[Federal Register Volume 75, Number 245 (Wednesday, December 22, 2010)]
[Proposed Rules]
[Pages 80397-80409]
[FR Doc No: 2010-32157]

-----------------------------------------------------------------------

DEPARTMENT OF ENERGY

Federal Energy Regulatory Commission

18 CFR Part 40

[Docket No. RM09-9-000]

Version One Regional Reliability Standards for Facilities Design,
Connections, and Maintenance; Protection and Control; and Voltage and
Reactive

December 17, 2010.
AGENCY: Federal Energy Regulatory Commission, DOE.

ACTION: Notice of proposed rulemaking.

-----------------------------------------------------------------------

SUMMARY: Under section 215 of the Federal Power Act, the Commission
proposes to approve four revised regional Reliability Standards
developed by the Western Electricity Coordinating Council and approved
by the North American Electric Reliability Corporation, which the
Commission has certified as the Electric Reliability Organization
responsible for developing and enforcing mandatory Reliability
Standards. These regional Reliability Standards have been designated by
WECC as FAC-501-WECC-1--Transmission Maintenance, PRC-004-WECC-1--
Protection System and Remedial Action Scheme Misoperation, VAR-002-
WECC-1--Automatic Voltage Regulators, and VAR-501-WECC-1--Power System
Stabilizer. Proposed FAC-501-WECC-1 addresses transmission maintenance
for specified transmission paths in the Western Interconnection.
Proposed PRC-004-WECC-1 addresses the analysis of misoperations that
occur on transmission and generation protection systems and remedial
action schemes in the Western Interconnection. Proposed VAR-002-WECC-1
is meant to ensure that automatic voltage regulators remain in service
on synchronous generators and condensers in the Western
Interconnection. Proposed VAR-501-WECC-1 is meant to ensure that power
system stabilizers remain in service on synchronous generators in the
Western Interconnection. In addition, under section 215(d)(5) of the
Federal Power Act, the Commission proposes to direct the Western
Electricity Coordinating Council, working through its standards
development process, to develop modifications to these to regional
Reliability Standards to address specific issues, as discussed below.

DATES: Comments are due February 22, 2011.

ADDRESSES: You may submit comments, identified by docket number and in
accordance with the requirements posted on the Commission's Web site,
http://www.ferc.gov. Comments may be submitted by any of the following
methods:
     Agency Web Site: Documents created electronically using
word processing software should be filed in native applications or
print-to-PDF format, and not in a scanned format, at http://www.ferc.gov/docs-filing/efiling.asp.
     Mail/Hand Delivery: Commenters unable to file comments
electronically must mail or hand-deliver an original copy of their
comments to: Federal Energy Regulatory Commission, Secretary of the
Commission, 888 First Street, NE., Washington, DC 20426. These
requirements can be found on the Commission's Web site, see, e.g., the
``Quick Reference Guide for Paper Submissions,'' available at http://www.ferc.gov/docs-filing/efiling.asp or via phone from FERC Online
support at<PHONE_NUMBER> or toll-free at 1-866-208-3676.

FOR FURTHER INFORMATION CONTACT:
A. Cory Lankford (Legal Information) Office of the General Counsel,
Federal Energy Regulatory Commission, 888 First Street, NE.,
Washington, DC 20426,<PHONE_NUMBER>.
Nick Henery (Technical Information), Office of Electric Reliability,
Federal Energy Regulatory Commission, 888 First Street, NE.,
Washington, DC 20426,<PHONE_NUMBER>.
Danny Johnson (Technical Information), Office of Electric Reliability,
Federal Energy Regulatory Commission, 888 First Street, NE.,
Washington, DC 20426,<PHONE_NUMBER>.
Scott Sells (Technical Information), Office of Electric Reliability,
Federal Energy Regulatory Commission, 888 First Street, NE.,
Washington, DC 20426,<PHONE_NUMBER>.

SUPPLEMENTARY INFORMATION:

Table of Contents

                                                              Paragraph
                                                                 Nos.

