8. Section 63.6595 is amended by revising paragraphs (a) and (b)(2)
to read as follows:

Sec.  63.6595  When do I have to comply with this subpart?

    (a) Affected Sources. (1) If you have an existing stationary RICE
with a site rating of more than 500 brake HP located at a major source
of HAP emissions, you must comply with the applicable emission
limitations and operating limitations no later than June 15, 2007.
    (2) If you start up your new or reconstructed stationary RICE with
a site rating of more than 500 brake HP located at a major source of
HAP emissions before August 16, 2004, you must comply with the
applicable emission limitations and operating limitations in this
subpart no later than August 16, 2004.
    (3) If you start up your new or reconstructed stationary RICE with
a site rating of more than 500 brake HP located at a major source of
HAP emissions after August 16, 2004, you must comply with the
applicable emission limitations and operating limitations in this
subpart upon startup of your affected source.

    (4) If you start up your new or reconstructed stationary RICE with
a site rating of less than or equal to 500 brake HP located at a major
source of HAP emissions before [DATE OF PUBLICATION OF FINAL RULE IN
THE Federal Register], you must comply with the applicable emission
limitations and operating limitations in this subpart no later than
[DATE OF PUBLICATION OF FINAL RULE IN THE Federal Register].
    (5) If you start up your new or reconstructed stationary RICE with
a site rating of less than or equal to 500 brake HP located at a major
source of HAP emissions after [DATE OF PUBLICATION OF FINAL RULE IN THE
Federal Register], you must comply with the applicable emission
limitations and operating limitations in this subpart upon startup of
your affected source.
    (6) If you start up your new or reconstructed stationary RICE
located at an area source of HAP emissions before [DATE OF PUBLICATION
OF FINAL RULE IN THE FEDERAL REGISTER], you must comply with the
applicable emission limitations and operating limitations in this
subpart no later than [DATE OF PUBLICATION OF FINAL RULE IN THE Federal
Register].
    (7) If you start up your new or reconstructed stationary RICE
located at an area source of HAP emissions after [DATE OF PUBLICATION
OF FINAL RULE IN THE FEDERAL REGISTER], you must comply with the
applicable emission limitations and operating limitations in this
subpart upon startup of your affected source.
    (b) * * *
    (2) Any stationary RICE for which construction or reconstruction is
commenced before your area source becomes a major source of HAP must be
in compliance with the provisions of this subpart that are applicable
to RICE located at major sources within 3 years after your area source
becomes a major source of HAP.
* * * * *
    9. Section 63.6600 is revised to read as follows:

Sec.  63.6600  What emission limitations and operating limitations must
I meet if I own or operate a stationary RICE with a site rating of more
than 500 brake HP located at a major source of HAP emissions?

    (a) If you own or operate an existing, new, or reconstructed spark
ignition 4SRB stationary RICE with a site rating of more than 500 brake
HP located at a major source of HAP emissions, you must comply with the
emission limitations in Table 1a to this subpart and the operating
limitations in Table 1b to this subpart which apply to you.
    (b) If you own or operate a new or reconstructed 2SLB or 4SLB
stationary RICE with a site rating of more than 500 brake HP located at
major source of HAP emissions or a new or reconstructed CI stationary
RICE with a site rating of more than 500 brake HP located at a major
source of HAP emissions, you must comply with the emission limitations
in Table 2a to this subpart and the operating limitations in Table 2b
to this subpart which apply to you.
    (c) If you own or operate any of the following RICE with a site
rating of more than 500 brake HP located at a major source of HAP
emissions, you do not need to comply with the emission limitations in
Tables 1a and 2a to this subpart or operating limitations in Tables 1b
and 2b to this subpart: an existing 2SLB stationary RICE, an existing
4SLB stationary RICE, or an existing CI stationary RICE; a stationary
RICE that combusts landfill gas or digester gas equivalent to 10
percent or more of the gross heat input on an annual basis; an
emergency stationary RICE; or a limited use stationary RICE.
    10. Section 63.6601 is added to read as follows:

Sec.  63.6601  What emission limitations must I meet if I own or
operate a stationary RICE with a site rating of equal to or less than
500 brake HP located at a major source of HAP emissions or a stationary
RICE located at an area source of HAP emissions?

    (a) If you own or operate a new or reconstructed stationary RICE
with a site rating of equal to or less than 500 brake HP located at a
major source of HAP emissions or a new or reconstructed stationary RICE
located at an area source of HAP emissions, you must comply with the
emission limitations in Table 3 to this subpart which apply to you.
    (b) If you own or operate an existing stationary RICE with a site
rating of equal to or less than 500 brake HP located at a major source
of HAP emissions or an existing stationary RICE located at an area
source, you do not need to comply with the emission limitations in
Table 3 to this subpart.
    11. Section 63.6610 is amended by revising the section heading,
adding introductory text, and revising paragraphs (a) through (c) to
read as follows:

Sec.  63.6610  By what date must I conduct the initial performance
tests or other initial compliance demonstrations if I own or operate a
stationary RICE with a site rating of more than 500 brake HP located at
a major source of HAP emissions?

    If you own or operate a stationary RICE with a site rating of more
than 500 brake HP located at a major source of HAP emissions you are
subject to the requirements of this section.
    (a) You must conduct the initial performance test or other initial
compliance demonstrations in Table 5 to this subpart that apply to you
within 180 days after the compliance date that is specified for your
stationary RICE in Sec.  63.6595 and according to the provisions in
Sec.  63.7(a)(2).
    (b) If you commenced construction or reconstruction between
December 19, 2002 and June 15, 2004 and own or operate stationary RICE
with a site rating of more than 500 brake HP located at a major source
of HAP emissions, you must demonstrate initial compliance with either
the proposed emission limitations or the promulgated emission
limitations no later than February 10, 2005 or no later than 180 days
after startup of the source, whichever is later, according to Sec.
63.7(a)(2)(ix).
    (c) If you commenced construction or reconstruction between
December 19, 2002 and June 15, 2004 and own or operate stationary RICE
with a site rating of more than 500 brake HP located at a major source
of HAP emissions, and you chose to comply with the proposed emission
limitations when demonstrating initial compliance, you must conduct a
second performance test to demonstrate compliance with the promulgated
emission limitations by December 13, 2007 or after startup of the
source, whichever is later, according to Sec.  63.7(a)(2)(ix).
* * * * *
    12. Section 63.6611 is added to read as follows:

Sec.  63.6611  By what date must I conduct the initial performance
tests or other initial compliance demonstrations if I own or operate a
stationary RICE with a site rating of less than or equal to 500 brake
HP located at a major source of HAP emissions or a stationary RICE
located at an area source of HAP emissions?

    (a) If you own or operate a new or reconstructed 4SLB stationary
RICE with a site rating of greater than or equal to 250 and less than
or equal to 500 brake HP located at a major source of HAP emissions,
you must conduct an initial performance test within 240 days after the
compliance date that is specified for your stationary RICE in Sec.
63.6595 and according to the

provisions specified in Table 5 to this subpart, as appropriate.
    (b) If you own or operate a new or reconstructed uncertified
stationary RICE with a site rating of less than or equal to 500 brake
HP located at a major source of HAP emissions or a new or reconstructed
uncertified stationary RICE located at an area source of HAP emissions
you must conduct an initial performance test within 240 days after the
compliance date that is specified for your stationary RICE in Sec.
63.6595 and according to the provisions specified in Table 5 to this
subpart, as appropriate.
    (c) If you own or operate a new or reconstructed certified
stationary RICE with a site rating of less than or equal to 500 brake
HP located at a major source of HAP emissions or a certified stationary
RICE located at an area source of HAP emissions you are not required to
conduct an initial performance test.
    13. Section 63.6615 is revised to read as follows:

Sec.  63.6615  When must I conduct subsequent performance tests?

    If you must comply with the emission limitations and operating
limitations, you must conduct subsequent performance tests as specified
in Table 4 to this subpart.
    14. Section 63.6620 is amended by revising paragraphs (a) and (b)
and adding paragraph (j) to read as follows:

Sec.  63.6620  What performance tests and other procedures must I use?

    (a) You must conduct each performance test in Tables 4 and 5 to
this subpart that applies to you.
    (b) Each performance test must be conducted according to the
requirements in Sec.  63.7(e)(1) and under the specific conditions that
this subpart specifies in Table 5. The test must be conducted at any
load condition within plus or minus 10 percent of 100 percent load.
* * * * *
    (j) To determine compliance with the non-methane hydrocarbons
(NMHC) mass per unit output emission limitation, you must use Equation
5 of this section:
[GRAPHIC] [TIFF OMITTED] TP12JN06.008

Where:

ER = Emission rate of NMHC in g/HP-hr.
Cd = NMHC concentration measured as propane in ppm.
1.832 x 10-3 = Conversion constant for ppm NMHC measured
as propane, to grams per standard cubic meter at 25 degrees Celsius.
Q = Stack gas volumetric flow rate, in standard cubic meters per
hour.
T = Time of test run, in hours.
HP-hr = Brake work of the engine, in HP-hr.

    15. Section 63.6625 is amended by revising the introductory text of
paragraph (a), revising paragraph (b), and adding paragraphs (d), (e),
and (f) to read as follows:

Sec.  63.6625  What are my monitoring, installation, operation, and
maintenance requirements?

