                                                recommends the following:
                                                                                Workers should use
                                                                                appropriate safety and protective
                                                                                equipment (e.g., protective
                                                                                gloves, tightly sealed goggles,
                                                                                protective work clothing, and
                                                                                particulate-removing respirators
                                                                                using NIOSH type N95 or better
                                                                                filters) consistent with OSHA
                                                                                guidelines.
                                                                                A local exhaust system
                                                                                should be installed and operated
                                                                                to provide adequate ventilation
                                                                                to reduce airborne exposure to
                                                                                Powdered Aerosol H constituents.
                                                                                An eye wash fountain and
                                                                                quick drench facility should be
                                                                                close to the production area.
                                                                                Training for safe
                                                                                handling procedures should be
                                                                                provided to all employees that
                                                                                would be likely to handle the
                                                                                containers of the agent or
                                                                                extinguishing units filled with
                                                                                the agent.
                                                                                Workers responsible for
                                                                                cleanup should allow particulates
                                                                                to settle before reentering area
                                                                                and wear appropriate personal
                                                                                protective equipment.
                                                                                All spills should be
                                                                                cleaned up immediately in
                                                                                accordance with good industrial
                                                                                hygiene practices.
                                                                                See notes 1 through 5 to this
                                                                                table.
--------------------------------------------------------------------------------------------------------------------------------------------------------
\1\ National Fire Protection Association (NFPA) standards are available from www.nfpa.org.
Note 1: The EPA recommends that users consult Section VIII of the OSHA Technical Manual for information on selecting the appropriate types of personal
  protective equipment for all listed fire suppression agents. The EPA has no intention of duplicating or displacing OSHA coverage related to the use of
  personal protective equipment (e.g., respiratory protection), fire protection, hazard communication, worker training or any other occupational safety
  and health standard with respect to halon substitutes).
Note 2: Use of all listed fire suppression agents should conform to relevant OSHA requirements, including 29 CFR 1910.160 and 1910.162.
Note 3: Per OSHA requirements, protective gear (SCBA) should be available in the event personnel should reenter the area.
Note 4: Discharge testing should be strictly limited to that which is essential to meet safety or performance requirements.
Note 5: The agent should be recovered from the fire protection system in conjunction with testing or servicing and recycled for later use or destroyed.

[FR Doc. 2022-14665 Filed 7-27-22; 8:45 am]
BILLING CODE 6560-50-P


Site Visit

Gage Products and Ford Motor Company

May 15, 2006

On May 15, 2006, representatives of EPA’s Hazardous Waste
Identification Division visited the facilities of Gage Products and Ford
in Detroit, MI, to tour their facilities and discuss their solvent
recycling processes. In attendance:

Charlotte Mooney	EPA OSW

Amy Lile		EPA OSW

Kathy Blanton		EPA OSW

Donald Dixon		Gage

Sharon Stahl		Gage

Julie Mileskiy		Gage, Environmental Engineer

Mark Weisman	Gage, Chemical Engineer

Jim Walker		Ford, Environmental Supervisor

Dave Drinan		Ford, Environmental Compliance Engineer

Representatives of EPA, Gage, and Ford discussed the operations at the
Gage solvent recycling facility, the benefits they see for recycling of
doing it at an off-site facility, and Gage’s relationship with their
customers. EPA participated in a tour of Gage’s storage areas,
laboratories, and recycling facility as well as a tour of a Ford plant
that uses Gage’s solvent service to see the solvents in use.


[Federal Register Volume 79, Number 62 (Tuesday, April 1, 2014)]
[Notices]
[Pages 18388-18389]
[FR Doc No: 2014-07209]

-----------------------------------------------------------------------

DEPARTMENT OF TRANSPORTATION

Federal Motor Carrier Safety Administration

[FMCSA Docket No. FMCSA-2013-0194]

Qualification of Drivers; Exemption Applications; Diabetes
Mellitus

AGENCY: Federal Motor Carrier Safety Administration (FMCSA), DOT.

ACTION: Notice of final disposition.

