content.
2. HCl.............................  a. Collect fuel samples....  Procedure in Sec.   63.7521(c) or ASTM D5192
                                                                   \a\, or ASTM D7430 \a\, or ASTM D6883 \a\, or
                                                                   ASTM D2234/D2234M \a\ (for coal) or ASTM
                                                                   D6323 \a\ (for coal or biomass), ASTM D4177
                                                                   \a\ (for liquid fuels) or ASTM D4057 \a\ (for
                                                                   liquid fuels), or equivalent.
                                     b. Composite fuel samples..  Procedure in Sec.   63.7521(d) or equivalent.
                                     c. Prepare composited fuel   EPA SW-846-3050B \a\ (for solid samples), ASTM
                                      samples.                     D2013/D2013M \a\ (for coal), or ASTM D5198
                                                                   \a\ (for biomass), or EPA 3050 \a\ or
                                                                   equivalent.
                                     d. Determine heat content    ASTM D5865 \a\ (for coal) or ASTM E711 \a\
                                      of the fuel type.            (for biomass), ASTM D5864, ASTM D240 \a\ or
                                                                   equivalent.
                                     e. Determine moisture        ASTM D3173 \a\ or ASTM E871 \a\, or D5864 \a\,
                                      content of the fuel type.    or ASTM D240 \a\, or ASTM D95 \a\ (for liquid
                                                                   fuels), or ASTM D4006 \a\ (for liquid fuels),
                                                                   or ASTM D4177 \a\ (for liquid fuels) or ASTM
                                                                   D4057 \a\ (for liquid fuels) or equivalent.
                                     f. Measure chlorine          EPA SW-846-9250 \a\, ASTM D6721 \a\, ASTM
                                      concentration in fuel        D4208 \a\ (for coal), or EPA SW-846-5050 \a\
                                      sample.                      or ASTM E776 \a\ (for solid fuel), or EPA SW-
                                                                   846-9056 \a\ or SW-846-9076 \a\ (for solids
                                                                   or liquids) or equivalent.
                                     g. Convert concentrations    Equation 7 in Sec.   63.7530.
                                      into units of pounds of
                                      HCl per MMBtu of heat
                                      content.
3. Mercury Fuel Specification for    a. Measure mercury           Method 30B (M30B) at 40 CFR part 60, appendix
 other gas 1 fuels.                   concentration in the fuel    A-8 of this chapter or ASTM D5954 \a\, ASTM
                                      sample and convert to        D6350 \a\, ISO 6978-1:2003(E) \a\, or ISO
                                      units of micrograms per      6978-2:2003(E) \a\, or EPA-1631 \a\ or
                                      cubic meter, or.             equivalent.
                                     b. Measure mercury           Method 29, 30A, or 30B (M29, M30A, or M30B) at
                                      concentration in the         40 CFR part 60, appendix A-8 of this chapter
                                      exhaust gas when firing      or Method 101A or Method 102 at 40 CFR part
                                      only the other gas 1 fuel    61, appendix B of this chapter, or ASTM
                                      is fired in the boiler or    Method D6784 \a\ or equivalent.
                                      process heater.
4. TSM.............................  a. Collect fuel samples....  Procedure in Sec.   63.7521(c) or ASTM D5192
                                                                   \a\, or ASTM D7430 \a\, or ASTM D6883 \a\, or
                                                                   ASTM D2234/D2234M \a\ (for coal) or ASTM
                                                                   D6323 \a\ (for coal or biomass), or ASTM
                                                                   D4177 \a\, (for liquid fuels)or ASTM D4057
                                                                   \a\ (for liquid fuels), or equivalent.
                                     b. Composite fuel samples..  Procedure in Sec.   63.7521(d) or equivalent.
                                     c. Prepare composited fuel   EPA SW-846-3050B \a\ (for solid samples), ASTM
                                      samples.                     D2013/D2013M \a\ (for coal), ASTM D5198 \a\
                                                                   or TAPPI T266 \a\ (for biomass), or EPA 3050
                                                                   \a\ or equivalent.
                                     d. Determine heat content    ASTM D5865 \a\ (for coal) or ASTM E711 \a\
                                      of the fuel type.            (for biomass), or ASTM D5864 \a\ for liquids
                                                                   and other solids, or ASTM D240 \a\ or
                                                                   equivalent.
                                     e. Determine moisture        ASTM D3173 \a\ or ASTM E871 \a\, or D5864, or
                                      content of the fuel type.    ASTM D240 \a\, or ASTM D95 \a\ (for liquid
                                                                   fuels), or ASTM D4006 \a\ (for liquid fuels),
                                                                   or ASTM D4177 \a\ (for liquid fuels) or ASTM
                                                                   D4057 \a\ (for liquid fuels), or equivalent.
                                     f. Measure TSM               ASTM D3683 \a\, or ASTM D4606 \a\, or ASTM
                                      concentration in fuel        D6357 \a\ or EPA 200.8 \a\ or EPA SW-846-6020
                                      sample.                      \a\, or EPA SW-846-6020A \a\, or EPA SW-846-
                                                                   6010C \a\, EPA 7060 \a\ or EPA 7060A \a\ (for
                                                                   arsenic only), or EPA SW-846-7740\a\ (for
                                                                   selenium only).
                                     g. Convert concentrations    Equation 9 in Sec.   63.7530.
                                      into units of pounds of
                                      TSM per MMBtu of heat
                                      content.
----------------------------------------------------------------------------------------------------------------
\a\ Incorporated by reference, see Sec.   63.14.

