measured during
                                                                                the most recent
                                                                                HCl performance
                                                                                tests.
3. Mercury......................  a. Activated        i. Establish a      (1) Data from the   (a) You must
                                   carbon injection.   site-specific       activated carbon    collect activated
                                                       minimum activated   rate monitors and   carbon injection
                                                       carbon injection    mercury             rate data every
                                                       rate operating      performance test.   15 minutes during
                                                       limit according                         the entire period
                                                       to Sec.                                 of the
                                                       63.7530(b).                             performance
                                                                                tests.
                                                                                (b) Determine the
                                                                                hourly average
                                                                                activated carbon
                                                                                injection rate by
                                                                                computing the
                                                                                hourly averages
                                                                                using all of the
                                                                                15-minute
                                                                                readings taken
                                                                                during each
                                                                                performance test.
                                                                                (c) Determine the
                                                                                lowest hourly
                                                                                average
                                                                                established
                                                                                during the
                                                                                performance test
                                                                                as your operating
                                                                                limit. When your
                                                                                unit operates at
                                                                                lower loads,
                                                                                multiply your
                                                                                activated carbon
                                                                                injection rate by
                                                                                the load fraction
                                                                                (e.g., actual
                                                                                heat input
                                                                                divided by heat
                                                                                input during
                                                                                performance test,
                                                                                for 50 percent
                                                                                load, multiply
                                                                                the injection
                                                                                rate operating
                                                                                limit by 0.5) to
                                                                                determine the
                                                                                required
                                                                                injection rate.
4. Carbon monoxide..............  a. Oxygen.........  i. Establish a      (1) Data from the   (a) You must
                                                       unit-specific       oxygen analyzer     collect oxygen
                                                       limit for minimum   system specified    data every 15
                                                       oxygen level        in Sec.             minutes during
                                                       according to Sec.   63.7525(a).         the entire period
                                                         63.7520.                              of the
                                                                                performance
                                                                                tests.
                                                                                (b) Determine the
                                                                                hourly average
                                                                                oxygen
                                                                                concentration by
                                                                                computing the
                                                                                hourly averages
                                                                                using all of the
                                                                                15-minute
                                                                                readings taken
                                                                                during each
                                                                                performance test.
                                                                                (c) Determine the
                                                                                lowest hourly
                                                                                average
                                                                                established
                                                                                during the
                                                                                performance test
                                                                                as your minimum
                                                                                operating limit.

                                                  * * * * * * *
----------------------------------------------------------------------------------------------------------------

0
35. Table 8 to subpart DDDDD of part 63 is revised to read as follows:
    As stated in Sec.  63.7540, you must show continuous compliance
with the emission limitations for each boiler or process heater
according to the following:

Table 8 to Subpart DDDDD of Part 63--Demonstrating Continuous Compliance
------------------------------------------------------------------------
     If you must meet the
following operating limits or       You must demonstrate continuous
work practice standards . . .             compliance by . . .
------------------------------------------------------------------------
1. Opacity...................  a. Collecting the opacity monitoring
                                system data according to Sec.
                                63.7525(c) and Sec.   63.7535; and
                               b. Reducing the opacity monitoring data
                                to 6-minute averages; and
                               c. Maintaining opacity to less than or
                                equal to 10 percent (daily block
                                average).
2. PM CPMS...................  a. Collecting the PM CPMS output data
                                according to Sec.   63.7525;
                               b. Reducing the data to 30-day rolling
                                averages; and
                               c. Maintaining the 30-day rolling average
                                PM CPMS output data to less than the
                                operating limit established during the
                                performance test according to Sec.
                                63.7530(b)(4).
3. Fabric Filter Bag Leak      Installing and operating a bag leak
 Detection Operation.           detection system according to Sec.
                                63.7525 and operating the fabric filter
                                such that the requirements in Sec.
                                63.7540(a)(9) are met.
4. Wet Scrubber Pressure Drop  a. Collecting the pressure drop and
 and Liquid Flow-rate.          liquid flow rate monitoring system data
                                according to Sec.  Sec.   63.7525 and
                                63.7535; and
                               b. Reducing the data to 30-day rolling
                                averages; and
                               c. Maintaining the 30-day rolling average
                                pressure drop and liquid flow-rate at or
                                above the operating limits established
                                during the performance test according to
                                Sec.   63.7530(b).
5. Wet Scrubber pH...........  a. Collecting the pH monitoring system
                                data according to Sec.  Sec.   63.7525
                                and 63.7535; and

                               b. Reducing the data to 30-day rolling
                                averages; and
                               c. Maintaining the 30-day rolling average
                                pH at or above the operating limit
                                established during the performance test
                                according to Sec.   63.7530(b).
6. Dry Scrubber Sorbent or     a. Collecting the sorbent or carbon
 Carbon Injection Rate.         injection rate monitoring system data
                                for the dry scrubber according to Sec.
                                Sec.   63.7525 and 63.7535; and
                               b. Reducing the data to 30-day rolling
                                averages; and
                               c. Maintaining the 30-day rolling average
                                sorbent or carbon injection rate at or
                                above the minimum sorbent or carbon
                                injection rate as defined in Sec.
                                63.7575.
7. Electrostatic Precipitator  a. Collecting the total secondary
 Total Secondary Electric       electric power input monitoring system
 Power Input.                   data for the electrostatic precipitator
                                according to Sec.  Sec.   63.7525 and
                                63.7535; and
                               b. Reducing the data to 30-day rolling
                                averages; and
                               c. Maintaining the 30-day rolling average
                                total secondary electric power input at
                                or above the operating limits
                                established during the performance test
                                according to Sec.   63.7530(b).
8. Emission limits using fuel  a. Conduct monthly fuel analysis for HCl
 analysis.                      or mercury or TSM according to Table 6
                                to this subpart; and
                               b. Reduce the data to 12-month rolling
                                averages; and
                               c. Maintain the 12-month rolling average
                                at or below the applicable emission
                                limit for HCl or mercury or TSM in
                                Tables 1 and 2 or 11 through 13 to this
                                subpart.
9. Oxygen content............  a. Continuously monitor the oxygen
                                content using an oxygen analyzer system
                                according to Sec.   63.7525(a). This
                                requirement does not apply to units that
                                install an oxygen trim system since
                                these units will set the trim system to
                                the level specified in Sec.
                                63.7525(a)(2).
                               b. Reducing the data to 30-day rolling
                                averages; and
                               c. Maintain the 30-day rolling average
                                oxygen content at or above the lowest
                                hourly average oxygen level measured
                                during the most recent CO performance
                                test.
10. Boiler or process heater   a. Collecting operating load data or
 operating load.                steam generation data every 15 minutes.
                               b. Maintaining the operating load such
                                that it does not exceed 110 percent of
                                the highest hourly average operating
                                load recorded during the most recent
                                performance test according to Sec.
                                63.7520(c).
11. SO2 emissions using SO2    a. Collecting the SO2 CEMS output data
 CEMS.                          according to Sec.   63.7525;
                               b. Reducing the data to 30-day rolling
                                averages; and
                               c. Maintaining the 30-day rolling average
                                SO2 CEMS emission rate to a level at or
                                below the minimum hourly SO2 rate
                                measured during the most recent HCl
                                performance test according to Sec.
                                63.7530.
------------------------------------------------------------------------