I. Background..............................................            3
    A. Mandatory Reliability Standards.....................            3
    B. Western Electricity Coordinating Council............            6
II. Proposed Regional Reliability Standards................            8
III. Discussion............................................           10
    A. FAC-501-WECC-1--Transmission Maintenance............           11
    B. PRC-004-WECC-1--Protection System and Remedial                 25
     Action Scheme Misoperation............................
    C. VAR-002-WECC-1--Automatic Voltage Regulators........           42
    D. VAR-501-WECC-1--Power System Stabilizer.............           65
IV. Information Collection Statement.......................           88
V. Environmental Analysis..................................           92
VI. Regulatory Flexibility Act Certification...............           93
VII. Comment Procedures....................................           94
VIII. Document Availability................................           98

    1. Under section 215 of the Federal Power Act (FPA),\1\ the
Commission proposes to approve four revised regional Reliability
Standards developed by the Western Electricity Coordinating Council
(WECC) and approved by the North American Electric Reliability
Corporation (NERC), which the Commission has certified as the Electric
Reliability Organization (ERO) responsible for developing and enforcing
mandatory Reliability Standards.\2\ These regional Reliability
Standards have been designated by WECC as FAC-501-WECC-1--Transmission
Maintenance, PRC-004-WECC-1--Protection System and Remedial Action
Scheme Misoperation, VAR-002-WECC-1--Automatic Voltage Regulators, and
VAR-501-WECC-1--Power System Stabilizer. Proposed FAC-501-WECC-1
addresses transmission maintenance for specified transmission paths in
the Western

Interconnection. Proposed PRC-004-WECC-1 addresses the analysis of
misoperations that occur on transmission and generation protection
systems and remedial action schemes in the Western Interconnection.
Proposed VAR-002-WECC-1 is meant to ensure that automatic voltage
regulators remain in service on synchronous generators and condensers
in the Western Interconnection. Proposed VAR-501-WECC-1 is meant to
ensure that power system stabilizers remain in service on synchronous
generators in the Western Interconnection. Under section 215(d)(5) of
the Federal Power Act, the Commission proposes to direct WECC, through
its standard development process, to develop modifications to these
regional Reliability Standards to address specific issues, as discussed
below.
---------------------------------------------------------------------------

    \1\ 16 U.S.C. 824o (2006).
    \2\ North American Electric Reliability Corp., 116 FERC ]
61,062, order on reh'g & compliance, 117 FERC ] 61,126 (2006), aff'd
sub nom. Alcoa, Inc. v. FERC, 564 F.3d 1342 (D.C. Cir. 2009).
---------------------------------------------------------------------------

    2. Related, the Commission also seeks comment on whether it should
direct the ERO to develop modifications to the NERC Reliability
Standards addressing the use of automatic voltage regulators and power
system stabilizers. The Commission's concerns regarding the NERC
Reliability Standard are introduced here as they correspond with
certain elements of the WECC standards that are the subject of the
immediate proceeding. However, any proposal to direct the development
of modifications to the NERC Reliability Standards would be addressed
in a separate proceeding.

I. Background

A. Mandatory Reliability Standards

    3. Section 215 of the FPA requires a Commission-certified ERO to
develop mandatory and enforceable Reliability Standards, which are
subject to Commission review and approval. Once approved, the
Reliability Standards may be enforced by the ERO, subject to Commission
oversight, or by the Commission independently.\3\
---------------------------------------------------------------------------

    \3\ 16 U.S.C. 824o(e)(3).
---------------------------------------------------------------------------

    4. Reliability Standards that the ERO proposes to the Commission
may include Reliability Standards that are proposed to the ERO by a
Regional Entity to be effective in that region.\4\ A Regional Entity is
an entity that has been approved by the Commission to enforce
Reliability Standards under delegated authority from the ERO.\5\ When
the ERO reviews a regional Reliability Standard that would be
applicable on an interconnection-wide basis and that has been proposed
by a Regional Entity organized on an interconnection-wide basis, the
ERO must rebuttably presume that the regional Reliability Standard is
just, reasonable, not unduly discriminatory or preferential, and in the
public interest.\6\ In turn, the Commission must give ``due weight'' to
the technical expertise of the ERO and of a Regional Entity organized
on an interconnection-wide basis.\7\
---------------------------------------------------------------------------

    \4\ 16 U.S.C. 824o(e)(4).
    \5\ 16 U.S.C. 824o(a)(7) and (e)(4).
    \6\ 18 CFR 39.5 (2010).
    \7\ 16 U.S.C. 824o(d)(2).
---------------------------------------------------------------------------

    5. In Order No. 672, the Commission urged uniformity of Reliability
Standards, but recognized a potential need for regional differences.\8\
Accordingly, the Commission stated that:
---------------------------------------------------------------------------

    \8\ Rules Concerning Certification of the Electric Reliability
Organization; Procedures for the Establishment, Approval, and
Enforcement of Electric Reliability Standards, Order No. 672, 71 FR
8662 (Feb. 17, 2006), FERC Stats. & Regs. ] 31,204, at P 290, order
on reh'g, Order No. 672-A, 71 FR 19814 (Apr. 18, 2006), FERC Stats.
& Regs. ] 31,212 (2006).