0
26. Table 7 to subpart DDDDD of part 63 is revised to read as follows:

                       Table 7 to Subpart DDDDD of Part 63--Establishing Operating Limits
    [As stated in Sec.   63.7520, you must comply with the following requirements for establishing operating
                                                    limits:]
----------------------------------------------------------------------------------------------------------------
                                   And your
  If you have an applicable       operating                                                   According to the
   emission limit for . . .       limits are       You must . . .          Using . . .            following
                                based on . . .                                                  requirements
----------------------------------------------------------------------------------------------------------------
1. PM, TSM, or mercury.......  a. Wet scrubber  i. Establish a site-  (1) Data from the     (a) You must collect
                                operating        specific minimum      scrubber pressure     scrubber pressure
                                parameters.      scrubber pressure     drop and liquid       drop and liquid
                                                 drop and minimum      flow rate monitors    flow rate data
                                                 flow rate operating   and the PM, TSM, or   every 15 minutes
                                                 limit according to    mercury performance   during the entire
                                                 Sec.   63.7530(b).    test.                 period of the
                                                                                performance tests.
                                                                                (b) Determine the
                                                                                lowest hourly
                                                                                average scrubber
                                                                                pressure drop and
                                                                                liquid flow rate by
                                                                                computing the
                                                                                hourly averages
                                                                                using all of the 15-
                                                                                minute readings
                                                                                taken during each
                                                                                performance test.
                               b.               i. Establish a site-  (1) Data from the     (a) You must collect
                                Electrostatic    specific minimum      voltage and           secondary voltage
                                precipitator     total secondary       secondary amperage    and secondary
                                operating        electric power        monitors during the   amperage for each
                                parameters       input according to    PM or mercury         ESP cell and
                                (option only     Sec.   63.7530(b).    performance test.     calculate total
                                for units that                                               secondary electric
                                operate wet                                                  power input data
                                scrubbers).                                                  every 15 minutes
                                                                                during the entire
                                                                                period of the
                                                                                performance tests.
                                                                                (b) Determine the
                                                                                average total
                                                                                secondary electric
                                                                                power input by
                                                                                computing the
                                                                                hourly averages
                                                                                using all of the 15-
                                                                                minute readings
                                                                                taken during each
                                                                                performance test.
2. HCl.......................  a. Wet scrubber  i. Establish site-    (1) Data from the pH  (a) You must collect
                                operating        specific minimum      and liquid flow-      pH and liquid flow-
                                parameters.      effluent pH and       rate monitors and     rate data every 15
                                                 flow rate operating   the HCl performance   minutes during the
                                                 limits according to   test.                 entire period of
                                                 Sec.   63.7530(b).                          the performance
                                                                                tests.
                                                                                (b) Determine the
                                                                                hourly average pH
                                                                                and liquid flow
                                                                                rate by computing
                                                                                the hourly averages
                                                                                using all of the 15-
                                                                                minute readings
                                                                                taken during each
                                                                                performance test.
                               b. Dry scrubber  i. Establish a site-  (1) Data from the     (a) You must collect
                                operating        specific minimum      sorbent injection     sorbent injection
                                parameters.      sorbent injection     rate monitors and     rate data every 15
                                                 rate operating        HCl or mercury        minutes during the
                                                 limit according to    performance test.     entire period of
                                                 Sec.   63.7530(b).                          the performance
                                                 If different acid                           tests.
                                                 gas sorbents are
                                                 used during the HCl
                                                 performance test,
                                                 the average value
                                                 for each sorbent
                                                 becomes the site-
                                                 specific operating
                                                 limit for that
                                                 sorbent.
                                                                                (b) Determine the
                                                                                hourly average
                                                                                sorbent injection
                                                                                rate by computing
                                                                                the hourly averages
                                                                                using all of the 15-
                                                                                minute readings
                                                                                taken during each
                                                                                performance test.
                                                                                (c) Determine the
                                                                                lowest hourly
                                                                                average of the
                                                                                three test run
                                                                                averages
                                                                                established during
                                                                                the performance
                                                                                test as your
                                                                                operating limit.
                                                                                When your unit
                                                                                operates at lower
                                                                                loads, multiply
                                                                                your sorbent
                                                                                injection rate by
                                                                                the load fraction,
                                                                                as defined in Sec.
                                                                                63.7575, to
                                                                                determine the
                                                                                required injection
                                                                                rate.
                               c. Alternative   i. Establish a site-  (1) Data from SO2     (a) You must collect
                                Maximum SO2      specific maximum      CEMS and the HCl      the SO2 emissions
                                emission rate.   SO2 emission rate     performance test.     data according to
                                                 operating limit                             Sec.   63.7525(m)
                                                 according to Sec.                           during the most
                                                 63.7530(b).                                 recent HCl
                                                                                performance tests.