0
36. Table 9 to subpart DDDDD of part 63 is amended by revising the
entry for ``1. Compliance report'' to read as follows:
    As stated in Sec.  63.7550, you must comply with the following
requirements for reports:

       Table 9 to Subpart DDDDD of Part 63--Reporting Requirements
------------------------------------------------------------------------
                                    The report must     You must submit
      You must submit a(n)           contain . . .     the report . . .
------------------------------------------------------------------------
1. Compliance report............  a. Information      Semiannually,
                                   required in Sec.    annually,
                                    63.7550(c)(1)      biennially, or
                                   through (5); and    every 5 years
                                                       according to the
                                                       requirements in
                                                       Sec.
                                                       63.7550(b).

                              * * * * * * *
------------------------------------------------------------------------

0
37. Table 10 to subpart DDDDD of part 63 is amended by:
0
a. Revising the entry for ``Sec.  63.6(i)''.
0
b. Revising the entry for ``Sec.  63.7(e)(1)''.
0
c. Revising the entry for ``63.8(g)''.
0
d. Revising the entry for ``Sec.  63.10(e) and (f)''.
0
e. Adding an entry for ``Sec.  63.10(e)''.
    The revisions and addition read as follows.
    As stated in Sec.  63.7565, you must comply with the applicable
General Provisions according to the following:

     Table 10 to Subpart DDDDD of Part 63--Applicability of General
                       Provisions to Subpart DDDDD
------------------------------------------------------------------------
                                                      Applies to subpart
           Citation                   Subject               DDDDD
------------------------------------------------------------------------

                              * * * * * * *
Sec.   63.6(i)................  Extension of         Yes. Note:
                                 compliance.          Facilities may
                                                      also request
                                                      extensions of
                                                      compliance for the
                                                      installation of
                                                      combined heat and
                                                      power, waste heat
                                                      recovery, or gas
                                                      pipeline or fuel
                                                      feeding
                                                      infrastructure as
                                                      a means of
                                                      complying with
                                                      this subpart.

                              * * * * * * *
Sec.   63.7(e)(1).............  Conditions for       No. Subpart DDDDD
                                 conducting           specifies
                                 performance tests.   conditions for
                                                      conducting
                                                      performance tests
                                                      at Sec.
                                                      63.7520(a) to (c).

                              * * * * * * *
Sec.   63.8(g)................  Reduction of         Yes.
                                 monitoring data.

                              * * * * * * *
Sec.   63.10(e)...............  Additional           Yes.
                                 reporting
                                 requirements for
                                 sources with CMS.
Sec.   63.10(f)...............  Waiver of            Yes.
                                 recordkeeping or
                                 reporting
                                 requirements.

                              * * * * * * *
------------------------------------------------------------------------

0
38. Add Table 11 to subpart DDDDD of part 63 to read as follows:

 Table 11 to Subpart DDDDD of Part 63--Alternative Emission Limits for New or Reconstructed Boilers and Process
        Heaters That Commenced Construction or Reconstruction After June 4, 2010, and Before May 20, 2011
----------------------------------------------------------------------------------------------------------------
                                                                       The emissions must
                                                                         not exceed the
                                                                       following emission   Using this specified
 If your boiler or process heater   For the following pollutants . .     limits, except      sampling volume or
   is in this subcategory . . .                     .                   during periods of    test run duration .
                                                                      startup and shutdown           . .
                                                                              . . .
----------------------------------------------------------------------------------------------------------------
1. Units in all subcategories       a. HCl..........................  0.022 lb per MMBtu    For M26A, collect a
 designed to burn solid fuel.                                          of heat input.        minimum of 1 dscm
                                                                                per run; for M26
                                                                                collect a minimum
                                                                                of 120 liters per
                                                                                run.
2. Units in all subcategories       a. Mercury......................  8.0E-07 \a\ lb per    For M29, collect a
 designed to burn solid fuel that                                      MMBtu of heat input.  minimum of 4 dscm
 combust at least 10 percent                                                                 per run; for M30A
 biomass/bio-based solids on an                                                              or M30B, collect a
 annual heat input basis and less                                                            minimum sample as
 than 10 percent coal/solid fossil                                                           specified in the
 fuels on an annual heat input                                                               method; for ASTM
 basis.                                                                                D6784 \b\ collect a
                                                                                minimum of 4 dscm.
3. Units in all subcategories       a. Mercury......................  2.0E-06 lb per MMBtu  For M29, collect a
 designed to burn solid fuel that                                      of heat input.        minimum of 4 dscm
 combust at least 10 percent coal/                                                           per run; for M30A
 solid fossil fuels on an annual                                                             or M30B, collect a
 heat input basis and less than 10                                                           minimum sample as
 percent biomass/bio-based solids                                                            specified in the
 on an annual heat input basis.                                                              method; for ASTM
                                                                                D6784 \b\ collect a
                                                                                minimum of 4 dscm.
4. Units designed to burn coal/     a. Filterable PM (or TSM).......  1.1E-03 lb per MMBtu  Collect a minimum of
 solid fossil fuel.                                                    of heat input; or     3 dscm per run.
                                                                       (2.3E-05 lb per
                                                                       MMBtu of heat
                                                                       input).
5. Pulverized coal boilers          a. Carbon monoxide (CO) (or       130 ppm by volume on  1 hr minimum
 designed to burn coal/solid         CEMS).                            a dry basis           sampling time.
 fossil fuel.                                                          corrected to 3
                                                                       percent oxygen, 3-
                                                                       run average; or
                                                                       (320 ppm by volume
                                                                       on a dry basis
                                                                       corrected to 3
                                                                       percent oxygen, 30-
                                                                       day rolling
                                                                       average).
6. Stokers designed to burn coal/   a. CO (or CEMS).................  130 ppm by volume on  1 hr minimum
 solid fossil fuel.                                                    a dry basis           sampling time.
                                                                       corrected to 3
                                                                       percent oxygen, 3-
                                                                       run average; or
                                                                       (340 ppm by volume
                                                                       on a dry basis
                                                                       corrected to 3
                                                                       percent oxygen, 10-
                                                                       day rolling
                                                                       average).
7. Fluidized bed units designed to  a. CO (or CEMS).................  130 ppm by volume on  1 hr minimum
 burn coal/solid fossil fuel.                                          a dry basis           sampling time.
                                                                       corrected to 3
                                                                       percent oxygen, 3-
                                                                       run average; or
                                                                       (230 ppm by volume
                                                                       on a dry basis
                                                                       corrected to 3
                                                                       percent oxygen, 30-
                                                                       day rolling
                                                                       average).