    As a general matter, we will accept the following two types of
regional differences, provided they are otherwise just, reasonable,
not unduly discriminatory or preferential and in the public
interest, as required under the statute: (1) A regional difference
that is more stringent than the continent-wide Reliability Standard,
including a regional difference that addresses matters that the
continent-wide Reliability Standard does not; and (2) a regional
Reliability Standard that is necessitated by a physical difference
in the Bulk-Power System.\9\
---------------------------------------------------------------------------

    \9\ Id. P 291.
---------------------------------------------------------------------------

B. Western Electricity Coordinating Council

    6. On April 19, 2007, the Commission accepted delegation agreements
between NERC and each of eight Regional Entities.\10\ In its order, the
Commission accepted WECC as a Regional Entity organized on an
Interconnection-wide basis. As a Regional Entity, WECC oversees
transmission system reliability in the Western Interconnection. The
WECC region encompasses nearly 1.8 million square miles, including 14
western U.S. states, the Canadian provinces of Alberta and British
Columbia, and the northern portion of Baja California in Mexico.
---------------------------------------------------------------------------

    \10\ North American Electric Reliability Corp., 119 FERC ]
61,060, at P 432 (2007).
---------------------------------------------------------------------------

    7. In June 2007, the Commission approved eight regional Reliability
Standards for WECC including the currently-effective WECC PRC-STD-001-
1, PRC-STD-003-1, PRC-STD-005-1, VAR-STD-002a-1, and VAR-STD-002b-
1.\11\ The Commission directed WECC to develop certain modifications to
WECC PRC-STD-001-1, PRC-STD-003-1, PRC-STD-005-1, VAR-STD-002a-1, and
VAR-STD-002b-1, as identified by NERC in its filing letter for the
current standards.\12\ For example, the Commission determined that: (1)
Regional definitions should conform to definitions set forth in the
NERC Glossary of Terms Used in Reliability Standards (NERC Glossary),
unless a specific deviation has been justified; and (2) documents that
are referenced in the Reliability Standard should be attached to the
Reliability Standard. The Commission also found that it is important
that regional Reliability Standards and NERC Reliability Standards
achieve a reasonable level of consistency in their structure so that
there is a common understanding of the elements.
---------------------------------------------------------------------------

    \11\ North American Electric Reliability Corp., 119 FERC ]
61,260 (2007).
    \12\ Id.
---------------------------------------------------------------------------

II. Proposed Regional Reliability Standards

    8. On March 25, 2009, NERC submitted a petition (NERC Petition) to
the Commission seeking approval of four WECC regional Reliability
Standards.\13\ The four proposed WECC regional Reliability Standards
are designated as FAC-501-WECC-1, PRC-004-WECC-1, VAR-002-WECC-1, and
VAR-501-WECC-1.\14\ In its petition, NERC explains that the four
proposed regional Reliability Standards are meant to replace certain
currently approved regional Reliability Standards:
---------------------------------------------------------------------------

    \13\ See 18 CFR 39.5(a) (requiring the ERO to submit regional
Reliability Standards on behalf of a Regional Entity).
    \14\ The proposed regional Reliability Standards are not
attached to the NOPR. They are, however, available on the
Commission's eLibrary document retrieval system in Docket No. RM09-
9-000 and are posted on the ERO's Web site, available at http://www.nerc.com.
---------------------------------------------------------------------------

     FAC-501-WECC-1 is intended to replace the current approved
PRC-STD-005-1;
     PRC-004-WECC-1 is intended to replace WECC PRC-STD-001-1
and PRC-STD-003-1;
     VAR-002-WECC-1 is intended to replace WECC VAR-STD-002a-1;
and
     VAR-501-WECC-1 is intended to replace WECC VAR-STD-002b-1.
    NERC states that the NERC board of trustees approved the proposed
regional Reliability Standards on October 29, 2008, on the condition
that WECC address certain shortcomings raised during the comment
periods in the next revision of the Reliability Standards.
    9. NERC requests an effective date for FAC-501-WECC-1, VAR-002-
WECC-1, and VAR-501-WECC-1 of the first day of the first quarter after
Commission approval. For PRC-004-WECC-1, NERC requests an effective
date of the first day of the second quarter after approval by the
Commission.