                                                                                (b) The maximum SO2
                                                                                emission rate is
                                                                                equal to the
                                                                                highest hourly
                                                                                average SO2
                                                                                emission rate
                                                                                measured during the
                                                                                most recent HCl
                                                                                performance tests.
3. Mercury...................  a. Activated     i. Establish a site-  (1) Data from the     (a) You must collect
                                carbon           specific minimum      activated carbon      activated carbon
                                injection.       activated carbon      rate monitors and     injection rate data
                                                 injection rate        mercury performance   every 15 minutes
                                                 operating limit       test.                 during the entire
                                                 according to Sec.                           period of the
                                                 63.7530(b).                                 performance tests.
                                                                                (b) Determine the
                                                                                hourly average
                                                                                activated carbon
                                                                                injection rate by
                                                                                computing the
                                                                                hourly averages
                                                                                using all of the 15-
                                                                                minute readings
                                                                                taken during each
                                                                                performance test.
                                                                                (c) Determine the
                                                                                lowest hourly
                                                                                average established
                                                                                during the
                                                                                performance test as
                                                                                your operating
                                                                                limit. When your
                                                                                unit operates at
                                                                                lower loads,
                                                                                multiply your
                                                                                activated carbon
                                                                                injection rate by
                                                                                the load fraction,
                                                                                as defined in Sec.
                                                                                63.7575, to
                                                                                determine the
                                                                                required injection
                                                                                rate.
4. Carbon monoxide for which   a. Oxygen......  i. Establish a unit-  (1) Data from the     (a) You must collect
 compliance is demonstrated                      specific limit for    oxygen analyzer       oxygen data every
 by a performance test.                          minimum oxygen        system specified in   15 minutes during
                                                 level according to    Sec.   63.7525(a).    the entire period
                                                 Sec.   63.7530(b).                          of the performance
                                                                                tests.
                                                                                (b) Determine the
                                                                                hourly average
                                                                                oxygen
                                                                                concentration by
                                                                                computing the
                                                                                hourly averages
                                                                                using all of the 15-
                                                                                minute readings
                                                                                taken during each
                                                                                performance test.
                                                                                (c) Determine the
                                                                                lowest hourly
                                                                                average established
                                                                                during the
                                                                                performance test as
                                                                                your minimum
                                                                                operating limit.
5. Any pollutant for which     a. Boiler or     i. Establish a unit   (1) Data from the     (a) You must collect
 compliance is demonstrated     process heater   specific limit for    operating load        operating load or
 by a performance test.         operating load.  maximum operating     monitors or from      steam generation
                                                 load according to     steam generation      data every 15
                                                 Sec.   63.7520(c).    monitors.             minutes during the
                                                                                entire period of
                                                                                the performance
                                                                                test.
                                                                                (b) Determine the
                                                                                average operating
                                                                                load by computing
                                                                                the hourly averages
                                                                                using all of the 15-
                                                                                minute readings
                                                                                taken during each
                                                                                performance test.
                                                                                (c) Determine the
                                                                                average of the
                                                                                three test run
                                                                                averages during the
                                                                                performance test,
                                                                                and multiply this
                                                                                by 1.1 (110
                                                                                percent) as your
                                                                                operating limit.
----------------------------------------------------------------------------------------------------------------

0
27. Table 8 to subpart DDDDD of part 63 is amended by revising the
entry for ``3,'' ``9,'' ``10,'' and ``11'' to read as follows:

Table 8 to Subpart DDDDD of Part 63--Demonstrating Continuous Compliance
 [As stated in Sec.   63.7540, you must show continuous compliance with
 the emission limitations for each boiler or process heater according to
                             the following:]
------------------------------------------------------------------------
     If you must meet the
following operating limits or       You must demonstrate continuous
work practice standards . . .             compliance by . . .
------------------------------------------------------------------------

                                * * * * *
3. Fabric Filter Bag Leak      Installing and operating a bag leak
 Detection Operation.           detection system according to Sec.
                                63.7525 and operating the fabric filter
                                such that the requirements in Sec.
                                63.7540(a)(7) are met.

                                * * * * *
9. Oxygen content............  a. Continuously monitor the oxygen
                                content using an oxygen analyzer system
                                according to Sec.   63.7525(a). This
                                requirement does not apply to units that
                                install an oxygen trim system since
                                these units will set the trim system to
                                the level specified in Sec.
                                63.7525(a)(7).
                               b. Reducing the data to 30-day rolling
                                averages; and
                               c. Maintain the 30-day rolling average
                                oxygen content at or above the lowest
                                hourly average oxygen level measured
                                during the most recent CO performance
                                test.
10. Boiler or process heater   a. Collecting operating load data or
 operating load.                steam generation data every 15 minutes.
                               b. Reducing the data to 30-day rolling
                                averages; and
                               b. Maintaining the 30-day rolling average
                                operating load such that it does not
                                exceed 110 percent of the highest hourly
                                average operating load recorded during
                                the most recent performance test
                                according to Sec.   63.7520(c).
11. SO2emissions using         a. Collecting the SO2CEMS output data
 SO2CEMS.                       according to Sec.   63.7525;
                               b. Reducing the data to 30-day rolling
                                averages; and
                               c. Maintaining the 30-day rolling average
                                SO2CEMS emission rate to a level at or
                                below the highest hourly SO2rate
                                measured during the most recent HCl
                                performance test according to Sec.
                                63.7530.
------------------------------------------------------------------------