8. Fluidized bed units with an      a. CO (or CEMS).................  140 ppm by volume on  1 hr minimum
 integrated heat exchanger                                             a dry basis           sampling time.
 designed to burn coal/solid                                           corrected to 3
 fossil fuel.                                                          percent oxygen, 3-
                                                                       run average; or
                                                                       (150 ppm by volume
                                                                       on a dry basis
                                                                       corrected to 3
                                                                       percent oxygen, 30-
                                                                       day rolling
                                                                       average).
9. Stokers/sloped grate/others      a. CO (or CEMS).................  620 ppm by volume on  1 hr minimum
 designed to burn wet biomass fuel.                                    a dry basis           sampling time.
                                                                       corrected to 3
                                                                       percent oxygen, 3-
                                                                       run average; or
                                                                       (390 ppm by volume
                                                                       on a dry basis
                                                                       corrected to 3
                                                                       percent oxygen, 30-
                                                                       day rolling
                                                                       average).
                                    b. Filterable PM (or TSM).......  3.0E-02 lb per MMBtu  Collect a minimum of
                                                                       of heat input; or     2 dscm per run.
                                                                       (2.6E-05 lb per
                                                                       MMBtu of heat
                                                                       input).
10. Stokers/sloped grate/others     a. CO...........................  560 ppm by volume on  1 hr minimum
 designed to burn kiln-dried                                           a dry basis           sampling time.
 biomass fuel.                                                         corrected to 3
                                                                       percent oxygen.
                                    b. Filterable PM (or TSM).......  3.0E-02 lb per MMBtu  Collect a minimum of
                                                                       of heat input; or     2 dscm per run.
                                                                       (4.0E-03 lb per
                                                                       MMBtu of heat
                                                                       input).
11. Fluidized bed units designed    a. CO (or CEMS).................  230 ppm by volume on  1 hr minimum
 to burn biomass/bio-based solids.                                     a dry basis           sampling time.
                                                                       corrected to 3
                                                                       percent oxygen, 3-
                                                                       run average; or
                                                                       (310 ppm by volume
                                                                       on a dry basis
                                                                       corrected to 3
                                                                       percent oxygen, 30-
                                                                       day rolling
                                                                       average).
                                    b. Filterable PM (or TSM).......  9.8E-03 lb per MMBtu  Collect a minimum of
                                                                       of heat input; or     3 dscm per run
                                                                       (8.3E-05 \a\ lb per
                                                                       MMBtu of heat
                                                                       input).
12. Suspension burners designed to  a. CO (or CEMS).................  2,400 ppm by volume   1 hr minimum
 burn biomass/bio-based solids.                                        on a dry basis        sampling time.
                                                                       corrected to 3
                                                                       percent oxygen, 3-
                                                                       run average; or
                                                                       (2,000 ppm by
                                                                       volume on a dry
                                                                       basis corrected to
                                                                       3 percent oxygen,
                                                                       10-day rolling
                                                                       average).
                                    b. Filterable PM (or TSM).......  3.0E-02 lb per MMBtu  Collect a minimum of
                                                                       of heat input; or     2 dscm per run.
                                                                       (6.5E-03 lb per
                                                                       MMBtu of heat
                                                                       input).
13. Dutch Ovens/Pile burners        a. CO (or CEMS).................  1,010 ppm by volume   1 hr minimum
 designed to burn biomass/bio-                                         on a dry basis        sampling time.
 based solids.                                                         corrected to 3
                                                                       percent oxygen, 3-
                                                                       run average; or
                                                                       (520 ppm by volume
                                                                       on a dry basis
                                                                       corrected to 3
                                                                       percent oxygen, 10-
                                                                       day rolling
                                                                       average).
                                    b. Filterable PM (or TSM).......  8.0E-03 lb per MMBtu  Collect a minimum of
                                                                       of heat input; or     3 dscm per run.
                                                                       (3.9E-05 lb per
                                                                       MMBtu of heat
                                                                       input).
14. Fuel cell units designed to     a. CO...........................  910 ppm by volume on  1 hr minimum
 burn biomass/bio-based solids.                                        a dry basis           sampling time.
                                                                       corrected to 3
                                                                       percent oxygen.
                                    b. Filterable PM (or TSM).......  2.0E-02 lb per MMBtu  Collect a minimum of
                                                                       of heat input; or     2 dscm per run.
                                                                       (2.9E-05 lb per
                                                                       MMBtu of heat
                                                                       input).
15. Hybrid suspension grate boiler  a. CO (or CEMS).................  1,100 ppm by volume   1 hr minimum
 designed to burn biomass/bio-                                         on a dry basis        sampling time.
 based solids.                                                         corrected to 3
                                                                       percent oxygen, 3-
                                                                       run average; or
                                                                       (900 ppm by volume
                                                                       on a dry basis
                                                                       corrected to 3
                                                                       percent oxygen, 30-
                                                                       day rolling
                                                                       average).
                                    b. Filterable PM (or TSM).......  2.6E-02 lb per MMBtu  Collect a minimum of
                                                                       of heat input; or     3 dscm per run.
                                                                       (4.4E-04 lb per
                                                                       MMBtu of heat
                                                                       input).
16. Units designed to burn liquid   a. HCl..........................  4.4E-04 lb per MMBtu  For M26A: Collect a
 fuel.                                                                 of heat input.        minimum of 2 dscm
                                                                                per run; for M26,
                                                                                collect a minimum
                                                                                of 240 liters per
                                                                                run.