    (a) If you elect to install a continuous emissions monitoring
system (CEMS) as specified in Table 6 of this subpart, you must
install, operate, and maintain a CEMS to monitor CO and either oxygen
or CO2 at both the inlet and the outlet of the control
device according to the requirements in paragraphs (a)(1) through (4)
of this section.
* * * * *
    (b) If you are required to install a continuous parameter
monitoring system (CPMS) as specified in Table 6 to this subpart, you
must install, operate, and maintain each CPMS according to the
requirements in Sec.  63.8.
* * * * *
    (d) If you are operating a new or reconstructed emergency
stationary RICE with a site rating of equal to or less than 500 brake
HP located at a major source of HAP emissions or a new or reconstructed
stationary RICE located at an area source of HAP emissions, you must
install a non-resettable hour meter prior to the startup of the engine.
    (e) If you are operating a new or reconstructed stationary RICE
with a site rating of equal to or less than 500 brake HP located at a
major source of HAP emissions or a new or reconstructed stationary RICE
located at an area source of HAP emissions, you must operate and
maintain the stationary RICE and control device according to the
manufacturer's written instructions or procedures developed by the
owner or operator that are approved by the engine manufacturer.
    (f) If you are operating a new or reconstructed certified
stationary RICE with a site rating of equal to or less than 500 brake
HP located at a major source of HAP emissions (except new or
reconstructed 4SLB stationary RICE with a site rating of equal to or
greater than 250 brake HP and less than or equal to 500 brake HP
located at a major source of HAP emissions) or a new or reconstructed
certified stationary RICE located at an area source, you may only
change those settings that are allowed by the manufacturer.
    16. Section 63.6630 is amended by revising paragraph (a) to read as
follows:

Sec.  63.6630  How do I demonstrate initial compliance with the
emission limitations and operating limitations?

    (a) You must demonstrate initial compliance with each emission and
operating limitation that applies to you according to Table 6 to this
subpart.
* * * * *
    17. Section 63.6640 is amended by revising paragraphs (a), (b), and
(e) and adding paragraph (f) to read as follows:

Sec.  63.6640  How do I demonstrate continuous compliance with the
emission limitations and operating limitations?

    (a) You must demonstrate continuous compliance with each emission
limitation and operating limitation in Tables 1a and 1b, Tables 2a and
2b, and Table 3 to this subpart that apply to you according to methods
specified in Table 7 to this subpart.
    (b) You must report each instance in which you did not meet each
emission limitation or operating limitation in Tables 1a and 1b, Tables
2a and 2b, and Table 3 to this subpart that apply to you. These
instances are deviations from the emission and operating limitations in
this subpart. These deviations must be reported according to the
requirements in Sec.  63.6650. If you change your catalyst, you must
reestablish the values of the operating parameters measured during the
initial performance test. When you reestablish the values of your
operating parameters, you must also conduct a performance test to
demonstrate that you are meeting the required emission limitation
applicable to your stationary RICE.
* * * * *
    (e) You must also report each instance in which you did not meet
the requirements in Table 9 to this subpart that apply to you. If you
own or operate an existing 2SLB stationary RICE, an existing 4SLB
stationary RICE, an existing 4SRB stationary RICE with a site rating
equal to or less than 500 brake HP located at a major source of

HAP emissions, an existing 4SRB stationary RICE located at an area
source of HAP emissions, an existing CI stationary RICE, an existing
emergency stationary RICE, an existing limited use emergency stationary
RICE, or an existing stationary RICE which fires landfill gas or
digester gas equivalent to 10 percent or more of the gross heat input
on an annual basis, you do not need to comply with the requirements in
Table 9 to this subpart. If you own or operate a new or reconstructed
stationary RICE that combusts landfill gas or digester gas equivalent
to 10 percent or more of the gross heat input on an annual basis, a new
or reconstructed emergency stationary RICE, or a new or reconstructed
limited use stationary RICE, you do not need to comply with the
requirements in Table 9 to this subpart, except for the initial
notification requirements.
    (f) If you own or operate a stationary emergency RICE with a site
rating of equal to or less than 500 brake HP located at a major source
of HAP emissions or a stationary emergency RICE located at an area
source of HAP emissions, you may operate your emergency stationary RICE
for the purpose of maintenance checks and readiness testing.
Maintenance checks and readiness testing of such units is limited to
100 hours per year. There is no time limit on the use of stationary
emergency RICE in emergency situations. The owner or operator may
petition the Administrator for approval of additional hours to be used
for maintenance checks and readiness testing, but a petition is not
required if the owner or operator maintains records that Federal,
State, or local standards require maintenance and testing or emergency
engines beyond 100 hours per year. For owners and operators or
emergency engines, any operation other than emergency operation and
maintenance and testing as permitted in this section, is prohibited.
    18. Section 63.6645 is amended by:
    a. Revising paragraphs (a), (b), and (c);
    b. Redesignating paragraphs (d) through (f) as paragraphs (h)
through (j);
    c. Adding paragraphs (d) through (g); and
    d. Revising newly redesignated paragraphs (h) and (j) to read as
follows:

Sec.  63.6645  What notifications must I submit and when?

    (a) If you own or operate a stationary RICE with a site rating of
more than 500 brake HP located at a major source of HAP emissions or a
new or reconstructed 4SLB stationary RICE with a site rating of greater
than or equal to 250 HP located at a major source of HAP emissions, you
must submit all of the notifications in Sec. Sec.  63.7(b) and (c),
63.8(e), (f)(4) and (f)(6), 63.9(b) through (e), and (g) and (h) that
apply to you by the dates specified.
    (b) As specified in Sec.  63.9(b)(2), if you start up your
stationary RICE with a site rating of more than 500 brake HP located at
a major source of HAP emissions before the effective date of this
subpart, you must submit an Initial Notification not later than
December 13, 2004.
    (c) If you start up your new or reconstructed stationary RICE with
a site rating of more than 500 brake HP located at a major source of
HAP emissions on or after August 16, 2004, you must submit an Initial
Notification not later than 120 days after you become subject to this
subpart.
    (d) As specified in Sec.  63.9(b)(2), if you start up your
stationary RICE with a site rating of equal to or less than 500 brake
HP located at a major source of HAP emissions before the effective date
of this subpart and you are required to submit an initial notification,
you must submit an Initial Notification not later than [180 DAYS AFTER
DATE THE FINAL RULE IS PUBLISHED IN THE Federal Register].
    (e) If you start up your new or reconstructed stationary RICE with
a site rating of equal to or less than 500 brake HP located at a major
source of HAP emissions on or after [60 DAYS AFTER DATE THE FINAL RULE
IS PUBLISHED IN THE Federal Register] and you are required to submit an
initial notification, you must submit an Initial Notification not later
than 120 days after you become subject to this subpart.
    (f) As specified in Sec.  63.9(b)(2), if you start up your
stationary RICE located at an area source of HAP emissions before the
effective date of this subpart and you are required to submit an
initial notification, you must submit an Initial Notification not later
than [180 DAYS AFTER DATE THE FINAL RULE IS PUBLISHED IN THE Federal
Register].
    (g) If you start up your new or reconstructed stationary RICE
located at an area source of HAP emissions on or after [60 DAYS AFTER
DATE THE FINAL RULE IS PUBLISHED IN THE Federal Register] and you are
required to submit an initial notification, you must submit an Initial
Notification not later than 120 days after you become subject to this
subpart.
    (h) If you are required to submit an Initial Notification but are
otherwise not affected by the requirements of this subpart, in
accordance withSec.  63.6590(b), your notification should include the
information in Sec.  63.9(b)(2)(i) through (v), and a statement that
your stationary RICE has no additional requirements and explain the
basis of the exclusion (for example, that it operates exclusively as an
emergency stationary RICE if it has a site rating of more than 500
brake HP located at a major source of HAP emissions).
* * * * *
    (j) If you are required to conduct a performance test or other
initial compliance demonstration as specified in Tables 5 and 6 to this
subpart, you must submit a Notification of Compliance Status according
to Sec.  63.9(h)(2)(ii).
    (1) For each initial compliance demonstration required in Table 6
to this subpart that does not include a performance test, you must
submit the Notification of Compliance Status before the close of
business on the 30th day following the completion of the initial
compliance demonstration.
    (2) For each initial compliance demonstration required in Table 6
to this subpart that includes a performance test conducted according to
the requirements in Table 5 to this subpart, you must submit the
Notification of Compliance Status, including the performance test
results, before the close of business on the 60th day following the
completion of the performance test according to Sec.  63.10(d)(2).
    19. Section 63.6650 is amended by:
    a. Revising paragraph (a);
    b. Revising paragraph (b) introductory text;
    c. Revising paragraph (f); and
    d. Revising paragraph (g) introductory text to read as follows:

Sec.  63.6650  What reports must I submit and when?

    (a) You must submit each report in Table 8 to this subpart that
applies to you.
    (b) Unless the Administrator has approved a different schedule for
submission of reports under Sec.  63.10(a), you must submit each report
by the date in Table 8 to this subpart and according to the
requirements in paragraphs (b)(1) through (5) of this section.
* * * * *
    (f) Each affected source that has obtained a title V operating
permit pursuant to 40 CFR part 70 or 71 must report all deviations as
defined in this subpart in the semiannual monitoring report required by
40 CFR 70.6 (a)(3)(iii)(A) or 40 CFR 71.6(a)(3)(iii)(A). If an affected
source submits a Compliance report pursuant to Table 8 to this subpart
along with, or as part of, the semiannual monitoring report required by
40 CFR 70.6(a)(3)(iii)(A) or 40 CFR 71.6(a)(3)(iii)(A), and the

Compliance report includes all required information concerning
deviations from any emission or operating limitation in this subpart,
submission of the Compliance report shall be deemed to satisfy any
obligation to report the same deviations in the semiannual monitoring
report. However, submission of a Compliance report shall not otherwise
affect any obligation the affected source may have to report deviations
from permit requirements to the permit authority.
    (g) If you are operating as a new or reconstructed stationary RICE
which fires landfill gas or digester gas equivalent to 10 percent or
more of the gross heat input on an annual basis, you must submit an
annual report according to Table 8 to this subpart by the date
specified unless the Administrator has approved a different schedule,
according to the information described in paragraphs (b)(1) through
(b)(5) of this section. You must report the data specified in (g)(1)
through (g)(3) of this section.
* * * * *
    20. Section 63.6655 is amended by revising paragraph (d) and adding
paragraphs (e) and (f) to read as follows:

Sec.  63.6655  What records must I keep?