0
28. Table 9 to subpart DDDDD of part 63 is revised to read as follows:

       Table 9 to Subpart DDDDD of Part 63--Reporting Requirements
    [As stated in Sec.   63.7550, you must comply with the following
                       requirements for reports:]
------------------------------------------------------------------------
                                                         You must submit
    You must submit a(n)      The report must contain .   the report . .
                                         . .                    .
------------------------------------------------------------------------
1. Compliance report........  a. Information required    Semiannually,
                               in Sec.   63.7550(c)(1)    annually,
                               through (5); and.          biennially, or
                                                          every 5 years
                                                          according to
                                                          the
                                                          requirements
                                                          in Sec.
                                                          63.7550(b).
                              b. If there are no
                               deviations from any
                               emission limitation
                               (emission limit and
                               operating limit) that
                               applies to you and there
                               are no deviations from
                               the requirements for
                               work practice standards
                               for periods of startup
                               and shutdown in Table 3
                               to this subpart that
                               apply to you, a
                               statement that there
                               were no deviations from
                               the emission limitations
                               and work practice
                               standards during the
                               reporting period. If
                               there were no periods
                               during which the CMSs,
                               including continuous
                               emissions monitoring
                               system, continuous
                               opacity monitoring
                               system, and operating
                               parameter monitoring
                               systems, were out-of-
                               control as specified in
                               Sec.   63.8(c)(7), a
                               statement that there
                               were no periods during
                               which the CMSs were out-
                               of-control during the
                               reporting period; and.
                              c. If you have a
                               deviation from any
                               emission limitation
                               (emission limit and
                               operating limit) where
                               you are not using a CMS
                               to comply with that
                               emission limit or
                               operating limit, or a
                               deviation from a work
                               practice standard for
                               periods of startup and
                               shutdown, during the
                               reporting period, the
                               report must contain the
                               information in Sec.
                               63.7550(d); and.
                              d. If there were periods
                               during which the CMSs,
                               including continuous
                               emissions monitoring
                               system, continuous
                               opacity monitoring
                               system, and operating
                               parameter monitoring
                               systems, were out-of-
                               control as specified in
                               Sec.   63.8(c)(7), or
                               otherwise not operating,
                               the report must contain
                               the information in Sec.
                                63.7550(e).
------------------------------------------------------------------------

* * * * *
0
29. Table 11 to subpart DDDDD of part 63 is revised to read as follows:

 Table 11 to Subpart DDDDD of Part 63--Alternative Emission Limits for New or Reconstructed Boilers and Process
        Heaters That Commenced Construction or Reconstruction After June 4, 2010, and Before May 20, 2011
----------------------------------------------------------------------------------------------------------------
                                                                 The emissions must not
                                                                  exceed the following
 If your boiler or process heater is      For the following     emission limits, except    Using this specified
      in this subcategory . . .            pollutants . . .        during periods of     sampling volume or test
                                                                 startup and shutdown .     run duration . . .
                                                                          . .
----------------------------------------------------------------------------------------------------------------
1. Units in all subcategories          a. HCl.................  0.022 lb per MMBtu of    For M26A, collect a
 designed to burn solid fuel.                                    heat input.              minimum of 1 dscm per
                                                                                run; for M26 collect a
                                                                                minimum of 120 liters
                                                                                per run.
2. Units in all subcategories          a. Mercury.............  8.0E-07 \a\ lb per       For M29, collect a
 designed to burn solid fuel that                                MMBtu of heat input.     minimum of 4 dscm per
 combust at least 10 percent biomass/                                                     run; for M30A or M30B,
 bio-based solids on an annual heat                                                       collect a minimum
 input basis and less than 10 percent                                                     sample as specified in
 coal/solid fossil fuels on an annual                                                     the method; for ASTM
 heat input basis.                                                                        D6784 \b\ collect a
                                                                                minimum of 4 dscm.
3. Units in all subcategories          a. Mercury.............  2.0E-06 lb per MMBtu of  For M29, collect a
 designed to burn solid fuel that                                heat input.              minimum of 4 dscm per
 combust at least 10 percent coal/                                                        run; for M30A or M30B,
 solid fossil fuels on an annual heat                                                     collect a minimum
 input basis and less than 10 percent                                                     sample as specified in
 biomass/bio-based solids on an                                                           the method; for ASTM
 annual heat input basis.                                                                 D6784 \b\ collect a
                                                                                minimum of 4 dscm.
4. Units design to burn coal/solid     a. Filterable PM (or     1.1E-03 lb per MMBtu of  Collect a minimum of 3
 fossil fuel.                           TSM).                    heat input; or (2.3E-    dscm per run.
                                                                 05 lb per MMBtu of
                                                                 heat input).
5. Pulverized coal boilers designed    a. Carbon monoxide (CO)  130 ppm by volume on a   1 hr minimum sampling
 to burn coal/solid fossil fuel.        (or CEMS).               dry basis corrected to   time.
                                                                 3 percent oxygen, 3-
                                                                 run average; or (320
                                                                 ppm by volume on a dry
                                                                 basis corrected to 3
                                                                 percent oxygen \c\, 30-
                                                                 day rolling average).
6. Stokers designed to burn coal/      a. CO (or CEMS)........  130 ppm by volume on a   1 hr minimum sampling
 solid fossil fuel.                                              dry basis corrected to   time.
                                                                 3 percent oxygen, 3-
                                                                 run average; or (340
                                                                 ppm by volume on a dry
                                                                 basis corrected to 3
                                                                 percent oxygen \c\, 10-
                                                                 day rolling average).
7. Fluidized bed units designed to     a. CO (or CEMS)........  130 ppm by volume on a   1 hr minimum sampling
 burn coal/solid fossil fuel.                                    dry basis corrected to   time
                                                                 3 percent oxygen, 3-
                                                                 run average; or (230
                                                                 ppm by volume on a dry
                                                                 basis corrected to 3
                                                                 percent oxygen \c\, 30-
                                                                 day rolling average).
8. Fluidized bed units with an         a. CO (or CEMS)........  140 ppm by volume on a   1 hr minimum sampling
 integrated heat exchanger designed                              dry basis corrected to   time.
 to burn coal/solid fossil fuel.                                 3 percent oxygen, 3-
                                                                 run average; or (150
                                                                 ppm by volume on a dry
                                                                 basis corrected to 3
                                                                 percent oxygen \c\, 30-
                                                                 day rolling average).
9. Stokers/sloped grate/others         a. CO (or CEMS)........  620 ppm by volume on a   1 hr minimum sampling
 designed to burn wet biomass fuel.                              dry basis corrected to   time.
                                                                 3 percent oxygen, 3-
                                                                 run average; or (390
                                                                 ppm by volume on a dry
                                                                 basis corrected to 3
                                                                 percent oxygen \c\, 30-
                                                                 day rolling average).
                                       b. Filterable PM (or     3.0E-02 lb per MMBtu of  Collect a minimum of 2
                                        TSM).                    heat input; or (2.6E-    dscm per run.
                                                                 05 lb per MMBtu of
                                                                 heat input).
10. Stokers/sloped grate/others        a. CO..................  560 ppm by volume on a   1 hr minimum sampling
 designed to burn kiln-dried biomass                             dry basis corrected to   time.
 fuel.                                                           3 percent oxygen.
                                       b. Filterable PM (or     3.0E-02 lb per MMBtu of  Collect a minimum of 2
                                        TSM).                    heat input; or (4.0E-    dscm per run.
                                                                 03 lb per MMBtu of
                                                                 heat input).