                                    b. Mercury......................  4.8E-07 \a\ lb per    For M29, collect a
                                                                       MMBtu of heat input.  minimum of 4 dscm
                                                                                per run; for M30A
                                                                                or M30B, collect a
                                                                                minimum sample as
                                                                                specified in the
                                                                                method; for ASTM
                                                                                D6784 \b\ collect a
                                                                                minimum of 4 dscm.
17. Units designed to burn heavy    a. CO...........................  130 ppm by volume on  1 hr minimum
 liquid fuel.                                                          a dry basis           sampling time.
                                                                       corrected to 3
                                                                       percent oxygen, 3-
                                                                       run average.
                                    b. Filterable PM (or TSM).......  1.3E-02 lb per MMBtu  Collect a minimum of
                                                                       of heat input; or     3 dscm per run.
                                                                       (7.5E-05 lb per
                                                                       MMBtu of heat
                                                                       input).
18. Units designed to burn light    a. CO...........................  130 ppm by volume on  1 hr minimum
 liquid fuel.                                                          a dry basis           sampling time.
                                                                       corrected to 3
                                                                       percent oxygen.
                                    b. Filterable PM (or TSM).......  2.0E-03 \a\ lb per    Collect a minimum of
                                                                       MMBtu of heat         3 dscm per run
                                                                       input; or (2.9E-05
                                                                       lb per MMBtu of
                                                                       heat input).
19. Units designed to burn liquid   a. CO...........................  130 ppm by volume on  1 hr minimum
 fuel that are non-continental                                         a dry basis           sampling time.
 units.                                                                corrected to 3
                                                                       percent oxygen, 3-
                                                                       run average based
                                                                       on stack test.
                                    b. Filterable PM (or TSM).......  2.3E-02 lb per MMBtu  Collect a minimum of
                                                                       of heat input; or     4 dscm per run
                                                                       (8.6E-04 lb per
                                                                       MMBtu of heat
                                                                       input).
20. Units designed to burn gas 2    a. CO...........................  130 ppm by volume on  1 hr minimum
 (other) gases.                                                        a dry basis           sampling time.
                                                                       corrected to 3
                                                                       percent oxygen.
                                    b. HCl..........................  1.7E-03 lb per MMBtu  For M26A, collect a
                                                                       of heat input.        minimum of 2 dscm
                                                                                per run; for M26,
                                                                                collect a minimum
                                                                                of 240 liters per
                                                                                run.
                                    c. Mercury......................  7.9E-06 lb per MMBtu  For M29, collect a
                                                                       of heat input.        minimum of 3 dscm
                                                                                per run; for M30A
                                                                                or M30B, collect a
                                                                                minimum sample as
                                                                                specified in the
                                                                                method; for ASTM
                                                                                D6784 \b\ collect a
                                                                                minimum of 3 dscm.
                                    d. Filterable PM (or TSM).......  6.7E-03 lb per MMBtu  Collect a minimum of
                                                                       of heat input; or     3 dscm per run
                                                                       (2.1E-04 lb per
                                                                       MMBtu of heat
                                                                       input).
----------------------------------------------------------------------------------------------------------------
\a\ If you are conducting stack tests to demonstrate compliance and your performance tests for this pollutant
  for at least 2 consecutive years show that your emissions are at or below this limit, you can skip testing
  according to Sec.   63.7515 if all of the other provisions of Sec.   63.7515 are met. For all other pollutants
  that do not contain a footnote ``a'', your performance tests for this pollutant for at least 2 consecutive
  years must show that your emissions are at or below 75 percent of this limit in order to qualify for skip
  testing.
\b\ Incorporated by reference, see Sec.   63.14.

0
39. Add Table 12 to subpart DDDDD of part 63 to read as follows:

 Table 12 to Subpart DDDDD of Part 63--Alternative Emission Limits for New or Reconstructed Boilers and Process
     Heaters that Commenced Construction or Reconstruction after May 20, 2011, and Before December 23, 2011
----------------------------------------------------------------------------------------------------------------
                                                                       The emissions must
                                                                         not exceed the
                                                                       following emission   Using this specified
 If your boiler or process heater   For the following pollutants . .     limits, except      sampling volume or
   is in this subcategory . . .                     .                   during periods of    test run duration .
                                                                      startup and shutdown           . .
                                                                              . . .
----------------------------------------------------------------------------------------------------------------
1. Units in all subcategories       a. HCl..........................  0.022 lb per MMBtu    For M26A, collect a
 designed to burn solid fuel.                                          of heat input.        minimum of 1 dscm
                                                                                per run; for M26
                                                                                collect a minimum
                                                                                of 120 liters per
                                                                                run.
                                    b. Mercury......................  3.5E-06 \a\ lb per    For M29, collect a
                                                                       MMBtu of heat input.  minimum of 3 dscm
                                                                                per run; for M30A
                                                                                or M30B, collect a
                                                                                minimum sample as
                                                                                specified in the
                                                                                method; for ASTM
                                                                                D6784 \b\ collect a
                                                                                minimum of 3 dscm.
2. Units design to burn coal/solid  a. Filterable PM (or TSM).......  1.1E-03 lb per MMBtu  Collect a minimum of
 fossil fuel.                                                          of heat input; or     3 dscm per run.
                                                                       (2.3E-05 lb per
                                                                       MMBtu of heat
                                                                       input).