III. Discussion

    10. As discussed below, the Commission proposes to approve FAC-501-
WECC-1, PRC-004-WECC-1, VAR-002-WECC-1, and VAR-501-WECC-1 as just,
reasonable, not unduly discriminatory or preferential, and in the
public interest. In addition, under section 215(d)(5) of the FPA and
section 39.5(f) of our regulations, the Commission proposes to direct
WECC to develop certain modifications to further clarify the
requirements of the proposed WECC regional Reliability Standards.

A. FAC-501-WECC-1--Transmission Maintenance

    11. NERC PRC-005-1 applies to all transmission and generator owners
as well as distribution providers that own a transmission protection
system. The Reliability Standard is meant to ensure that all
transmission and generation protection systems affecting the
reliability of the Bulk-Power System are maintained and tested.
    12. On June 8, 2007, the Commission approved a WECC regional
Reliability Standard that corresponds to the NERC Reliability Standard
PRC-005-1.\15\ WECC PRC-STD-005-1 applies to transmission owners and
operators identified in an attached table titled ``Major WECC Transfer
Paths in the Bulk Electric System'' (WECC Transfer Path Table) and to
owners of remedial action schemes identified in the ``Major WECC
Remedial Action Schemes'' table (WECC Remedial Action Schemes Table).
WECC PRC-STD-005-1 requires each transmission owner and operator of the
specified transmission paths to perform maintenance and inspection on
those paths as described by its transmission maintenance and inspection
plan. The regional Reliability Standard identifies specific contents
that each applicable transmission owner and transmission operator must
include in its transmission maintenance and inspection plan. For
example, a plan must include the scheduled interval for time-based
maintenance, describe maintenance and inspection methods, provide
relevant checklists or forms, and provide criteria for assessing the
condition of a facility. Each applicable entity must retain all
pertinent maintenance and inspection records for at least five years.
Further each applicable entity must annually certify to WECC staff that
it has developed, documented, and implemented a transmission
maintenance and inspection plan.
---------------------------------------------------------------------------

    \15\ North American Electric Reliability Corp., 119 FERC ]
61,260 at P 95.
---------------------------------------------------------------------------

WECC and NERC Proposal
    13. NERC states that proposed FAC-501-WECC-1 is intended to replace
approved WECC PRC-STD-005-1. The proposed regional Reliability Standard
would apply to transmission owners that maintain transmission paths
listed in the WECC Transfer Path Table, which is no longer an
attachment to the Reliability Standard but is maintained on the WECC
Web site. Proposed FAC-501-WECC-1 contains three main provisions.
Requirement R1 provides that each transmission owner must have a
transmission, maintenance, and inspection plan, and each transmission
owner must annually review and update as required their transmission
maintenance and inspection plan. Requirement R2 states that each
transmission owner must include specified maintenance categories \16\
when developing their transmission maintenance and inspection plan.
Requirement 3 states that each transmission owner must implement and
follow their transmission maintenance and inspection plan.
---------------------------------------------------------------------------

    \16\ The maintenance categories to be included in the
transmission maintenance and inspection plan are included in
Attachment 1 of FAC-501-WECC-1--``Transmission Line and Station
Maintenance Details.''
---------------------------------------------------------------------------

    14. NERC recommends approval of FAC-501-WECC-1, stating that the
proposed regional Reliability Standard addresses matters that the NERC
Reliability Standard does not. Specifically, according to NERC, FAC-
501-WECC-1 requires, for specified transmission paths, a highly
detailed maintenance and inspection plan for all transmission and
substation equipment components, beyond the relay and communication
system maintenance and testing required by the corresponding NERC
Reliability Standard.\17\
---------------------------------------------------------------------------

    \17\ NERC Petition at 11, 14.
---------------------------------------------------------------------------