* * * * *
    (d) You must keep the records required in Table 7 to this subpart
to show continuous compliance with each emission or operating
limitation that applies to you.
    (e) If you own or operate a stationary emergency RICE with a site
rating of equal to or less than 500 brake HP located at a major source
of HAP emissions or a stationary emergency RICE located at an area
source of HAP emissions you must keep records of the operation of the
engine that is recorded through the non-resettable hour meter. You must
keep records of the operation in emergency and non-emergency that are
recorded through the non-resettable hour meter. You must record the
time of operation of the engine and the reason the engine was in
operation during that time.
    (f) If you own or operate a stationary emergency RICE with a site
rating of equal to or less than 500 brake HP located at a major source
of HAP emissions or a stationary emergency RICE located at an area
source of HAP emissions, you must keep records documenting proper
engine maintenance.
    21. Section 63.6665 is revised to read as follows:

Sec.  63.6665  What parts of the General Provisions apply to me?

    Table 9 to this subpart shows which parts of the General Provisions
in Sec. Sec.  63.1 through 63.15 apply to you. If you own or operate an
existing 2SLB RICE, an existing 4SLB stationary RICE, an existing 4SRB
RICE with a site rating of equal to or less than 500 brake HP located
at a major source of HAP emissions, an existing 4SRB RICE located at an
area source of HAP emissions, an existing CI stationary RICE, an
existing stationary RICE that combusts landfill gas or digester gas
equivalent to 10 percent or more of the gross heat input on an annual
basis, an existing emergency stationary RICE, or an existing limited
use stationary RICE, you do not need to comply with any of the
requirements of the General Provisions. If you own or operate a new
stationary RICE that combusts landfill gas or digester gas equivalent
to 10 percent or more of the gross heat input on an annual basis, a new
emergency stationary RICE, or a new limited use stationary RICE, you do
not need to comply with the requirements in the General Provisions
except for the initial notification requirements.
    22. Section 63.6675 is amended by:
    a. Adding definitions of ``Certified stationary RICE,''
``Compression Ignition,'' ``Gasoline,'' ``Maximum engine power,''
``Model year,'' ``Non-methane hydrocarbons,'' ``Spark ignition,''
``Total hydrocarbons,'' and ``Useful life'' in alphabetical order;
    b. Removing the definitions for ``Compression ignition engine'' and
``Spark ignition engine;'' and
    c. Revising the definitions of ``Emergency stationary RICE'' and
``Natural gas;'' to read as follows:

Sec.  63.6675  What definitions apply to this subpart?

* * * * *
    Certified stationary RICE means an engine that belongs to an engine
family that has a certificate of conformity that complies with the
emission standards and requirements in this part, or of 40 CFR part 90
or 40 CFR part 1048, as appropriate.
    Compression ignition means relating to a type of stationary
internal combustion engine that is not a spark ignition engine.
* * * * *
    Emergency stationary RICE means any stationary RICE whose operation
is limited to emergency situations and required testing and
maintenance. Examples include stationary RICE used to produce power for
critical networks or equipment (including power supplied to portions of
a facility) when electric power from the local utility (or the normal
power source, if the facility runs on its own power production) is
interrupted, or stationary RICE used to pump water in the case of fire
or flood, etc. Stationary RICE used for peak shaving are not considered
emergency stationary RICE.
* * * * *
    Gasoline means any fuel sold in any State for use in motor vehicles
and motor vehicle engines, or nonroad or stationary engines, and
commonly or commercially known or sold as gasoline.
* * * * *
    Maximum engine power means maximum engine power as defined in 40
CFR 1039.801.
    Model Year means either: the calendar year in which the engine was
originally produced, or the annual new model production period of the
engine manufacturer if it is different than the calendar year. This
must include January 1 of the calendar year for which the model year is
named. It may not begin before January 2 of the previous calendar year,
and it must end by December 31 of the named calendar year. For an
engine that is converted to a stationary engine after being placed into
service as a nonroad or other non-stationary engine, model year means
the calendar year or new model production period in which the engine
was originally produced.
    Natural gas means a naturally occurring mixture of hydrocarbon and
non-hydrocarbon gases found in geologic formations beneath the Earth's
surface, of which the principal constituent is methane. Natural gas may
be field or pipeline quality.
    Non-methane hydrocarbons means the difference between the emitted
mass of total hydrocarbons and the emitted mass of methane.
* * * * *
    Spark ignition means relating to either: a gasoline-fueled engine;
or any other type of engine a spark plug (or other sparking device) and
with operating characteristics significantly similar to the theoretical
Otto combustion cycle. Spark ignition engines usually use a throttle to
regulate intake air flow to control power during normal operation.
Dual-fuel engines in which a liquid fuel (typically diesel fuel) is
used for CI and gaseous fuel (typically natural gas) is used as the
primary fuel at an annual average ratio of less than 2 parts diesel
fuel to 100 parts total fuel on an energy equivalent basis are spark
ignition engines.
* * * * *

    Total hydrocarbons means the combined mass of organic compounds
measured by the specified procedure for measuring total hydrocarbon,
expressed as a hydrocarbon with a hydrogen-to-carbon mass ratio of
1.85:1.
* * * * *
    Useful life means the period during which the engine is designed to
properly function in terms of reliability and fuel consumption, without
being remanufactured, specified as a number of hours of operation or
calendar years, whichever comes first. The values for useful life for
stationary CI ICE with a displacement of less than 10 liters per
cylinder are given in 40 CFR 1039.101(g). The values for useful life
for stationary CI ICE with a displacement of greater than or equal to
10 liters per cylinder and less than 30 liters per cylinder are given
in 40 CFR 94.9(a). The values for useful life for stationary SI ICE
with a maximum engine power less than or equal to 25 HP are given in 40
CFR 90.105. The values for useful life for stationary SI ICE with a
maximum engine power greater than 25 HP certified to 40 CFR part 1048
are given in 40 CFR 1048.101(g). The useful life for stationary SI ICE
with a maximum engine power greater than 25 HP certified under the
voluntary manufacturer certification program 40 CFR part 60 subpart
JJJJ is 8,000 hours or 10 years, whichever comes first.
    23. Table 1a to Subpart ZZZZ of Part 63 is revised to read as
follows:

Table 1a to Subpart ZZZZ of Part 63.--Emission Limitations for Existing,
   New, and Reconstructed Spark Ignition, 4SRB Stationary RICE >500 HP
               Located at a Major Source of HAP Emissions
    [As stated in Sec.   63.6600, you must comply with the following
emission limitations for existing, new and reconstructed 4SRB stationary
 RICE >500 HP located at a major source of HAP emissions at 100 percent
                     load plus or minus 10 percent:]
------------------------------------------------------------------------
                                           You must meet the following
             For each . . .                 emission limitations . . .
------------------------------------------------------------------------
1. 4SRB stationary RICE................  a. reduce formaldehyde
                                          emissions by 76 percent or
                                          more. If you commenced
                                          constructed or reconstruction
                                          between December 19, 2002, and
                                          June 15, 2004, you may reduce
                                          formaldehyde emissions by 75
                                          percent or more until June 15,
                                          2007;
                                         or
                                         b. limit the concentration of
                                          formaldehyde in the stationary
                                          RICE exhaust 350 ppbvd or less
                                          at 15 percent O2.
------------------------------------------------------------------------

    24. Table 1b to Subpart ZZZZ of Part 63 is revised to read as
follows:

     Table 1b to Subpart ZZZZ of Part 63.--Operating Limitations for
  Existing, New, and Reconstructed Spark Ignition, 4SRB Stationary RICE
           >500 HP Located at a Major Source of HAP Emissions
[As stated in Sec.  Sec.   63.6600, 63.6630 and 63.6640, you must comply
 with the following operating emission limitations for existing, new and
 reconstructed 4SRB stationary RICE >500 HP located at a major source of
                             HAP emissions:]
------------------------------------------------------------------------
                                           You must meet the following
             For each . . .                 operating limitation . . .
------------------------------------------------------------------------
1. 4SRB stationary RICE complying with   a. maintain your catalyst so
 the requirement to reduce formaldehyde   that the pressure drop across
 emissions by 76 percent or more (or by   the catalyst does not change
 75 percent or more, if applicable) and   by more than 2 inches of water
 using NSCR;                              at 100 percent load plus or
                                          minus 10 percent from the
                                          pressure drop across the
                                          catalyst measured during the
                                          initial performance test; and

                   or

4SRB stationary RICE complying with the  b. maintain the temperature of
 requirement to limit the concentration   your stationary RICE exhaust
 of formaldehyde in the stationary RICE   so that the catalyst inlet
 exhaust to 350 ppbvd or less at 15       temperature is greater than or
 percent O2 and using NSCR.               equal to 750 [deg]F and less
                                          than or equal to 1250 [deg]F.
2. 4SRB stationary RICE complying with   comply with any operating
 the requirement to reduce formaldehyde   limitations approved by the
 emissions by 76 percent or more (or by   Administrator.
 75 percent or more, if applicable) and
 not using NSCR;

                   or

4SRB stationary RICE complying with the
 requirement to limit the concentration
 of formaldehyde in the stationary RICE
 exhaust to 350 ppbvd or less at 15
 percent O2 and not using NSCR.
------------------------------------------------------------------------