3. Pulverized coal boilers          a. Carbon monoxide (CO) (or       130 ppm by volume on  1 hr minimum
 designed to burn coal/solid         CEMS).                            a dry basis           sampling time.
 fossil fuel.                                                          corrected to 3
                                                                       percent oxygen, 3-
                                                                       run average; or
                                                                       (320 ppm by volume
                                                                       on a dry basis
                                                                       corrected to 3
                                                                       percent oxygen, 30-
                                                                       day rolling
                                                                       average).
4. Stokers designed to burn coal/   a. CO (or CEMS).................  130 ppm by volume on  1 hr minimum
 solid fossil fuel.                                                    a dry basis           sampling time.
                                                                       corrected to 3
                                                                       percent oxygen, 3-
                                                                       run average; or
                                                                       (340 ppm by volume
                                                                       on a dry basis
                                                                       corrected to 3
                                                                       percent oxygen, 10-
                                                                       day rolling
                                                                       average).
5. Fluidized bed units designed to  a. CO (or CEMS).................  130 ppm by volume on  1 hr minimum
 burn coal/solid fossil fuel.                                          a dry basis           sampling time.
                                                                       corrected to 3
                                                                       percent oxygen, 3-
                                                                       run average; or
                                                                       (230 ppm by volume
                                                                       on a dry basis
                                                                       corrected to 3
                                                                       percent oxygen, 30-
                                                                       day rolling
                                                                       average).
6. Fluidized bed units with an      a. CO (or CEMS).................  140 ppm by volume on  1 hr minimum
 integrated heat exchanger                                             a dry basis           sampling time.
 designed to burn coal/solid                                           corrected to 3
 fossil fuel.                                                          percent oxygen, 3-
                                                                       run average; or
                                                                       (150 ppm by volume
                                                                       on a dry basis
                                                                       corrected to 3
                                                                       percent oxygen, 30-
                                                                       day rolling
                                                                       average).
7. Stokers/sloped grate/others      a. CO (or CEMS).................  620 ppm by volume on  1 hr minimum
 designed to burn wet biomass fuel.                                    a dry basis           sampling time.
                                                                       corrected to 3
                                                                       percent oxygen, 3-
                                                                       run average; or
                                                                       (390 ppm by volume
                                                                       on a dry basis
                                                                       corrected to 3
                                                                       percent oxygen, 30-
                                                                       day rolling
                                                                       average).
                                    b. Filterable PM (or TSM).......  3.0E-02 lb per MMBtu  Collect a minimum of
                                                                       of heat input; or     2 dscm per run.
                                                                       (2.6E-05 lb per
                                                                       MMBtu of heat
                                                                       input).
8. Stokers/sloped grate/others      a. CO...........................  460 ppm by volume on  1 hr minimum
 designed to burn kiln-dried                                           a dry basis           sampling time.
 biomass fuel.                                                         corrected to 3
                                                                       percent oxygen.
                                    b. Filterable PM (or TSM).......  3.0E-02 lb per MMBtu  Collect a minimum of
                                                                       of heat input; or     2 dscm per run.
                                                                       (4.0E-03 lb per
                                                                       MMBtu of heat
                                                                       input).
9. Fluidized bed units designed to  a. CO (or CEMS).................  260 ppm by volume on  1 hr minimum
 burn biomass/bio-based solids.                                        a dry basis           sampling time.
                                                                       corrected to 3
                                                                       percent oxygen, 3-
                                                                       run average; or
                                                                       (310 ppm by volume
                                                                       on a dry basis
                                                                       corrected to 3
                                                                       percent oxygen, 30-
                                                                       day rolling
                                                                       average).
                                    b. Filterable PM (or TSM).......  9.8E-03 lb per MMBtu  Collect a minimum of
                                                                       of heat input; or     3 dscm per run.
                                                                       (8.3E-05 \a\ lb per
                                                                       MMBtu of heat
                                                                       input).
10. Suspension burners designed to  a. CO (or CEMS).................  2,400 ppm by volume   1 hr minimum
 burn biomass/bio-based solids.                                        on a dry basis        sampling time.
                                                                       corrected to 3
                                                                       percent oxygen, 3-
                                                                       run average; or
                                                                       (2,000 ppm by
                                                                       volume on a dry
                                                                       basis corrected to
                                                                       3 percent oxygen,
                                                                       10-day rolling
                                                                       average).
                                    b. Filterable PM (or TSM).......  3.0E-02 lb per MMBtu  Collect a minimum of
                                                                       of heat input; or     2 dscm per run.
                                                                       (6.5E-03 lb per
                                                                       MMBtu of heat
                                                                       input).
11. Dutch Ovens/Pile burners        a. CO (or CEMS).................  470 ppm by volume on  1 hr minimum
 designed to burn biomass/bio-                                         a dry basis           sampling time.
 based solids.                                                         corrected to 3
                                                                       percent oxygen, 3-
                                                                       run average; or
                                                                       (520 ppm by volume
                                                                       on a dry basis
                                                                       corrected to 3
                                                                       percent oxygen, 10-
                                                                       day rolling
                                                                       average).
                                    b. Filterable PM (or TSM).......  3.2E-03 lb per MMBtu  Collect a minimum of
                                                                       of heat input; or     3 dscm per run.
                                                                       (3.9E-05 lb per
                                                                       MMBtu of heat
                                                                       input).