-----------------------------------------------------------------------

SUMMARY: FMCSA announces its decision to exempt 40 individuals from its
rule prohibiting persons with insulin-treated diabetes mellitus (ITDM)
from operating commercial motor vehicles (CMVs) in interstate commerce.
The exemptions will enable these individuals to operate CMVs in
interstate commerce.

DATES: The exemptions are effective April 1, 2014. The exemptions
expire on March 31, 2016.

FOR FURTHER INFORMATION CONTACT: Elaine M. Papp, Chief, Medical
Programs Division,<PHONE_NUMBER><EMAIL_ADDRESS>FMCSA, Room
W64-224, Department of Transportation, 1200 New Jersey Avenue SE.,
Washington, DC 20590-0001. Office hours are from 8:30 a.m. to 5 p.m.,
Monday through Friday, except Federal holidays.

SUPPLEMENTARY INFORMATION:

Electronic Access

    You may see all the comments online through the Federal Document
Management System (FDMS) at: http://www.regulations.gov.
    Docket: For access to the docket to read background documents or
comments, go to http://www.regulations.gov and/or Room W12-140 on the
ground level of the West Building, 1200 New Jersey Avenue SE.,
Washington, DC, between 9 a.m. and 5 p.m., Monday through Friday,
except Federal holidays.
    Privacy Act: Anyone may search the electronic form of all comments
received into any of DOT's dockets by the name of the individual
submitting the comment (or of the person signing the comment, if
submitted on behalf of an association, business, labor union, or other
entity). You may review DOT's Privacy Act Statement for the Federal
Docket Management System (FDMS) published in the Federal Register on
January 17, 2008 (73 FR 3316).

Background

    On February 5, 2013, FMCSA published a notice of receipt of Federal
diabetes exemption applications from 40 individuals and requested
comments from the public (79 FR 6987). The public comment period closed
on March 7, 2014 and no comments were received.
    FMCSA has evaluated the eligibility of the 40 applicants and
determined that granting the exemptions to these individuals would
achieve a level of safety equivalent to or greater than the level that
would be achieved by complying with the current regulation 49 CFR
391.41(b)(3).

Diabetes Mellitus and Driving Experience of the Applicants

    The Agency established the current requirement for diabetes in 1970
because several risk studies indicated that drivers with diabetes had a
higher rate of crash involvement than the general population. The
diabetes rule provides that ``A person is physically qualified to drive
a commercial motor vehicle if that person has no established medical
history or clinical diagnosis of diabetes mellitus currently requiring
insulin for control'' (49 CFR 391.41(b)(3)).
    FMCSA established its diabetes exemption program, based on the
Agency's July 2000 study entitled ``A Report to Congress on the
Feasibility of a Program to Qualify Individuals with Insulin-Treated
Diabetes Mellitus to Operate in Interstate Commerce as Directed by the
Transportation Act for the 21st Century.'' The report concluded that a
safe and practicable protocol to allow some drivers with ITDM to
operate CMVs is feasible. The September 3, 2003 (68 FR 52441), Federal
Register notice in conjunction with the November 8, 2005 (70 FR 67777),
Federal Register notice provides the current protocol for allowing such
drivers to operate CMVs in interstate commerce.
    These 40 applicants have had ITDM over a range of 1 to 41 years.
These applicants report no severe hypoglycemic reactions resulting in
loss of consciousness or seizure, requiring the assistance of another
person, or resulting in impaired cognitive function that occurred
without warning symptoms, in the past 12 months and no recurrent (2 or
more) severe hypoglycemic episodes in the past 5 years. In each case,
an endocrinologist verified that the driver has demonstrated a
willingness to properly monitor and manage his/her diabetes mellitus,
received education related to diabetes management, and is on a stable
insulin regimen. These drivers report no other disqualifying
conditions, including diabetes-related complications. Each meets the
vision requirement at 49 CFR 391.41(b)(10).
    The qualifications and medical condition of each applicant were
stated and discussed in detail in the February 5, 2014, Federal
Register notice and they will not be repeated in this notice.

Discussion of Comments

    FMCSA received no comments in this proceeding.