    25. Table 2a to Subpart ZZZZ of Part 63 is revised to read as
follows:

 Table 2a to Subpart ZZZZ of Part 63.--Emission Limitations for New and
Reconstructed Lean Burn and Compression Ignition Stationary RICE >500 HP
               Located at a Major Source of HAP Emissions
    [As stated in Sec.   63.6600, you must comply with the following
  emission limitations for new and reconstructed lean burn and new and
 reconstructed compression ignition stationary RICE >500 HP located at a
   major source of HAP emissions at 100 percent load plus or minus 10
                                percent:]
------------------------------------------------------------------------
                                           You must meet the following
             For each . . .                 emission limitation . . .
------------------------------------------------------------------------
1. 2SLB stationary RICE................  a. reduce CO emissions by 58
                                          percent or more;
                                         or
                                         b. limit concentration of
                                          formaldehyde in the stationary
                                          RICE exhaust to 12 ppmvd or
                                          less at 15 percent O2. If you
                                          commenced construction or
                                          reconstruction between
                                          December 19, 2002, and June
                                          15, 2004, you may limit
                                          concentration of formaldehyde
                                          to 17 ppmvd or less at 15
                                          percent O2 until June 15,
                                          2007.
2. 4SLB stationary RICE................  a. reduce CO emissions by 93
                                          percent or more;
                                         or
                                         b. limit concentration of
                                          formaldehyde in the stationary
                                          RICE exhaust to 14 ppmvd or
                                          less at 15 percent O2.
3. CI stationary RICE..................  a. reduce CO emissions by 70
                                          percent or more;
                                         or
                                         b. limit concentration of
                                          formaldehyde in the stationary
                                          RICE exhaust to 580 ppbvd or
                                          less at 15 percent O2.
------------------------------------------------------------------------

    26. Table 2b to Subpart ZZZZ of Part 63 is revised to read as
follows:

 Table 2b to Subpart ZZZZ of Part 63.--Operating Limitations for New and
Reconstructed Lean Burn and Compression Ignition Stationary RICE >500 HP
               Located at a Major Source of HAP Emissions
   [As stated in Sec.  Sec.   63.6600, 63.6630, and 63.6640, you must
       comply with the following operating limitations for new and
 reconstructed lean burn and new and reconstructed compression ignition
   stationary RICE >500 HP located at a major source of HAP emissions:
------------------------------------------------------------------------
                                           You must meet the following
             For each . . .                 operating limitation . . .
------------------------------------------------------------------------
1. 2SLB and 4SLB stationary RICE and CI  a. maintain your catalyst so
 stationary RICE complying with the       that the pressure drop across
 requirement to reduce CO emissions and   the catalyst does not change
 using an oxidation catalyst; or 2SLB     by more than 2 inches of water
 and 4SLB stationary RICE and CI          at 100 percent load plus or
 stationary RICE complying with the       minus 10 percent from the
 requirement to limit the concentration   pressure drop across the
 of formaldehyde in the stationary RICE   catalyst that was measured
 exhaust and using an oxidation           during the initial performance
 catalyst.                                test; and
                                         b. maintain the temperature of
                                          your stationary RICE exhaust
                                          so that the catalyst inlet
                                          temperature is greater than or
                                          equal to 450 [deg]F and less
                                          than or equal to 1350 [deg]F.
2. 2SLB and 4SLB stationary RICE and CI  comply with any operating
 stationary RICE complying with the       limitations approved by the
 requirement to reduce CO emissions and   Administrator.
 not using an oxidation catalyst; or
 2SLB and 4SLB stationary RICE and CI
 stationary RICE complying with the
 requirement to limit the concentration
 of formaldehyde in the stationary RICE
 exhaust and not using an oxidation
 catalyst.
------------------------------------------------------------------------

    27. Tables 3 through 8 to Subpart ZZZZ of Part 63 are amended by:
    a. Redesignating Tables 3 through 8 as Tables 4 through 9;
    b. Adding Table 3; and
    c. Revising the newly redesignated Tables 4 through 9 to read as
follows:

  Table 3 to Subpart ZZZZ of Part 63.--Emission Limitations for New and Reconstructed Stationary RICE < =500 HP
 Located at a Major Source of HAP Emissions or New or Reconstructed Stationary RICE Located at an Area Source of
                                                  HAP Emissions
----------------------------------------------------------------------------------------------------------------
                                                                                You must meet the
           For each. . .             With a Maximum Engine   And with a Manufacture Date     following emission
                                          Power. . .                  of a. . .               limitation. . .
----------------------------------------------------------------------------------------------------------------
1. New or reconstructed SI          < =25 HP...............  January 1, 2008..............  Comply with the NMHC
 stationary RICE.                                                                           emission standards
                                                                                for new SI engines
                                                                                as specified in 40
                                                                                CFR part 60 subpart
                                                                                JJJJ Sec.
                                                                                60.4233(a).
2. New or reconstructed SI          25< HP< 500.............  January 1, 2008..............  Comply with the NMHC
 stationary RICE using gasoline or  HP >=500..............  July 1, 2007.................   emission standards
 rich burn engines using LPG.                                                               for new SI engines
                                                                                as specified in 40
                                                                                CFR part 60 subpart
                                                                                JJJJ Sec.
                                                                                60.4233(b) or (c),
                                                                                as applicable.
3. New or reconstructed non-
 emergency SI natural gas
 stationary RICE, except engines
 addressed in row 5 of this table.

                and                 25< HP< 500 a...........  January 1, 2008..............  Limit the
                                                                                concentration of
                                                                                NMHC in the
                                                                                stationary RICE
                                                                                exhaust to 1.0 and g/
                                                                                HP-hr.
New or reconstructed non-emergency  ......................  January 1, 2011..............  Limit the
 SI lean burn LPG stationary RICE,                                                          concentration of
 except engines addressed in row 5                                                          NMHC in the
 of this table.                                                                             stationary RICE
                                                                                exhaust to 0.7 g/HP-
                                                                                hr.
4. New or reconstructed non-        HP>=500...............  July 1, 2007.................  Limit the
 emergency SI natural gas                                                                   concentration of
 Stationary RICE.                                                                           NMHC in the
                                                                                stationary RICE
                                                                                exhaust to 1.0 g/HP-
                                                                                hr.
                and

New or reconstructed non-emergency  ......................  July 1, 2010.................  Limit the
 SI lean burn LPG stationary RICE.                                                          concentration of
                                                                                NMHC in the
                                                                                stationary RICE
                                                                                exhaust to 0.7 g/HP-
                                                                                hr.
5. New or reconstructed non-        250 < =HP < =500........  See applicability dates in     a. reduce CO
 emergency 4SLB stationary RICE                              Sec.   63.6595.                emissions by 93
 located at a major source of HAP                                                           percent or more;
 emissions (except landfill and                                                             or
 digester gas)).                                                                           b. limit the
                                                                                concentration of
                                                                                formaldehyde in the
                                                                                stationary RICE
                                                                                exhaust to 14 ppmvd
                                                                                or less at 15
                                                                                percent O2.
6. New or reconstructed 2007 model  Any...................  2007+ model year.............  Comply with the PM
 year and later CI stationary RICE.                                                         and NMHC emission
                                                                                standards for new CI
                                                                                engines as specified
                                                                                in 40 CFR part 60
                                                                                subpart IIII Sec.
                                                                                Sec.   60.4204 and
                                                                                60.4205, as
                                                                                applicable.
7. New or reconstructed landfill/   HP< 500................  January 1, 2008..............  Limit the
 digester gas stationary RICE.                                                              concentration of
                                                                                NMHC in the
                                                                                stationary RICE
                                                                                exhaust to 1.0 g/HP-
                                                                                hr.
                                    HP >=500..............  July 1, 2007.................  Limit the
                                                                                concentration of
                                                                                NMHC in the
                                                                                stationary RICE
                                                                                exhaust to 1.0 g/HP-
                                                                                hr.
8. New or reconstructed emergency   Any...................  January 1, 2009..............  Limit the
 SI stationary RICE.                                                                        concentration of
                                                                                NMHC in the
                                                                                stationary RICE
                                                                                exhaust to 1.0 g/HP-
                                                                                hr.
----------------------------------------------------------------------------------------------------------------
a Stationary SI natural gas and lean burn LPG engines between 25 and 50 HP may comply with the requirements of
  row 2 of this table, instead of row 3 of this table, as applicable.

    Table 4 to Subpart ZZZZ of Part 63.--Subsequent Performance Tests
 As stated in Sec.  Sec.   63.6615 and 63.6620, you must comply with the
           following subsequent performance test requirements:
------------------------------------------------------------------------
                               Complying with the
       For each . . .         requirement to . . .     You must . . .
------------------------------------------------------------------------
1. 2SLB, 4SLB, and CI         Reduce CO emissions   Conduct subsequent
 stationary RICE.              and not using a       performance tests
                               CEMS.                 semiannually.\a\
2. 4SRB stationary RICE with  Reduce formaldehyde   Conduct subsequent
 a brake HP >=5,000 HP.        emissions.            performance tests
                                                     semiannually.\a\
3. Stationary RICE (all       Limit the             Conduct subsequent
 stationary RICE               concentration of      performance tests
 subcategories and all brake   formaldehyde in the   semiannually.\a\
 HP ratings.                   stationary RICE
                               exhaust.
4. New and reconstructed non- Limit the             Conduct subsequent
 emergency stationary RICE     concentration of      performance tests
 with a brake HP >500 HP       NMHC in the           every 3 years or
 located at an area source     stationary RICE       8,760 hours of
 of HAP emissions.             exhaust.              operation,
                                                     whichever comes
                                                     first.\b\
------------------------------------------------------------------------
\a\ After you have demonstrated compliance for two consecutive tests,
  you may reduce the frequency of subsequent performance tests to
  annually. If the results of any subsequent annual performance test
  indicate the stationary RICE is not in compliance with the CO or
  formaldehyde emission limitation, or you deviate from any of your
  operating limitations, you must resume semiannual performance tests.
\b\ New and reconstructed uncertified stationary RICE with a brake HP
  < =500 are not required to conduct subsequent performance testing
  unless the stationary RICE is rebuilt or undergoes major repair or
  maintenance. Certified engines are not required to conduct any
  performance testing.