12. Fuel cell units designed to     a. CO...........................  910 ppm by volume on  1 hr minimum
 burn biomass/bio-based solids.                                        a dry basis           sampling time.
                                                                       corrected to 3
                                                                       percent oxygen.
                                    b. Filterable PM (or TSM).......  2.0E-02 lb per MMBtu  Collect a minimum of
                                                                       of heat input; or     2 dscm per run.
                                                                       (2.9E-05 lb per
                                                                       MMBtu of heat
                                                                       input).
13. Hybrid suspension grate boiler  a. CO (or CEMS).................  1,500 ppm by volume   1 hr minimum
 designed to burn biomass/bio-                                         on a dry basis        sampling time.
 based solids.                                                         corrected to 3
                                                                       percent oxygen, 3-
                                                                       run average; or
                                                                       (900 ppm by volume
                                                                       on a dry basis
                                                                       corrected to 3
                                                                       percent oxygen, 30-
                                                                       day rolling
                                                                       average).
                                    b. Filterable PM (or TSM).......  2.6E-02 lb per MMBtu  Collect a minimum of
                                                                       of heat input; or     3 dscm per run.
                                                                       (4.4E-04 lb per
                                                                       MMBtu of heat
                                                                       input).
14. Units designed to burn liquid   a. HCl..........................  4.4E-04 lb per MMBtu  For M26A: Collect a
 fuel.                                                                 of heat input.        minimum of 2 dscm
                                                                                per run; for M26,
                                                                                collect a minimum
                                                                                of 240 liters per
                                                                                run.
                                    b. Mercury......................  4.8E-07 \a\ lb per    For M29, collect a
                                                                       MMBtu of heat input.  minimum of 4 dscm
                                                                                per run; for M30A
                                                                                or M30B, collect a
                                                                                minimum sample as
                                                                                specified in the
                                                                                method; for ASTM
                                                                                D6784 \b\ collect a
                                                                                minimum of 4 dscm.
15. Units designed to burn heavy    a. CO...........................  130 ppm by volume on  1 hr minimum
 liquid fuel.                                                          a dry basis           sampling time.
                                                                       corrected to 3
                                                                       percent oxygen, 3-
                                                                       run average.
                                    b. Filterable PM (or TSM).......  1.3E-02 lb per MMBtu  Collect a minimum of
                                                                       of heat input; or     2 dscm per run.
                                                                       (7.5E-05 lb per
                                                                       MMBtu of heat
                                                                       input).
16. Units designed to burn light    a. CO...........................  130 ppm by volume on  1 hr minimum
 liquid fuel.                                                          a dry basis           sampling time.
                                                                       corrected to 3
                                                                       percent oxygen.
                                    b. Filterable PM (or TSM).......  1.3E-03 \a\ lb per    Collect a minimum of
                                                                       MMBtu of heat         3 dscm per run.
                                                                       input; or (2.9E-05
                                                                       lb per MMBtu of
                                                                       heat input).
17. Units designed to burn liquid   a. CO...........................  130 ppm by volume on  1 hr minimum
 fuel that are non-continental                                         a dry basis           sampling time.
 units.                                                                corrected to 3
                                                                       percent oxygen, 3-
                                                                       run average based
                                                                       on stack test.
                                    b. Filterable PM (or TSM).......  2.3E-02 lb per MMBtu  Collect a minimum of
                                                                       of heat input; or     4 dscm per run.
                                                                       (8.6E-04 lb per
                                                                       MMBtu of heat
                                                                       input).
18. Units designed to burn gas 2    a. CO...........................  130 ppm by volume on  1 hr minimum
 (other) gases.                                                        a dry basis           sampling time.
                                                                       corrected to 3
                                                                       percent oxygen.
                                    b. HCl..........................  1.7E-03 lb per MMBtu  For M26A, Collect a
                                                                       of heat input.        minimum of 2 dscm
                                                                                per run; for M26,
                                                                                collect a minimum
                                                                                of 240 liters per
                                                                                run.
                                    c. Mercury......................  7.9E-06 lb per MMBtu  For M29, collect a
                                                                       of heat input.        minimum of 3 dscm
                                                                                per run; for M30A
                                                                                or M30B, collect a
                                                                                minimum sample as
                                                                                specified in the
                                                                                method; for ASTM
                                                                                D6784 \b\ collect a
                                                                                minimum of 3 dscm.
                                    d. Filterable PM (or TSM).......  6.7E-03 lb per MMBtu  Collect a minimum of
                                                                       of heat input; or     3 dscm per run.
                                                                       (2.1E-04 lb per
                                                                       MMBtu of heat
                                                                       input).
----------------------------------------------------------------------------------------------------------------
\a\ If you are conducting stack tests to demonstrate compliance and your performance tests for this pollutant
  for at least 2 consecutive years show that your emissions are at or below this limit, you can skip testing
  according to Sec.   63.7515 if all of the other provision of Sec.   63.7515 are met. For all other pollutants
  that do not contain a footnote ``a'', your performance tests for this pollutant for at least 2 consecutive
  years must show that your emissions are at or below 75 percent of this limit in order to qualify for skip
  testing.
\b\ Incorporated by reference, see Sec.   63.14.

0
40. Add Table 13 to subpart DDDDD of part 63 to read as follows:

 Table 13 to Subpart DDDDD of Part 63--Alternative Emission Limits for New or Reconstructed Boilers and Process
   Heaters That Commenced Construction or Reconstruction After December 23, 2011, and Before January 31, 2013
----------------------------------------------------------------------------------------------------------------
                                                                       The emissions must
                                                                         not exceed the
                                                                       following emission   Using this specified
 If your boiler or process heater   For the following pollutants . .     limits, except      sampling volume or
   is in this subcategory . . .                     .                   during periods of    test run duration .
                                                                      startup and shutdown           . .
                                                                              . . .
----------------------------------------------------------------------------------------------------------------
1. Units in all subcategories       a. HCl..........................  0.022 lb per MMBtu    For M26A, collect a
 designed to burn solid fuel.                                          of heat input.        minimum of 1 dscm
                                                                                per run; for M26
                                                                                collect a minimum
                                                                                of 120 liters per
                                                                                run.
                                    b. Mercury......................  8.6E-07 \a\ lb per    For M29, collect a
                                                                       MMBtu of heat input.  minimum of 4 dscm
                                                                                per run; for M30A
                                                                                or M30B, collect a
                                                                                minimum sample as
                                                                                specified in the
                                                                                method; for ASTM
                                                                                D6784 \b\ collect a
                                                                                minimum of 4 dscm.
2. Pulverized coal boilers          a. Carbon monoxide (CO) (or       130 ppm by volume on  1 hr minimum
 designed to burn coal/solid         CEMS).                            a dry basis           sampling time.
 fossil fuel.                                                          corrected to 3
                                                                       percent oxygen, 3-
                                                                       run average; or
                                                                       (320 ppm by volume
                                                                       on a dry basis
                                                                       corrected to 3
                                                                       percent oxygen, 30-
                                                                       day rolling
                                                                       average).
                                    b. Filterable PM (or TSM).......  1.1E-03 lb per MMBtu  Collect a minimum of
                                                                       of heat input; or     3 dscm per run.
                                                                       (2.8E-05 lb per
                                                                       MMBtu of heat
                                                                       input).
3. Stokers designed to burn coal/   a. CO (or CEMS).................  130 ppm by volume on  1 hr minimum
 solid fossil fuel.                                                    a dry basis           sampling time.
                                                                       corrected to 3
                                                                       percent oxygen, 3-
                                                                       run average; or
                                                                       (340 ppm by volume
                                                                       on a dry basis
                                                                       corrected to 3
                                                                       percent oxygen, 10-
                                                                       day rolling
                                                                       average).
                                    b. Filterable PM (or TSM).......  2.8E-02 lb per MMBtu  Collect a minimum of
                                                                       of heat input; or     2 dscm per run.
                                                                       (2.3E-05 lb per
                                                                       MMBtu of heat
                                                                       input).
4. Fluidized bed units designed to  a. CO (or CEMS).................  130 ppm by volume on  1 hr minimum
 burn coal/solid fossil fuel.                                          a dry basis           sampling time.
                                                                       corrected to 3
                                                                       percent oxygen, 3-
                                                                       run average; or
                                                                       (230 ppm by volume
                                                                       on a dry basis
                                                                       corrected to 3
                                                                       percent oxygen, 30-
                                                                       day rolling
                                                                       average).
                                    b. Filterable PM (or TSM).......  1.1E-03 lb per MMBtu  Collect a minimum of
                                                                       of heat input; or     3 dscm per run.
                                                                       (2.3E-05 lb per
                                                                       MMBtu of heat
                                                                       input).
5. Fluidized bed units with an      a. CO (or CEMS).................  140 ppm by volume on  1 hr minimum
 integrated heat exchanger                                             a dry basis           sampling time.
 designed to burn coal/solid                                           corrected to 3
 fossil fuel.                                                          percent oxygen, 3-
                                                                       run average; or
                                                                       (150 ppm by volume
                                                                       on a dry basis
                                                                       corrected to 3
                                                                       percent oxygen, 30-
                                                                       day rolling
                                                                       average).
                                    b. Filterable PM (or TSM).......  1.1E-03 lb per MMBtu  Collect a minimum of
                                                                       of heat input; or     3 dscm per run.
                                                                       (2.3E-05 lb per
                                                                       MMBtu of heat
                                                                       input).
6. Stokers/sloped grate/others      a. CO (or CEMS).................  620 ppm by volume on  1 hr minimum
 designed to burn wet biomass fuel.                                    a dry basis           sampling time.
                                                                       corrected to 3
                                                                       percent oxygen, 3-
                                                                       run average; or
                                                                       (410 ppm by volume
                                                                       on a dry basis
                                                                       corrected to 3
                                                                       percent oxygen, 10-
                                                                       day rolling
                                                                       average).
                                    b. Filterable PM (or TSM).......  3.0E-02 lb per MMBtu  Collect a minimum of
                                                                       of heat input; or     2 dscm per run.
                                                                       (2.6E-05 lb per
                                                                       MMBtu of heat
                                                                       input).
7. Stokers/sloped grate/others      a. CO...........................  460 ppm by volume on  1 hr minimum
 designed to burn kiln-dried                                           a dry basis           sampling time.
 biomass fuel.                                                         corrected to 3
                                                                       percent oxygen.
                                    b. Filterable PM (or TSM).......  3.2E-01 lb per MMBtu  Collect a minimum of
                                                                       of heat input; or     2 dscm per run.
                                                                       (4.0E-03 lb per
                                                                       MMBtu of heat
                                                                       input).
8. Fluidized bed units designed to  a. CO (or CEMS).................  230 ppm by volume on  1 hr minimum
 burn biomass/bio-based solids.                                        a dry basis           sampling time.
                                                                       corrected to 3
                                                                       percent oxygen, 3-
                                                                       run average; or
                                                                       (310 ppm by volume
                                                                       on a dry basis
                                                                       corrected to 3
                                                                       percent oxygen, 30-
                                                                       day rolling
                                                                       average).