Basis for Exemption Determination

    Under 49 U.S.C. 31136(e) and 31315, FMCSA may grant an exemption
from the diabetes requirement in 49 CFR 391.41(b)(3) if the exemption
is likely to achieve an equivalent or greater level of safety than
would be achieved without the exemption. The exemption allows the
applicants to operate CMVs in interstate commerce.
    To evaluate the effect of these exemptions on safety, FMCSA

considered medical reports about the applicants' ITDM and vision, and
reviewed the treating endocrinologists' medical opinion related to the
ability of the driver to safely operate a CMV while using insulin.
    Consequently, FMCSA finds that in each case exempting these
applicants from the diabetes requirement in 49 CFR 391.41(b)(3) is
likely to achieve a level of safety equal to that existing without the
exemption.

Conditions and Requirements

    The terms and conditions of the exemption will be provided to the
applicants in the exemption document and they include the following:
(1) That each individual submit a quarterly monitoring checklist
completed by the treating endocrinologist as well as an annual
checklist with a comprehensive medical evaluation; (2) that each
individual reports within 2 business days of occurrence, all episodes
of severe hypoglycemia, significant complications, or inability to
manage diabetes; also, any involvement in an accident or any other
adverse event in a CMV or personal vehicle, whether or not it is
related to an episode of hypoglycemia; (3) that each individual provide
a copy of the ophthalmologist's or optometrist's report to the medical
examiner at the time of the annual medical examination; and (4) that
each individual provide a copy of the annual medical certification to
the employer for retention in the driver's qualification file, or keep
a copy in his/her driver's qualification file if he/she is self-
employed. The driver must also have a copy of the certification when
driving, for presentation to a duly authorized Federal, State, or local
enforcement official.

Conclusion

    Based upon its evaluation of the 40 exemption applications, FMCSA
exempts Dana A. Albert (NY), John R. Benshoff (OH), Douglas R. Black,
Sr. (OH), Kenneth Bland (NY), George A. Blanda (NY), Terrence K. Cannon
(IL), Trisha J. Davis (ME), Brian J. Decker (IA), Joshua A. Enis (MS),
Richard R. Epstein (WI), Paul D. Ferris (NY), Tyrone E. Fisher (NJ),
Larry Gaskill (RI), Thomas H. Gaskins (NC), Gary A. Grant (WA), Brian
C. Halcomb (IL), David H. Hodges (AR), Gerald Lee (CA), Timothy R.
Lewis (OR), Gregory J. Littlefield (MN), Marvin E. Marry (KY), Glen H.
Miller (MI), Ryan M. Ottis (ND), Steven M. Parsons (WV), Fortino Perry
(AL), William L. Reece (ND), Jesus M. Rosario (MA), Jay R. Rude (AZ),
Denise D. Ruffin (MS), Richard R. Sterling (WI), Ryan E. Stretch (MO),
William F. Sullivan, IV (NY), Paul D. Summerford (MS), John R. Thompson
(WI), Everette L. Twyman (MO), Kim L. Watson (MD), Brian D. Weeks (WI),
Ammon R. West (ID), Michael A. White (MD), and John F. Whitesides (NC)
from the ITDM requirement in 49 CFR 391.41(b)(3), subject to the
conditions listed under ``Conditions and Requirements'' above.
    In accordance with 49 U.S.C. 31136(e) and 31315 each exemption will
be valid for two years unless revoked earlier by FMCSA. The exemption
will be revoked if the following occurs: (1) The person fails to comply
with the terms and conditions of the exemption; (2) the exemption has
resulted in a lower level of safety than was maintained before it was
granted; or (3) continuation of the exemption would not be consistent
with the goals and objectives of 49 U.S.C. 31136(e) and 31315. If the
exemption is still effective at the end of the 2-year period, the
person may apply to FMCSA for a renewal under procedures in effect at
that time.

    Issued on: March 18, 2014.
Larry W. Minor,
Associate Administrator for Policy.
[FR Doc. 2014-07209 Filed 3-31-14; 8:45 am]
BILLING CODE 4910-EX-P