11. Fluidized bed units designed to    a. CO (or CEMS)........  230 ppm by volume on a   1 hr minimum sampling
 burn biomass/bio-based solids.                                  dry basis corrected to   time.
                                                                 3 percent oxygen, 3-
                                                                 run average; or (310
                                                                 ppm by volume on a dry
                                                                 basis corrected to 3
                                                                 percent oxygen \c\, 30-
                                                                 day rolling average).
                                       b. Filterable PM (or     9.8E-03 lb per MMBtu of  Collect a minimum of 3
                                        TSM).                    heat input; or (8.3E-    dscm per run.
                                                                 05 \a\ lb per MMBtu of
                                                                 heat input).
12. Suspension burners designed to     a. CO (or CEMS)........  2,400 ppm by volume on   1 hr minimum sampling
 burn biomass/bio-based solids.                                  a dry basis corrected    time.
                                                                 to 3 percent oxygen, 3-
                                                                 run average; or (2,000
                                                                 ppm by volume on a dry
                                                                 basis corrected to 3
                                                                 percent oxygen \c\, 10-
                                                                 day rolling average).
                                       b. Filterable PM (or     3.0E-02 lb per MMBtu of  Collect a minimum of 2
                                        TSM).                    heat input; or (6.5E-    dscm per run.
                                                                 03 lb per MMBtu of
                                                                 heat input).
13. Dutch Ovens/Pile burners designed  a. CO (or CEMS)........  1,010 ppm by volume on   1 hr minimum sampling
 to burn biomass/bio-based solids.                               a dry basis corrected    time.
                                                                 to 3 percent oxygen, 3-
                                                                 run average; or (520
                                                                 ppm by volume on a dry
                                                                 basis corrected to 3
                                                                 percent oxygen \c\, 10-
                                                                 day rolling average).
                                       b. Filterable PM (or     8.0E-03 lb per MMBtu of  Collect a minimum of 3
                                        TSM).                    heat input; or (3.9E-    dscm per run.
                                                                 05 lb per MMBtu of
                                                                 heat input).
14. Fuel cell units designed to burn   a. CO..................  910 ppm by volume on a   1 hr minimum sampling
 biomass/bio-based solids.                                       dry basis corrected to   time.
                                                                 3 percent oxygen.
                                       b. Filterable PM (or     2.0E-02 lb per MMBtu of  Collect a minimum of 2
                                        TSM).                    heat input; or (2.9E-    dscm per run.
                                                                 05 lb per MMBtu of
                                                                 heat input).
15. Hybrid suspension grate boiler     a. CO (or CEMS)........  1,100 ppm by volume on   1 hr minimum sampling
 designed to burn biomass/bio-based                              a dry basis corrected    time.
 solids.                                                         to 3 percent oxygen, 3-
                                                                 run average; or (900
                                                                 ppm by volume on a dry
                                                                 basis corrected to 3
                                                                 percent oxygen \c\, 30-
                                                                 day rolling average).
                                       b. Filterable PM (or     2.6E-02 lb per MMBtu of  Collect a minimum of 3
                                        TSM).                    heat input; or (4.4E-    dscm per run.
                                                                 04 lb per MMBtu of
                                                                 heat input).
16. Units designed to burn liquid      a. HCl.................  4.4E-04 lb per MMBtu of  For M26A: Collect a
 fuel.                                                           heat input.              minimum of 2 dscm per
                                                                                run; for M26, collect
                                                                                a minimum of 240
                                                                                liters per run.
                                       b. Mercury.............  4.8E-07 \a\ lb per       For M29, collect a
                                                                 MMBtu of heat input.     minimum of 4 dscm per
                                                                                run; for M30A or M30B,
                                                                                collect a minimum
                                                                                sample as specified in
                                                                                the method; for ASTM
                                                                                D6784 \b\ collect a
                                                                                minimum of 4 dscm.
17. Units designed to burn heavy       a. CO..................  130 ppm by volume on a   1 hr minimum sampling
 liquid fuel.                                                    dry basis corrected to   time.
                                                                 3 percent oxygen, 3-
                                                                 run average.
                                       b. Filterable PM (or     1.3E-02 lb per MMBtu of  Collect a minimum of 3
                                        TSM).                    heat input; or (7.5E-    dscm per run.
                                                                 05 lb per MMBtu of
                                                                 heat input).
18. Units designed to burn light       a. CO..................  130 ppm by volume on a   1 hr minimum sampling
 liquid fuel.                                                    dry basis corrected to   time.
                                                                 3 percent oxygen.
                                       b. Filterable PM (or     2.0E-03 \a\ lb per       Collect a minimum of 3
                                        TSM).                    MMBtu of heat input;     dscm per run.
                                                                 or (2.9E-05 lb per
                                                                 MMBtu of heat input).