                                    b. Filterable PM (or TSM).......  9.8E-03 lb per MMBtu  Collect a minimum of
                                                                       of heat input; or     3 dscm per run.
                                                                       (8.3E-05 \a\ lb per
                                                                       MMBtu of heat
                                                                       input).
9. Suspension burners designed to   a. CO (or CEMS).................  2,400 ppm by volume   1 hr minimum
 burn biomass/bio-based solids.                                        on a dry basis        sampling time.
                                                                       corrected to 3
                                                                       percent oxygen, 3-
                                                                       run average; or
                                                                       (2,000 ppm by
                                                                       volume on a dry
                                                                       basis corrected to
                                                                       3 percent oxygen,
                                                                       10-day rolling
                                                                       average).
                                    b. Filterable PM (or TSM).......  5.1E-02 lb per MMBtu  Collect a minimum of
                                                                       of heat input; or     2 dscm per run.
                                                                       (6.5E-03 lb per
                                                                       MMBtu of heat
                                                                       input).
10. Dutch Ovens/Pile burners        a. CO (or CEMS).................  810 ppm by volume on  1 hr minimum
 designed to burn biomass/bio-                                         a dry basis           sampling time.
 based solids.                                                         corrected to 3
                                                                       percent oxygen, 3-
                                                                       run average; or
                                                                       (520 ppm by volume
                                                                       on a dry basis
                                                                       corrected to 3
                                                                       percent oxygen, 10-
                                                                       day rolling
                                                                       average).
                                    b. Filterable PM (or TSM).......  3.6E-02 lb per MMBtu  Collect a minimum of
                                                                       of heat input; or     2 dscm per run.
                                                                       (3.9E-05 lb per
                                                                       MMBtu of heat
                                                                       input).
11. Fuel cell units designed to     a. CO...........................  910 ppm by volume on  1 hr minimum
 burn biomass/bio-based solids.                                        a dry basis           sampling time.
                                                                       corrected to 3
                                                                       percent oxygen.
                                    b. Filterable PM (or TSM).......  2.0E-02 lb per MMBtu  Collect a minimum of
                                                                       of heat input; or     2 dscm per run.
                                                                       (2.9E-05 lb per
                                                                       MMBtu of heat
                                                                       input).
12. Hybrid suspension grate boiler  a. CO (or CEMS).................  1,500 ppm by volume   1 hr minimum
 designed to burn biomass/bio-                                         on a dry basis        sampling time.
 based solids.                                                         corrected to 3
                                                                       percent oxygen, 3-
                                                                       run average; or
                                                                       (900 ppm by volume
                                                                       on a dry basis
                                                                       corrected to 3
                                                                       percent oxygen, 30-
                                                                       day rolling
                                                                       average).
                                    b. Filterable PM (or TSM).......  2.6E-02 lb per MMBtu  Collect a minimum of
                                                                       of heat input; or     3 dscm per run.
                                                                       (4.4E-04 lb per
                                                                       MMBtu of heat
                                                                       input).
13. Units designed to burn liquid   a. HCl..........................  1.2E-03 lb per MMBtu  For M26A: Collect a
 fuel.                                                                 of heat input.        minimum of 2 dscm
                                                                                per run; for M26,
                                                                                collect a minimum
                                                                                of 240 liters per
                                                                                run.
                                    b. Mercury......................  4.9E-07 \a\ lb per    For M29, collect a
                                                                       MMBtu of heat input.  minimum of 4 dscm
                                                                                per run; for M30A
                                                                                or M30B, collect a
                                                                                minimum sample as
                                                                                specified in the
                                                                                method; for ASTM
                                                                                D6784 \b\ collect a
                                                                                minimum of 4 dscm.
14. Units designed to burn heavy    a. CO (or CEMS).................  130 ppm by volume on  1 hr minimum
 liquid fuel.                                                          a dry basis           sampling time.
                                                                       corrected to 3
                                                                       percent oxygen, 3-
                                                                       run average; or (18
                                                                       ppm by volume on a
                                                                       dry basis corrected
                                                                       to 3 percent
                                                                       oxygen, 10-day
                                                                       rolling average).
                                    b. Filterable PM (or TSM).......  1.3E-03 lb per MMBtu  Collect a minimum of
                                                                       of heat input; or     3 dscm per run.
                                                                       (7.5E-05 lb per
                                                                       MMBtu of heat
                                                                       input).
15. Units designed to burn light    a. CO (or CEMS).................  130 \a\ ppm by        1 hr minimum
 liquid fuel.                                                          volume on a dry       sampling time.
                                                                       basis corrected to
                                                                       3 percent oxygen;
                                                                       or (60 ppm by
                                                                       volume on a dry
                                                                       basis corrected to
                                                                       3 percent oxygen, 1-
                                                                       day block average)..
                                    b. Filterable PM (or TSM).......  1.1E-03 \a\ lb per    Collect a minimum of
                                                                       MMBtu of heat         3 dscm per run.
                                                                       input; or (2.9E-05
                                                                       lb per MMBtu of
                                                                       heat input).
16. Units designed to burn liquid   a. CO...........................  130 ppm by volume on  1 hr minimum
 fuel that are non-continental                                         a dry basis           sampling time.
 units.                                                                corrected to 3
                                                                       percent oxygen, 3-
                                                                       run average based
                                                                       on stack test; or
                                                                       (91 ppm by volume
                                                                       on a dry basis
                                                                       corrected to 3
                                                                       percent oxygen, 3-
                                                                       hour rolling
                                                                       average).

                                    b. Filterable PM (or TSM).......  2.3E-02 lb per MMBtu  Collect a minimum of
                                                                       of heat input; or     2 dscm per run.
                                                                       (8.6E-04 lb per
                                                                       MMBtu of heat
                                                                       input).
17. Units designed to burn gas 2    a. CO...........................  130 ppm by volume on  1 hr minimum
 (other) gases.                                                        a dry basis           sampling time.
                                                                       corrected to 3
                                                                       percent oxygen.
                                    b. HCl..........................  1.7E-03 lb per MMBtu  For M26A, Collect a
                                                                       of heat input.        minimum of 2 dscm
                                                                                per run; for M26,
                                                                                collect a minimum
                                                                                of 240 liters per
                                                                                run.
                                    c. Mercury......................  7.9E-06 lb per MMBtu  For M29, collect a
                                                                       of heat input.        minimum of 3 dscm
                                                                                per run; for M30A
                                                                                or M30B, collect a
                                                                                minimum sample as
                                                                                specified in the
                                                                                method; for ASTM
                                                                                D6784 \b\ collect a
                                                                                minimum of 3 dscm.
                                    d. Filterable PM (or TSM).......  6.7E-03 lb per MMBtu  Collect a minimum of
                                                                       of heat input; or     3 dscm per run.
                                                                       (2.1E-04 lb per
                                                                       MMBtu of heat
                                                                       input).
----------------------------------------------------------------------------------------------------------------
\a\ If you are conducting stack tests to demonstrate compliance and your performance tests for this pollutant
  for at least 2 consecutive years show that your emissions are at or below this limit and you are not required
  to conduct testing for CEMS or CPMS monitor certification, you can skip testing according to Sec.   63.7515 if
  all of the other provision of Sec.   63.7515 are met. For all other pollutants that do not contain a footnote
  ``a'', your performance tests for this pollutant for at least 2 consecutive years must show that your
  emissions are at or below 75 percent of this limit in order to qualify for skip testing.
\b\ Incorporated by reference, see Sec.   63.14.

[FR Doc. 2012-31646 Filed 1-30-13; 8:45 am]
BILLING CODE 6560-50-P