NOPR Proposal
    15. The Commission proposes to approve FAC-501-WECC-1 as just,
reasonable, not unduly discriminatory or preferential, and in the
public interest. As explained by NERC, proposed FAC-501-WECC-1 appears
to be more stringent, by virtue of its requirement for a highly
detailed maintenance and inspection plan, compared to the corresponding
NERC Reliability Standard.
    16. Further, in approving the currently-effective WECC PRC-STD-005-
1, the Commission directed WECC to make certain modifications to the
regional Reliability Standard. To address these directives, the
proposed regional Reliability Standard no longer references any WECC
Forms, and text regarding the Compliance Monitoring Period has been
removed. The proposed regional Reliability Standard no longer refers to
a regional definition of Disturbance, which conflicted with the
definition of Disturbance in the NERC Glossary. Since the term is not
included in any of the proposed regional Reliability Standards, the
Commission proposes to direct the ERO to remove this regional
definition from the NERC Glossary of terms upon Commission approval of
FAC-501-WECC-1. The proposed regional Reliability Standard also removes
the Sanctions Table and includes Violation Risk Factors, Violation
Severity Levels, Measures, and Time Horizons, as directed by the
Commission. These revisions appear generally consistent with the
Commission's directives, and signify meaningful improvement.
Accordingly, we propose to approve FAC-501-WECC-1. We also propose to
approve NERC's petition to retire currently-effective WECC PRC-STD-005-
1.
    17. While we propose to approve FAC-501-WECC-1, we have several
concerns regarding the requirements of the proposed regional
Reliability Standard that were not adequately addressed in the NERC
petition. Below, we discuss our concerns and, in the absence of a
satisfactory explanation from WECC, NERC and other commenters, under
section 215(d)(5) of the FPA and section 39.5(f) of our regulations, we
propose to direct that the Regional Entity develop modifications to the
regional Reliability Standard, as discussed below.
WECC Transfer Path Table
    18. First, we have a concern regarding the applicability of the
proposed regional Reliability Standard. As mentioned above, WECC PRC-
STD-005-1 is applicable to transmission owners or operators that
maintain transmission paths listed in the WECC Transfer Path Table,
which is attached to the regional Reliability Standard. The attachment
identifies 40 major transmission paths in the Western Interconnection.
By contrast, FAC-501-WECC-1 removes the attachment and, instead,
directs transmission owners to the most current WECC Transfer Path
Table, which is available on the WECC Web site. The table currently
posted on the WECC Web site identifies the same 40 major paths as the
attachment to the approved regional Reliability

Standard.\18\ However, the Commission is concerned that, by referencing
the WECC Transfer Path Table posted on the WECC Web site, the
applicability of FAC-501-WECC-1 could change without review and
approval by the ERO and the Commission, as required to make effective a
modification to a Reliability Standard.
---------------------------------------------------------------------------

    \18\ See Major WECC Transfer Paths table available at http://www.wecc.biz/Standards/Approved%20Standards/Supporting%20Tables/Table%20Major%20Paths%204-28-08.pdf. It appears that the list of
major transfer paths is relatively stable as the list has not
changed for at least the past three years.
---------------------------------------------------------------------------

    19. The possibility for the applicability of the Reliability
Standard to change at any time could create confusion for entities that
need to comply as well as any compliance enforcement staff trying to
determine which entities are responsible for complying with the
Reliability Standard. Under section 215(d)(5) of the FPA, we propose to
direct that WECC develop a modification to the Reliability Standard to
address our concern. For example, WECC could include its criterion for
identifying and modifying major transmission paths listed in the WECC
Transfer Path Table and make an informational filing each time it makes
a modification to the table. Another option would be for WECC to file
its criterion with the Commission and post revised transfer path tables
and referenced catalogs on its Web site before they become effective
with concurrent notification to NERC and the Commission. Alternatively,
the Regional Entity could include the WECC Transfer Path Table as an
attachment to the modified Reliability Standard. In this way, the
Commission would be able to verify that the Regional Entity is applying
the requirements of the regional Reliability Standard in a just and
reasonable manner.
System Operating Limits (SOL)
    20. Second, the Commission is concerned about WECC's use of the
term System Operating limit, as it is defined in the NERC Glossary.\19\
Currently, WECC determines transfer capability based on a ``rated
system path'' methodology and the table of Major WECC Transfer Paths
and associated catalog identify the facilities that make up each rated
system path. For at least ten years, WECC has used the defined term
Operating Transfer Capability limits, and not System Operating Limit,
to describe transmission limitations. WECC TOP-STD-007-0 defines
Operating Transfer Capability limits as:
---------------------------------------------------------------------------

    \19\ A System Operating Limit is defined in the NERC Glossary as
``the value (such as MW, MVar, Amperes, Frequency or Volts) that
satisfies the most limiting of the prescribed operating criteria for
a specified system configuration to ensure operation within
acceptable reliability criteria.'' See NERC Glossary, available at
http://www.nerc.com/docs/standards/rs/Glossary_of_Terms_2010April20.pdf.