19. Units designed to burn liquid      a. CO..................  130 ppm by volume on a   1 hr minimum sampling
 fuel that are non-continental units.                            dry basis corrected to   time.
                                                                 3 percent oxygen, 3-
                                                                 run average based on
                                                                 stack test.
                                       b. Filterable PM (or     2.3E-02 lb per MMBtu of  Collect a minimum of 4
                                        TSM).                    heat input; or (8.6E-    dscm per run.
                                                                 04 lb per MMBtu of
                                                                 heat input).
20. Units designed to burn gas 2       a. CO..................  130 ppm by volume on a   1 hr minimum sampling
 (other) gases.                                                  dry basis corrected to   time.
                                                                 3 percent oxygen.
                                       b. HCl.................  1.7E-03 lb per MMBtu of  For M26A, Collect a
                                                                 heat input.              minimum of 2 dscm per
                                                                                run; for M26, collect
                                                                                a minimum of 240
                                                                                liters per run.
                                       c. Mercury.............  7.9E-06 lb per MMBtu of  For M29, collect a
                                                                 heat input.              minimum of 3 dscm per
                                                                                run; for M30A or M30B,
                                                                                collect a minimum
                                                                                sample as specified in
                                                                                the method; for ASTM
                                                                                D6784 \b\ collect a
                                                                                minimum of 3 dscm.
                                       d. Filterable PM (or     6.7E-03 lb per MMBtu of  Collect a minimum of 3
                                        TSM).                    heat input; or (2.1E-    dscm per run.
                                                                 04 lb per MMBtu of
                                                                 heat input).
----------------------------------------------------------------------------------------------------------------
\a\ If you are conducting stack tests to demonstrate compliance and your performance tests for this pollutant
  for at least 2 consecutive years show that your emissions are at or below this limit, you can skip testing
  according to Sec.   63.7515 if all of the other provision of Sec.   63.7515 are met. For all other pollutants
  that do not contain a footnote ``a'', your performance tests for this pollutant for at least 2 consecutive
  years must show that your emissions are at or below 75 percent of this limit in order to qualify for skip
  testing.
\b\ Incorporated by reference, see Sec.   63.14.
\c\ An owner or operator may request that compliance with the carbon monoxide emission limit be determined using
  carbon dioxide measurements corrected to an equivalent of 3 percent oxygen. The relationship between oxygen
  and carbon dioxide levels for the affected facility shall be established during the initial compliance test.

0
29. Table 12 to subpart DDDDD of part 63 is revised to read as follows:

 Table 12 to Subpart DDDDD of Part 63--Alternative Emission Limits for New or Reconstructed Boilers and Process
     Heaters That Commenced Construction or Reconstruction After May 20, 2011, and Before December 23, 2011
----------------------------------------------------------------------------------------------------------------
                                                             The emissions must not
                                                              exceed the following        Using this specified
 If your boiler or process heater     For the following      emission limits, except    sampling volume or test
   is in this subcategory . . .        pollutants . . .     during periods of startup      run duration . . .
                                                               and shutdown . . .
----------------------------------------------------------------------------------------------------------------
1. Units in all subcategories       a. HCl...............  0.022 lb per MMBtu of heat  For M26A, collect a
 designed to burn solid fuel.                               input.                      minimum of 1 dscm per
                                                                                run; for M26 collect a
                                                                                minimum of 120 liters
                                                                                per run.
                                    b. Mercury...........  3.5E-06 \a\ lb per MMBtu    For M29, collect a
                                                            of heat input.              minimum of 3 dscm per
                                                                                run; for M30A or M30B,
                                                                                collect a minimum sample
                                                                                as specified in the
                                                                                method; for ASTM D6784
                                                                                \b\ collect a minimum of
                                                                                3 dscm.
2. Units design to burn coal/solid  a. Filterable PM (or   1.1E-03 lb per MMBtu of     Collect a minimum of 3
 fossil fuel.                        TSM).                  heat input; or (2.3E-05     dscm per run.
                                                            lb per MMBtu of heat
                                                            input).
3. Pulverized coal boilers          a. Carbon monoxide     130 ppm by volume on a dry  1 hr minimum sampling
 designed to burn coal/solid         (CO) (or CEMS)         basis corrected to 3        time.
 fossil fuel.                                               percent oxygen, 3-run
                                                            average; or (320 ppm by
                                                            volume on a dry basis
                                                            corrected to 3 percent
                                                            oxygen \c\, 30-day
                                                            rolling average)
4. Stokers designed to burn coal/   a. CO (or CEMS)......  130 ppm by volume on a dry  1 hr minimum sampling
 solid fossil fuel.                                         basis corrected to 3        time.
                                                            percent oxygen, 3-run
                                                            average; or (340 ppm by
                                                            volume on a dry basis
                                                            corrected to 3 percent
                                                            oxygen \c\, 10-day
                                                            rolling average)

5. Fluidized bed units designed to  a. CO (or CEMS)......  130 ppm by volume on a dry  1 hr minimum sampling
 burn coal/solid fossil fuel.                               basis corrected to 3        time.
                                                            percent oxygen, 3-run
                                                            average; or (230 ppm by
                                                            volume on a dry basis
                                                            corrected to 3 percent
                                                            oxygen \c\, 30-day
                                                            rolling average)
6. Fluidized bed units with an      a. CO (or CEMS)......  140 ppm by volume on a dry  1 hr minimum sampling
 integrated heat exchanger                                  basis corrected to 3        time.
 designed to burn coal/solid                                percent oxygen, 3-run
 fossil fuel.                                               average; or (150 ppm by
                                                            volume on a dry basis
                                                            corrected to 3 percent
                                                            oxygen \c\, 30-day
                                                            rolling average)
7. Stokers/sloped grate/others      a. CO (or CEMS)......  620 ppm by volume on a dry  1 hr minimum sampling
 designed to burn wet biomass fuel.                         basis corrected to 3        time.
                                                            percent oxygen, 3-run
                                                            average; or (390 ppm by
                                                            volume on a dry basis
                                                            corrected to 3 percent
                                                            oxygen \c\, 30-day
                                                            rolling average)
                                    b. Filterable PM (or   3.0E-02 lb per MMBtu of     Collect a minimum of 2
                                     TSM).                  heat input; or (2.6E-05     dscm per run.
                                                            lb per MMBtu of heat
                                                            input)
8. Stokers/sloped grate/others      a. CO................  460 ppm by volume on a dry  1 hr minimum sampling
 designed to burn kiln-dried                                basis corrected to 3        time.
 biomass fuel.                                              percent oxygen
                                    b. Filterable PM (or   3.0E-02 lb per MMBtu of     Collect a minimum of 2
                                     TSM).                  heat input; or (4.0E-03     dscm per run.
                                                            lb per MMBtu of heat
                                                            input)
9. Fluidized bed units designed to  a. CO (or CEMS)......  260 ppm by volume on a dry  1 hr minimum sampling
 burn biomass/bio-based solids.                             basis corrected to 3        time.
                                                            percent oxygen, 3-run
                                                            average; or (310 ppm by
                                                            volume on a dry basis
                                                            corrected to 3 percent
                                                            oxygen \c\, 30-day
                                                            rolling average)
                                    b. Filterable PM (or   9.8E-03 lb per MMBtu of     Collect a minimum of 3
                                     TSM).                  heat input; or (8.3E-05     dscm per run.
                                                            \a\ lb per MMBtu of heat
                                                            input)
10. Suspension burners designed to  a. CO (or CEMS)......  2,400 ppm by volume on a    1 hr minimum sampling
 burn biomass/bio-based solids.                             dry basis corrected to 3    time.
                                                            percent oxygen, 3-run
                                                            average; or (2,000 ppm by
                                                            volume on a dry basis
                                                            corrected to 3 percent
                                                            oxygen \c\, 10-day
                                                            rolling average)
                                    b. Filterable PM (or   3.0E-02 lb per MMBtu of     Collect a minimum of 2
                                     TSM).                  heat input; or (6.5E-03     dscm per run.
                                                            lb per MMBtu of heat
                                                            input)
11. Dutch Ovens/Pile burners        a. CO (or CEMS)......  470 ppm by volume on a dry  1 hr minimum sampling
 designed to burn biomass/bio-                              basis corrected to 3        time.
 based solids.                                              percent oxygen, 3-run
                                                            average; or (520 ppm by
                                                            volume on a dry basis
                                                            corrected to 3 percent
                                                            oxygen \c\, 10-day
                                                            rolling average)
                                    b. Filterable PM (or   3.2E-03 lb per MMBtu of     Collect a minimum of 3
                                     TSM).                  heat input; or (3.9E-05     dscm per run.
                                                            lb per MMBtu of heat
                                                            input)
12. Fuel cell units designed to     a. CO................  910 ppm by volume on a dry  1 hr minimum sampling
 burn biomass/bio-based solids.                             basis corrected to 3        time.
                                                            percent oxygen
                                    b. Filterable PM (or   2.0E-02 lb per MMBtu of     Collect a minimum of 2
                                     TSM).                  heat input; or (2.9E-05     dscm per run.
                                                            lb per MMBtu of heat
                                                            input)
13. Hybrid suspension grate boiler  a. CO (or CEMS)......  1,500 ppm by volume on a    1 hr minimum sampling
 designed to burn biomass/bio-                              dry basis corrected to 3    time.
 based solids.                                              percent oxygen, 3-run
                                                            average; or (900 ppm by
                                                            volume on a dry basis
                                                            corrected to 3 percent
                                                            oxygen \c\, 30-day
                                                            rolling average)
                                    b. Filterable PM (or   2.6E-02 lb per MMBtu of     Collect a minimum of 3
                                     TSM).                  heat input; or (4.4E-04     dscm per run.
                                                            lb per MMBtu of heat
                                                            input)
14. Units designed to burn liquid   a. HCl...............  4.4E-04 lb per MMBtu of     For M26A: Collect a
 fuel.                                                      heat input.                 minimum of 2 dscm per
                                                                                run; for M26, collect a
                                                                                minimum of 240 liters
                                                                                per run.