                     Table 5 to Subpart ZZZZ of Part 63.--Requirements for Performance Tests
      [As stated in Sec.  Sec.   63.6610, 63.6611, 63.6620, and 63.6640, you must comply with the following
                            requirements for performance tests for stationary RICE:]
----------------------------------------------------------------------------------------------------------------
                                 Complying with                                               According to the
        For each . . .           the requirement   You must . . .        Using . . .            following to
                                      . . .                                                  requirements . . .
----------------------------------------------------------------------------------------------------------------
1. 2SLB, 4SLB, and CI           a. reduce CO      i. measure the    (1) portable CO and    (a) using ASTM D6522-
 stationary RICE.                emissions.        O2 at the inlet   O2 analyzer.           00 (2005) \a\
                                                   and outlet of                            (incorporated by
                                                   the control                              reference see Sec.
                                                   device; and                              63.14). Measurements
                                                                                to determine O2 must
                                                                                be made at the same
                                                                                time as the
                                                                                measurements for CO
                                                                                concentration.
                                ii. measure the   (1) portable CO   (a) using ASTM D6522-
                                 CO at the inlet   and O2 analyzer.  00 (2005) \a\
                                 and the outlet                      (incorporation by
                                 of the control                      reference, see Sec.
                                 device.                              63.14). The CO
                                                                     concentration must
                                                                     be at 15 percent O2,
                                                                     dry basis.

2. 4SRB stationary RICE.......  a. reduce         i. select the     (1) Method 1 or 1A of  (a) sampling sites
                                 formaldehyde      sampling port     40 CFR part 60,        must be located at
                                 emissions.        location and      appendix A Sec.        the inlet and outlet
                                                   the number of     63.7(d)(1)(i).         of the control
                                                   traverse                                 device.
                                                   points; and.
                                ................  ii. measure O2    (1) Method 3 or 3A or  (a) measurements to
                                                   at the inlet of   3B of 40 CFR part      determine O2
                                                   the control       60, appendix A, or     concentration must
                                                   device; and       ASTM Method D6522-     be made at the same
                                                                     00(2005).              time as the
                                                                                measurements for
                                                                                formaldehyde
                                                                                concentration.
                                ................  iii. measure      (1) Method 4 of 40     (a) measurements to
                                                   moisture          CFR part 60,           determine moisture
                                                   content at the    appendix A, or Test    content must be made
                                                   inlet and         Method 320 of 40 CFR   at the same time and
                                                   outlet of the     part 63, appendix A    location as the
                                                   control device;   or ASTM D 6348-03.     measurements for
                                                   and                                      formaldehyde
                                                                                concentration.
                                ................  iv. measure       (1) Method 320 or 323  (a) formaldehyde
                                                   formaldehyde at   of 40 CFR part 63,     concentration must
                                                   the inlet and     appendix A; or ASTM    at 15 percent O2,
                                                   the outlet of     D6348-03, \b\          dry basis. Results
                                                   the control       provided in ASTM       of this test consist
                                                   device.           D6348-03 Annex A5      of the average of
                                                                     (Analyte Spiking       the three 1-hour or
                                                                     Technique), the        longer runs.
                                                                     percent R must be
                                                                     greater than or
                                                                     equal to 70 and less
                                                                     than or equal to 130.
3. stationary RICE............  a. limit the      i. select the     (1) Method 1 or 1A of  (a) if using a
                                 concentration     sampling port     40 CFR part 60,        control device, the
                                 of formaldehyde   location and      appendix A Sec.        sampling site must
                                 in the            the number of     63.7(d)(1)(i).         be located at the
                                 stationary RICE   traverse                                 outlet of the
                                 exhaust.          points; and                              control device.
                                ................  ii. determine     (1) Method 3 or 3A or  (a) measurements to
                                                   the O2            3B of 40 CFR part      determine O2
                                                   concentration     60, appendix A, or     concentration must
                                                   of the            ASTM Method D6522-00   be made at the same
                                                   stationary RICE   (2005).                time and location as
                                                   exhaust at the                           measurements for
                                                   sampling port                            formaldehyde
                                                   location; and                            concentration.
                                ................  iii. measure      (1) Method 4 of 40     (a) measurements to
                                                   moisture          CFR part 60,           determine moisture
                                                   content of the    appendix A, or Test    content must be made
                                                   stationary RICE   Method 320 of 40 CFR   at the same time and
                                                   exhaust at the    part 63, appendix A,   location as the
                                                   sampling port     or ASTM D 6348-03.     measurements for
                                                   location; and                            formaldehyde
                                                                                concentration.
                                ................  iv. measure       (1) Method 320 or 323  (a) Formaldehyde
                                                   formaldehyde at   of 40 CFR part 63,     concentration must
                                                   the exhaust of    appendix A; or ASTM    be at 15 percent O2,
                                                   the stationary    D6348-03 \b\           dry basis. Results
                                                   RICE.             provided in ASTM       of this test consist
                                                                     D6348-03 Annex A5      of the average of
                                                                     (Analyte Spiking       the three 1-hour or
                                                                     Technique), the        longer runs.
                                                                     percent R must be
                                                                     greater than or
                                                                     equal to 70 and less
                                                                     than or equal to 130.
4. New or reconstructed         limit the         i. select the     (1) Method 1 or 1A of  (a) if using a
 uncertified stationary RICE,    concentration     sampling port     40 CFR part 60,        control device, the
 except stationary RICE with a   of NMHC in the    location and      appendix A.            sampling site must
 brake HP >500 located at a      stationary RICE   the number of                            be located the
 major source of HAP emissions   exhaust.          traverse                                 outlet of the
 and new and reconstructed                         points;                                  control device.
 4SLB stationary RICE
 250< =HP< =500 located at a
 major source of HAP emissions.

                                ................  ii. If,           (2) Method 4 of 40     (b) measurements to
                                                   necessary,        CFR part 60,           determine moisture
                                                   measure           appendix A.            must be made at the
                                                   moisture                                 same time as the
                                                   content of the                           measurement for NMHC
                                                   stationary                               concentration.
                                                   internal
                                                   combustion
                                                   engine exhaust
                                                   at the sampling
                                                   port location;
                                                   and
                                ................  iii. measure      (3) Method 25 or       (c) Results of this
                                                   NMHC at the       Methods 25A and 18     test consist of the
                                                   exhaust of the    of 40 CFR part 60,     average of the three
                                                   stationary        appendix A.            1-hour or longer
                                                   internal                                 runs.
                                                   combustion
                                                   engine.
----------------------------------------------------------------------------------------------------------------
\a\ You may also use Methods 3A and 10 as options to ASTM-D6522-00 (2005). You may obtain a copy of ASTM-D6522-
  00 (2005) from at least one of the following addresses: American Society for Testing and Materials, 100 Barr
  Harbor Drive, West Conshohocken, PA 19428--2959, or University Microfilms International, 300 North Zeeb Road,
  Ann Arbor, MI 48106.
\b\ You may obtain a copy of ASTM-D6348-03 from at least one of the following addresses: American Society for
  Testing and Materials, 100 Barr Harbor Drive, West Conshohocken, PA 19428-2959, or University Microfilms
  International, 300 North Zeeb Road, Ann Arbor, MI 48106.

  Table 6 to Subpart ZZZZ of Part 63.--Initial Compliance with Emission
                  Limitations and Operating Limitations
[As stated in Sec.  Sec.   63.6625 and 63.6630 you must initially comply
     with the emission and operating limitations as required by the
                               following:]
------------------------------------------------------------------------
                                                          You have
        For each. . .          Complying with the   demonstrated initial
                               requirement to. . .   compliance if. . .
------------------------------------------------------------------------
1. 2SLB, 4SLB, and CI         a. reduce CO          i. the average
 stationary RICE.              emissions and using   reduction of
                               oxidation catalyst,   emissions of CO
                               and using a CPMS.     determined from the
                                                     initial performance
                                                     test achieves the
                                                     required CO percent
                                                     reduction; and
                                                    ii. you have
                                                     installed a CPMS to
                                                     continuously
                                                     monitor catalyst
                                                     inlet temperature
                                                     according to the
                                                     requirements in
                                                     Sec.   63.6625(b);
                                                     and
                                                    iii. you have
                                                     recorded the
                                                     catalyst pressure
                                                     drop and catalyst
                                                     inlet temperature
                                                     during the initial
                                                     performance test.
2. 2SLB, 4SLB, and CI         a. reduce CO          i. the average
 stationary RICE.              emissions and not     reduction of
                               using oxidation       emissions of CO
                               catalyst.             determined from the
                                                     initial performance
                                                     test achieves the
                                                     required CO percent
                                                     reduction; and
                                                    ii. you have
                                                     installed a CPMS to
                                                     continuously
                                                     monitor operating
                                                     parameters approved
                                                     by the
                                                     Administrator (if
                                                     any) according to
                                                     the requirements in
                                                     Sec.   63.6625(b);
                                                     and
                                                    iii. you have
                                                     recorded the
                                                     approved operating
                                                     parameters (if any)
                                                     during the initial
                                                     performance test.
3. 2SLB, 4SLB, and CI         a. reduce CO          i. you have
 stationary Rice.              emissions, and        installed a CEMS to
                               using a CEMS.         continuously
                                                     monitor CO and
                                                     either O2 or CO2 at
                                                     both the inlet and
                                                     outlet of the
                                                     oxidation catalyst
                                                     according to the
                                                     requirements in
                                                     Sec.   63.6625(a);
                                                     and
                                                    ii. you have
                                                     conducted a
                                                     performance
                                                     evaluation of your
                                                     CEMS using PS 3 and
                                                     4A of 40 CFR part
                                                     60, appendix B; and
                                                    iii. the average
                                                     reduction of CO
                                                     calculated using
                                                     Sec.   63.6620
                                                     equals or exceeds
                                                     the required
                                                     percent reduction.
                                                     The initial test
                                                     comprises the first
                                                     4-hour period after
                                                     successful
                                                     validation of the
                                                     CEMS. Compliance is
                                                     based on the
                                                     average percent
                                                     reduction achieved
                                                     during the 4-hour
                                                     period.