                                    b. Mercury...........  4.8E-07 \a\ lb per MMBtu    For M29, collect a
                                                            of heat input.              minimum of 4 dscm per
                                                                                run; for M30A or M30B,
                                                                                collect a minimum sample
                                                                                as specified in the
                                                                                method; for ASTM D6784
                                                                                \b\ collect a minimum of
                                                                                4 dscm.
15. Units designed to burn heavy    a. CO................  130 ppm by volume on a dry  1 hr minimum sampling
 liquid fuel.                                               basis corrected to 3        time.
                                                            percent oxygen, 3-run
                                                            average
                                    b. Filterable PM (or   1.3E-02 lb per MMBtu of     Collect a minimum of 2
                                     TSM).                  heat input; or (7.5E-05     dscm per run.
                                                            lb per MMBtu of heat
                                                            input)
16. Units designed to burn light    a. CO................  130 ppm by volume on a dry  1 hr minimum sampling
 liquid fuel.                                               basis corrected to 3        time.
                                                            percent oxygen
                                    b. Filterable PM (or   1.3E-03 \a\ lb per MMBtu    Collect a minimum of 3
                                     TSM).                  of heat input; or (2.9E-    dscm per run.
                                                            05 lb per MMBtu of heat
                                                            input)
17. Units designed to burn liquid   a. CO................  130 ppm by volume on a dry  1 hr minimum sampling
 fuel that are non-continental                              basis corrected to 3        time.
 units                                                      percent oxygen, 3-run
                                                            average based on stack
                                                            test
                                    b. Filterable PM (or   2.3E-02 lb per MMBtu of     Collect a minimum of 4
                                     TSM).                  heat input; or (8.6E-04     dscm per run.
                                                            lb per MMBtu of heat
                                                            input)
18. Units designed to burn gas 2    a. CO................  130 ppm by volume on a dry  1 hr minimum sampling
 (other) gases.                                             basis corrected to 3        time.
                                                            percent oxygen
                                    b. HCl...............  1.7E-03 lb per MMBtu of     For M26A, Collect a
                                                            heat input.                 minimum of 2 dscm per
                                                                                run; for M26, collect a
                                                                                minimum of 240 liters
                                                                                per run.
                                    c. Mercury...........  7.9E-06 lb per MMBtu of     For M29, collect a
                                                            heat input.                 minimum of 3 dscm per
                                                                                run; for M30A or M30B,
                                                                                collect a minimum sample
                                                                                as specified in the
                                                                                method; for ASTM D6784
                                                                                \b\ collect a minimum of
                                                                                3 dscm.
                                    d. Filterable PM (or   6.7E-03 lb per MMBtu of     Collect a minimum of 3
                                     TSM).                  heat input; or (2.1E-04     dscm per run.
                                                            lb per MMBtu of heat
                                                            input)
----------------------------------------------------------------------------------------------------------------
\a\ If you are conducting stack tests to demonstrate compliance and your performance tests for this pollutant
  for at least 2 consecutive years show that your emissions are at or below this limit, you can skip testing
  according to Sec.   63.7515 if all of the other provision of Sec.   63.7515 are met. For all other pollutants
  that do not contain a footnote ``a'', your performance tests for this pollutant for at least 2 consecutive
  years must show that your emissions are at or below 75 percent of this limit in order to qualify for skip
  testing.
\b\ Incorporated by reference, see Sec.   63.14.
\c\ An owner or operator may request that compliance with the carbon monoxide emission limit be determined using
  carbon dioxide measurements corrected to an equivalent of 3 percent oxygen. The relationship between oxygen
  and carbon dioxide levels for the affected facility shall be established during the initial compliance test.

[FR Doc. 2014-29569 Filed 1-20-15; 8:45 am]
BILLING CODE 6560-50-P