4. 4SRB stationary RICE.....  a. reduce             i. the average
                               formaldehyde          reduction of
                               emissions and using   emissions of
                               NSCR.                 formaldehyde
                                                     determined from the
                                                     initial performance
                                                     test is equal to or
                                                     greater than the
                                                     required
                                                     formaldehyde
                                                     percent reduction;
                                                     and
                                                    ii. you have
                                                     installed a CPMS to
                                                     continuously
                                                     monitor catalyst
                                                     inlet temperature
                                                     according to the
                                                     requirements in
                                                     Sec.   63.6625(b);
                                                     and
                                                    iii. you have
                                                     recorded the
                                                     catalyst pressure
                                                     drop and catalyst
                                                     inlet temperature
                                                     during the initial
                                                     performance test.
5. 4SRB stationary RICE.....  a. reduce             i. the average
                               formaldehyde          reduction of
                               emissions and not     emissions of
                               using NSCR.           formaldehyde
                                                     determined from the
                                                     initial performance
                                                     test is equal to or
                                                     greater than the
                                                     required
                                                     formaldehyde
                                                     percent reduction;
                                                     and
                                                    ii. you have
                                                     installed a CPMS to
                                                     continuously
                                                     monitor operating
                                                     parameters approved
                                                     by the
                                                     Administrator (if
                                                     any) according to
                                                     the requirements in
                                                     Sec.   63.6625(b);
                                                     and
                                                    iii. you have
                                                     recorded the
                                                     approved operating
                                                     parameters (if any)
                                                     during the initial
                                                     performance test.
6. Stationary RICE..........  a. limit the          i. the average
                               concentration of      formaldehyde
                               formaldehyde in the   concentration
                               stationary RICE       corrected to 15
                               exhaust and using     percent O2, dry
                               oxidation catalyst    basis, from the
                               or NSCR.              three test runs is
                                                     less than or equal
                                                     to the formaldehyde
                                                     emission
                                                     limitation; and
                                                    ii. you have
                                                     installed a CPMS to
                                                     continuously
                                                     monitor catalyst
                                                     inlet temperature
                                                     according to the
                                                     requirements in
                                                     Sec.   63.6625(b);
                                                     and
                                                    iii. you have
                                                     recorded the
                                                     catalyst pressure
                                                     drop and catalyst
                                                     inlet temperature
                                                     during the initial
                                                     performance test.
7. Stationary RICE..........  a. limit the          i. the average
                               concentration of      formaldehyde
                               formaldehyde in the   concentration,
                               stationary RICE       corrected to 15
                               exhaust and not       percent O2, dry
                               using oxidation       basis, from the
                               catalyst or NSCR.     three test runs is
                                                     less than or equal
                                                     to the formaldehyde
                                                     emission
                                                     limitation; and
                                                    ii. you have
                                                     installed a CPMS to
                                                     continuously
                                                     monitor operating
                                                     parameters approved
                                                     by the
                                                     Administrator (if
                                                     any) according to
                                                     the requirements in
                                                     Sec.   63.6625(b);
                                                     and
                                                    iii. you have
                                                     recorded the
                                                     approved operating
                                                     parameters (if any)
                                                     during the initial
                                                     performance test.
8. New and reconstructed SI   meet emission         you have purchased
 stationary RICE with a        standards in Sec.     an engine certified
 maximum engine power < =25     63.6605.              to the emission
 HP.                                                 standards specified
                                                     in 40 CFR part 60,
                                                     subpart JJJJ Sec.
                                                     60.4233(a).
9. New and reconstructed SI   meet emission         you have purchased
 stationary RICE with a        standards in Sec.     an engine certified
 maximum engine power >25 HP   63.6605.              to the emission
 that use gasoline or that                           standards specified
 are rich burn and use LPG.                          in 40 CFR part 60,
                                                     subpart JJJJ, Sec.
                                                     Sec.   60.4233(b)
                                                     or (c), as
                                                     applicable.
10. New and reconstructed SI  meet emission         i. you have
 stationary RICE with a        standards in Sec.     purchased an engine
 maximum engine power >25 HP   63.6605.              certified to the
 that use fuels other than                           emission standards
 gasoline and are not rich                           specified in 40 CFR
 burn engines that use LPG.                          part 60, subpart
                                                     JJJJ; or
                                                    ii. the average NMHC
                                                     concentration, from
                                                     the three test runs
                                                     is less than or
                                                     equal to 0.7g/HP-
                                                     hr.
11. New and reconstructed CI  meet emission         you have purchased
 stationary RICE.              standards in Sec.     an engine certified
                               63.6605.              to the emission
                                                     standards specified
                                                     in 40 CFR part 60,
                                                     subpart IIII, Sec.
                                                     Sec.   60.4204 and
                                                     60.4205, as
                                                     applicable.
------------------------------------------------------------------------

.

Table 7 to Subpart ZZZZ of Part 63.--Continuous Compliance With Emission
                  Limitations and Operating Limitations
   [As stated in Sec.   63.6640, you must continuously comply with the
   emissions and operating limitations as required by the following:]
------------------------------------------------------------------------
                                                    You must demonstrate
                               Complying with the        continuous
       For each . . .         requirement to . . .   compliance by . . .

------------------------------------------------------------------------
1. 2SLB, 4SLB, and CI         a. reduce CO          i. conducting
 stationary RICE.              emissions and using   semiannual
                               an oxidation          performance tests
                               catalyst, and using   for CO to
                               a CPM.                demonstrate that
                                                     the required CO
                                                     percent reduction
                                                     is achieved \a\;
                                                     and
                                                    ii. collecting the
                                                     catalyst inlet
                                                     temperature data
                                                     according to Sec.
                                                     63.6625(b); and
                                                    iii. reducing these
                                                     data to 4-hour
                                                     rolling averages;
                                                     and
                                                    iv. maintaining the
                                                     4-hour rolling
                                                     averages within the
                                                     operating
                                                     limitations for the
                                                     catalyst inlet
                                                     temperature; and
                                                    v. measuring the
                                                     pressure drop
                                                     across the catalyst
                                                     once per month and
                                                     demonstrating that
                                                     the pressure drop
                                                     across the catalyst
                                                     is within the
                                                     operating
                                                     limitation
                                                     established during
                                                     the performance
                                                     test.
2. 2SLB, 4SLB, and CI         a. reduce CO          i. conducting
 stationary RICE.              emissions and not     semiannual
                               using an oxidation    performance tests
                               catalyst, and using   for CO to
                               a CPMS.               demonstrate that
                                                     the required CO
                                                     percent reduction
                                                     is achieved \a\;
                                                     and
                                                    ii. collecting the
                                                     approved operating
                                                     parameter (if any)
                                                     data according to
                                                     Sec.   63.6625(b);
                                                     and
                                                    iii. reducing these
                                                     data to 4-hour
                                                     rolling averages;
                                                     and
                                                    iv. maintaining the
                                                     4-hour rolling
                                                     averages within the
                                                     operating
                                                     limitations for the
                                                     operating
                                                     parameters
                                                     established during
                                                     the performance
                                                     test.
3. 2SLB, 4SLB, and CI         a. reduce CO          i. collecting the
 stationary RICE.              emissions and using   monitoring data
                               a CEMS.               according Sec.
                                                     63.6625(a),
                                                     reducing the
                                                     measurements to 1-
                                                     hour averages,
                                                     calculating the
                                                     percent reduction
                                                     of CO emissions
                                                     according to Sec.
                                                     63.6620; and
                                                    ii. demonstrating
                                                     that the catalyst
                                                     achieves the
                                                     required percent
                                                     reduction of CO
                                                     emissions over the
                                                     4-hour averaging
                                                     period; and
                                                    iii. conducting an
                                                     annual RATA of your
                                                     CEMS using PS 3 and
                                                     4A of 40 CFR part
                                                     60, appendix B, as
                                                     well as daily and
                                                     periodic data
                                                     quality checks in
                                                     accordance with 40
                                                     CFR part 60,
                                                     appendix F,
                                                     procedure 1.
4. 4SRB stationary RICE.....  a. reduce             i. collecting the
                               formaldehyde          catalyst inlet
                               emissions and using   temperature data
                               NSCR.                 according to Sec.
                                                     63.6625(b); and
                                                    ii. reducing these
                                                     data to 4-hour
                                                     rolling averages;
                                                     and
                                                    iii. maintaining the
                                                     4-hour rolling
                                                     averages within the
                                                     operating
                                                     limitations for the
                                                     catalyst inlet
                                                     temperature; and
                                                    iv. measuring the
                                                     pressure drop
                                                     across the catalyst
                                                     once per month and
                                                     demonstrating that
                                                     the pressure drop
                                                     across the catalyst
                                                     is within the
                                                     operating
                                                     limitation
                                                     established during
                                                     the performance
                                                     test.
5. 4SRB stationary RICE.....  a. reduce             i. collecting the
                               formaldehyde          approved operating
                               emissionis and not    parameter (if any)
                               using NSCR.           data according to
                                                     Sec.   63.6625(b);
                                                     and
                                                    ii. reducing these
                                                     data to 4-hour
                                                     rolling averages;
                                                     and
                                                    iii. maintaining the
                                                     4-hour rolling
                                                     averages within the
                                                     operating
                                                     limitations for the
                                                     operating
                                                     parameters
                                                     established during
                                                     the performance
                                                     test.
6. 4SRB stationary RICE with  reduce formaldehyde   conducting
 a brake HP >=5,000.           emissions.            semiannual
                                                     performance tests
                                                     for formaldehyde to
                                                     demonstrate that
                                                     the required
                                                     formaldehyde
                                                     percent reduction
                                                     is achieved \a\.

7. stationary RICE..........  limit the             i. conducting
                               concentration of      semiannual
                               formaldehyde in the   performance tests
                               stationary RICE       for formaldehyde to
                               exhaust and using     demonstrate that
                               oxidation catalyst    your emissions
                               or NSCR.              remain at or below
                                                     the formaldehyde
                                                     concentration the
                                                     stationary limit
                                                     \a\; and
                                                    ii. collecting the
                                                     catalyst inlet
                                                     temperature data
                                                     according to Sec.
                                                     63.6625(b); and
                                                    iii. reducing these
                                                     data to 4-hour
                                                     rolling averages;
                                                     and
                                                    iv. maintaining the
                                                     4-hour rolling
                                                     averages within the
                                                     operating
                                                     limitations for the
                                                     catalyst inlet
                                                     temperature; and
                                                    v. measuring the
                                                     pressure drop
                                                     across the catalyst
                                                     once per month and
                                                     demonstrating that
                                                     the pressure drop
                                                     across the catalyst
                                                     is within the
                                                     operating
                                                     limitation
                                                     established during
                                                     the performance
                                                     test.
8. stationary RICE..........  limit the             i. conducting
                               concentration of      semiannual
                               formaldehyde in the   performance tests
                               stationary RICE       for formaldehyde to
                               exhaust and not       demonstrate that
                               using oxidation       your emissions
                               catalyst or NSCR.     remain at or below
                                                     the formaldehyde
                                                     concentration limit
                                                     \a\; and
                                                    ii. collecting the
                                                     approved operating
                                                     parameter (if any)
                                                     data according to
                                                     Sec.   63.6625(b);
                                                     and
                                                    ii. reducing these
                                                     data to 4-hour
                                                     rolling averages;
                                                     and
                                                    iii. maintaining the
                                                     4-hour rolling
                                                     averages within the
                                                     operating
                                                     limitations for the
                                                     operating
                                                     parameters
                                                     established during
                                                     the performance
                                                     test.
9. New and reconstructed      limit the             i. conducting
 uncertified stationary RICE   concentration of      performance tests
 with a brake HP >500          NMHC in the           every 3 years or
 located at an area source     stationary RICE       8,760 hours of
 of HAP emissions.             exhaust.              operation,
                                                     whichever comes
                                                     first for NMHC to
                                                     demonstrate that
                                                     the required NMHC
                                                     limit is achieved;
                                                     and
                                                    ii. operating and
                                                     maintaining your
                                                     stationary RICE and
                                                     control device
                                                     according to the
                                                     manufacturer's
                                                     written
                                                     instructions.
10. New and reconstructed     meet the emission     operating and
 certified stationary RICE,    standards specified   maintaining your
 except stationary RICE with   in 40 CFR part 60     stationary RICE and
 a brake HP >500 located at    subpart JJJJ Sec.     control device
 a major source of HAP         60.4233, as           according to the
 emissions.                    applicable.           manufacturer's
                                                     written
                                                     instructions.
------------------------------------------------------------------------
\a\ After you have demonstrated compliance for two consecutive tests,
  you may reduce the frequency of subsequent performance tests to
  annually. If the results of any subsequent annual performance test
  indicate the stationary RICE is not in compliance with the CO or
  formaldehyde emission limitation, or you deviate from any of your
  operating limitations, you must resume semiannual performance tests.

                         Table 8 to Subpart ZZZZ of Part 63.--Requirements for Reports.
           [As stated in Sec.   63.6650, you must comply with the following requirements for reports:]
----------------------------------------------------------------------------------------------------------------
                                                                The report must contain    You must submit the
            For each . . .               You must submit a(n)            . . .                 report . . .
----------------------------------------------------------------------------------------------------------------
1. Stationary RICE with a brake HP     a. compliance report...  i. if there are no       (a) semiannually
 >500 located at a major source of                               deviations from any      according to the
 HAP emissions.                                                  emission limitations     requirements in Sec.
                                                                 or operating             63.6650(b).
                                                                 limitations that apply
                                                                 to you, a statement
                                                                 that there were no
                                                                 deviations from the
                                                                 emission limitations
                                                                 or operating
                                                                 limitations during the
                                                                 reporting period. If
                                                                 there were no periods
                                                                 during which the CMS,
                                                                 including CEMS and
                                                                 CPMS, was out-of-
                                                                 control, as specified
                                                                 in Sec.   63.8(c)(7),
                                                                 a statement that there
                                                                 were not periods
                                                                 during which the CMS
                                                                 was out-of-control
                                                                 during the reporting
                                                                 period; or.

                 and

New or reconstructed 4SLB stationary   .......................  ii. if you had a         (a) semiannually
 RICE with a 250< =HP< =500 located at                             deviation from any       according to the
 a major source of HAP emissions.                                emission limitation or   requirements in Sec.
                                                                 operating limitation     63.6650(b).
                                                                 during the reporting
                                                                 period, the
                                                                 information in Sec.
                                                                 63.6660(d). If there
                                                                 were periods during
                                                                 which the CMS,
                                                                 including CEMS and
                                                                 CPMS, was out-of-
                                                                 control, as specified
                                                                 in Sec.   63.8(c)(7),
                                                                 the information in
                                                                 Sec.   63.6650(e); or
                                                                iii. if you had a        (a) semiannually
                                                                 startup, shutdown or     according to the
                                                                 malfunction during the   requirements in Sec.
                                                                 reporting period, the    63.6650(b).
                                                                 information in Sec.
                                                                 63.10(d)(5)(i).
2. Stationary RICE with a brake HP     b. an immediate          i. actions taken for     (a) by fax or telephone
 >500 located at a major source of      startup, shutdown, and   the event; and.          within 2 working days
 HAP emissions.                         malfunction report if                             after starting actions
                                        actions addressing the                            inconsistent with the
                                        startup, shutdown, or                             plan.
                                        malfunction were
                                        inconsistent with your
                                        startup, shutdown, or
                                        malfunction plan
                                        during the reporting
                                        period.
                 and

New or reconstructed 4SLB stationary                            ii. the information in   (a) by letter within 7
 RICE with a 250< =HP< =500 located at                             Sec.                     working days after the
 a major source of HAP emissions.                                63.10(d)(5)(ii).         end of the event
                                                                                unless you have made
                                                                                alternative
                                                                                arrangements with the
                                                                                permitting
                                                                                authorities. (Sec.
                                                                                63.10(d)(5)(ii)) plan.
3. New or reconstructed stationary     c. Report..............  i. the fuel flow rate    (a) annually, according
 RICE which fires landfill or                                    of each fuel and the     to the requirements in
 digester gas equivalent to 10                                   heating values that      Sec.   63.6650.
 percent or more of the gross heat                               were used in your
 input on an annual basis.                                       calculations, and you
                                                                 must demonstrate that
                                                                 the percentage of heat
                                                                 input provided by
                                                                 landfill gas or
                                                                 digester gas, is
                                                                 equivalent to 10
                                                                 percent or more of the
                                                                 gross heat input on an
                                                                 annual basis; and.
                                                                ii. the operating        (a) see item
                                                                 limits provided in       3(c)(i)(a).
                                                                 your federally
                                                                 enforceable permit,
                                                                 and any deviations
                                                                 from these limits; and
                                                                iii. any problems or     (a) see item
                                                                 errors suspected with    3(c)(i)(a).
                                                                 the meters.
----------------------------------------------------------------------------------------------------------------

            Table 9 to Subpart ZZZZ of Part 63.--Applicability of General Provisions to Subpart ZZZZ
        [As stated in Sec.   63.6665, you must comply with the following applicable general provisions.]
----------------------------------------------------------------------------------------------------------------
     General provisions citation         Subject of citation       Applies to subpart          Explanation
----------------------------------------------------------------------------------------------------------------
Sec.   63.1..........................  General applicability    Yes....................
                                        of the General
                                        Provisions.
Sec.   63.2..........................  Definitions............  Yes....................  Additional terms
                                                                                defined in Sec.
                                                                                63.6675.
Sec.   63.3..........................  Units and abbreviations  Yes....................
Sec.   63.4..........................  Prohibited activities    Yes....................
                                        and circumvention.
Sec.   63.5..........................  Construction and         Yes....................
                                        reconstruction.
Sec.   63.6(a).......................  Applicability..........  Yes....................
Sec.   63.6(b)(1)-(4)................  Compliance dates for     Yes....................
                                        new and reconstructed
                                        sources.
Sec.   63.6(b)(5)....................  Notification...........  Yes....................
Sec.   63.6(b)(6)....................  [Reserved].............
Sec.   63.6(b)(7)....................  Compliance dates for     Yes....................
                                        new and reconstructed
                                        area sources that
                                        become major sources.

Sec.   63.6(c)(1)-(2)................  Compliance dates for     Yes....................
                                        existing sources.
Sec.   63.6(c)(3)-(4)................  [Reserved].............
Sec.   63.6(c)(5)....................  Compliance dates for     Yes....................
                                        existing area sources
                                        that become major
                                        sources.
Sec.   63.6(d).......................  [Reserved].............
Sec.   63.6(e)(1)....................  Operation and            Yes....................
                                        maintenance.
Sec.   63.6(e)(2)....................  [Reserved].............
Sec.   63.6(e)(3)....................  Startup, shutdown, and   Yes....................
                                        malfunction plan.
Sec.   63.6(f)(1)....................  Applicability of         Yes....................
                                        standards except
                                        during startup
                                        shutdown malfunction
                                        (SSM).
Sec.   63.6(f)(2)....................  Methods for determining  Yes....................
                                        compliance.
Sec.   63.6(f)(3)....................  Finding of compliance..  Yes....................
Sec.   63.6(g)(1)-(3)................  Use of alternate         Yes....................
                                        standard.
Sec.   63.6(h).......................  Opacity and visible      No.....................  Subpart ZZZZ does not
                                        emission standards.                               contain opacity or
                                                                                visible emission
                                                                                standards.
Sec.   63.6(i).......................  Compliance extension     Yes....................
                                        procedures and
                                        criteria.
Sec.   63.6(j).......................  Presidential compliance  Yes....................
                                        exemption.
Sec.   63.7(a)(1)-(2)................  Performance test dates.  Yes....................  Subpart ZZZZ contains
                                                                                performance test dates
                                                                                at Sec.  Sec.
                                                                                63.6610 and 63.6611.
Sec.   63.7(a)(3)....................  CAA section 114          Yes....................
                                        authority.
Sec.   63.7(b)(1)....................  Notification of          Yes....................
                                        performance test.
Sec.   63.7(b)(2)....................  Notification of          Yes....................
                                        rescheduling.
Sec.   63.7(c).......................  Quality assurance/test   Yes....................
                                        plan.
Sec.   63.7(d).......................  Testing facilities.....  Yes....................
Sec.   63.7(e)(1)....................  Conditions for           Yes....................
                                        conducting performance
                                        tests.
Sec.   63.7(e)(2)....................  Conduct of performance   Yes....................  Subpart ZZZZ specifies
                                        tests and reduction of                            test methods at Sec.
                                        data.                                             63.6620.
Sec.   63.7(e)(3)....................  Test run duration......  Yes....................
Sec.   63.7(e)(4)....................  Administrator may        Yes....................
                                        require other testing
                                        under section 114 of
                                        the CAA.
Sec.   63.7(f).......................  Alternative test method  Yes....................
                                        provisions.
Sec.   63.7(g).......................  Performance test data    Yes....................
                                        analysis,
                                        recordkeeping, and
                                        reporting.
Sec.   63.7(h).......................  Waiver of tests........  Yes....................
Sec.   63.8(a)(1)....................  Applicability of         Yes....................  Subpart ZZZZ contains
                                        monitoring                                        specific for
                                        requirements.                                     monitoring at
                                                                                requirements Sec.
                                                                                63.6625.
Sec.   63.8(a)(2)....................  Performance              Yes....................
                                        specifications.
Sec.   63.8(a)(3)....................  [Reserved].............
Sec.   63.8(a)(4)....................  Monitoring for control   No.....................
                                        devices.
Sec.   63.8(b)(1)....................  Monitoring.............  Yes....................
Sec.   63.8(b)(2)-(3)................  Multiple effluents and   Yes....................
                                        multiple monitoring
                                        systems.
Sec.   63.8(c)(1)....................  Monitoring system        Yes....................
                                        operation and
                                        maintenance.
Sec.   63.8(c)(1)(i).................  Routine and predictable  Yes....................
                                        SSM.
Sec.   63.8(c)(1)(ii)................  SSM not in Startup       Yes....................  Plan
                                        Shutdown Malfunction.
Sec.   63.8(c)(1)(iii)...............  Compliance with          Yes....................
                                        operation and
                                        maintenance
                                        requirements.
Sec.   63.8(c)(2)-(3)................  Monitoring system        Yes....................
                                        installation.
Sec.   63.8(c)(4)....................  Continuous monitoring    Yes....................  Except that subpart
                                        system (CMS)                                      ZZZZ does not require
                                        requirements.                                     Continuous Opacity
                                                                                Monitoring System
                                                                                (COMS).
Sec.   63.8(c)(5)....................  COMS minimum procedures  No.....................  Subpart ZZZZ does not
                                                                                require COMS.
Sec.   63.8(c)(6)-(8)................  CMS requirements.......  Yes....................  Except that subpart
                                                                                ZZZZ does not require
                                                                                COMS.
Sec.   63.8(d).......................  CMS quality control....  Yes....................

Sec.   63.8(e).......................  CMS performance          Yes....................  Except for
                                        evaluation.                                       63.8(e)(5)(ii), which
                                                                                applies to COMS.
Sec.   63.8(f)(1)-(5)................  Alternative monitoring   Yes....................
                                        method.
Sec.   63.8(f)(6)....................  Alternative to relative  Yes....................
                                        accuracy test.
Sec.   63.8(g).......................  Data reduction.........  Yes....................  Except that provisions
                                                                                for COMS are not
                                                                                applicable. Averaging
                                                                                periods for
                                                                                demonstrating
                                                                                compliance are
                                                                                specified at ''63.6635
                                                                                and 63.6640.
Sec.   63.9(a).......................  Applicability and State  Yes....................
                                        delegation of
                                        notification
                                        requirements.
Sec.   63.9(b)(1)-(5)................  Initial notifications..  Yes....................  Except that Sec.
                                                                                63.9(b)(3) is
                                                                                reserved.
Sec.   63.9(c).......................  Request for compliance   Yes....................
                                        extension.
Sec.   63.9(d).......................  Notification of special  Yes....................
                                        compliance
                                        requirements for new
                                        sources.
Sec.   63.9(e).......................  Notification of          Yes....................
                                        performance test.
Sec.   63.9(f).......................  Notification of visible  No.....................  Subpart ZZZZ does not
                                        emission (VE)/opacity                             contain opacity or VE
                                        test.                                             standards.
Sec.   63.9(g)(1)....................  Notification of          Yes....................
                                        performance evaluation.
Sec.   63.9(g)(2)....................  Notification of use of   No.....................  Subpart ZZZZ does not
                                        COMS data.                                        contain opacity or VE
                                                                                standards.
Sec.   63.9(g)(3)....................  Notification that        Yes....................  If alternative is in
                                        criterion for                                     use.
                                        alternative to RATA is
                                        exceeded.
Sec.   63.9(h)(1)-(6)................  Notification of........  Yes....................  Except that
                                                                                notifications for
                                                                                compliance status
                                                                                sources using a CEMS
                                                                                are due 30 days after
                                                                                completion of
                                                                                performance
                                                                                evaluations.Sec.
                                                                                63.9(h)(4) is
                                                                                reserved.
Sec.   63.9(i).......................  Adjustment of submittal  Yes....................
                                        deadlines.
Sec.   63.9(j).......................  Change in previous       Yes....................
                                        information.
Sec.   63.10(a)......................  Administrative           Yes....................
                                        provisions for record
                                        keeping/reporting.
Sec.   63.10(b)(1)...................  Record retention.......  Yes....................
Sec.   63.10(b)(2)(i)-(v) SSM........  Records related to.....  Yes....................
Sec.   63.10(b)(2)(vi)-(xi)..........  Records................  Yes....................
Sec.   63.10(b)(2)(xii)..............  Record when under        Yes....................
                                        waiver.
Sec.   63.10(b)(2)(xiii).............  Records when using       Yes....................  For CO standard if
                                        alternative to RATA.                              using RATA
                                                                                alternative.
Sec.   63.10(b)(2)(xiv)..............  Records of supporting    Yes....................
                                        documentation.
Sec.   63.10(b)(3)...................  Records of               Yes....................
                                        applicability
                                        determination.
Sec.   63.10(c)......................  Additional records for   Yes....................  Except that Sec.
                                        sources using CEMS.                               63.10(c)(2)-(4) and
                                                                                (9) are reserved.
Sec.   63.10(d)(1)...................  General reporting        Yes....................
                                        requirements.
Sec.   63.10(d)(2)...................  Report of performance    Yes....................
                                        test results.
Sec.   63.10(d)(3)...................  Reporting opacity or VE  No.....................  Subpart ZZZZ does not
                                        observations.                                     contain opacity or VE
                                                                                standards.
Sec.   63.10(d)(4)...................  Progress reports.......  Yes....................
Sec.   63.10(d)(5)...................  Startup, shutdown, and   Yes....................
                                        malfunction reports.
Sec.   63.10(e)(1) and (2)(i)........  Additional CMS reports.  Yes....................
Sec.   63.10(e)(2)(ii)...............  COMS-related report....  No.....................  Subpart ZZZZ does not
                                                                                require COMS.
Sec.   63.10(e)(3)...................  Excess emission and      Yes....................  Except that Sec.
                                        parameter exceedances                             63.10(e)(3)(i)(C) is
                                        reports.                                          reserved.