    * * * the maximum amount of actual power that can be transferred
over direct or parallel transmission elements comprising:
     An interconnection from one Transmission Operator area
to another Transmission Operator area; or
     A transfer path within a Transmission Operator area.
    The net schedule over an interconnection or transfer path within
a Transmission Operator area shall not exceed the [operating
transfer capability], regardless of the prevailing actual power flow
on the interconnection or transfer path.

    Unlike a System Operating Limit, the definition of Operating
Transfer Capability limits is limited to direct or parallel
transmission elements between or within specific transmission
operators. Moreover, the rating of a System Operating Limit, which is
based on an operating criteria that is either thermally (based on
facility ratings) or stability-based (based on transient stability,
voltage stability, or system voltage limits) is the first element to
calculate in order to determine the Operating Transfer Capability limit
rating.
    21. Based on the above, it appears that a System Operating Limit is
not the same as an Operating Transfer Capability limit. Yet, WECC and
NERC believe that the terms can be used interchangeably and that WECC
revised the regional Reliability Standard to refer to System Operating
Limits to conform its terminology to the NERC Glossary. While we
believe using NERC Glossary terminology is generally preferable,\20\ we
are concerned that, in this instance, the use of a regional definition
might be most appropriate.
---------------------------------------------------------------------------

    \20\ See W. Elec. Coordinating Council Reg'l Reliability
Standard Regarding Automatic Time Error Corr., Order No. 723, 74 FR
25442 (May 28, 2009), 127 FERC ] 61,176, at P 38-40 (2009).
---------------------------------------------------------------------------

    22. Specifically, the Commission is concerned that the introduction
of the NERC Glossary definition of System Operating Limit in
Requirement R1 of the proposed regional Reliability Standard could
create confusion regarding which transmission owners are required to
maintain a transmission maintenance and inspection plan. Requirement R1
of the approved WECC Reliability Standard requires transmission owners
to inspect and maintain ``all bulk power transmission elements (i.e.,
lines, stations and rights of way) included as part of the transmission
facilities (or required to maintain transfer capability) impacting each
of the transmission paths listed * * *.'' \21\ By contrast, Requirement
R1 of WECC's proposed regional Reliability Standard would require
transmission owners to maintain a transmission maintenance and
inspection plan detailing their inspection and maintenance requirements
that ``apply to all transmission facilities necessary for System
Operating Limits associated with each of the transmission paths
identified in the WECC Transfer Path Table.'' \22\ Facilities that are
System Operating Limits associated with transmission paths identified
in the WECC Transfer Path Table are not necessarily on paths identified
in the WECC Transfer Path Table.
---------------------------------------------------------------------------

    \21\ WECC Reliability Standard PRC-STD-005-1, Requirement R1.
    \22\ Proposed WECC Reliability Standard, FAC-501-WECC-1,
Requirement R1, emphasis added.
---------------------------------------------------------------------------

    23. Thus, under the proposed language, Requirement R1 could apply
to more transmission facilities than identified in the WECC Transfer
Path Table. For example, a System Operating Limit for a rated path in
the WECC Transfer Path Table could be defined by a facility on a path
that is not identified in the WECC Transfer Path Table but which is
associated with an identified path. Under these circumstances, it is
unclear whether Requirement R1 would require maintenance on these
facilities that are not identified in the WECC Transfer Path Table. If
so, the requirement might need to apply to transmission owners that do
not own any paths identified in the WECC Transfer Path Table.
Accordingly, the Commission seeks comment as to whether, under
Requirement R1, a transmission owner that owns a major path would be
responsible for maintaining and inspecting transmission facilities
owned by another entity if such facilities are ``necessary for [System
Operating Limits] associated with'' the major path.
Summary
    24. In summary, the Commission proposes to approve FAC-501-WECC-1.
The Commission also proposes to approve NERC's petition to retire
currently-effective WECC PRC-STD-005-1. In addition, the Commission
requests comment on two issues discussed above regarding the (1) Major
WECC Transfer Path table, and (2) use of the term System Operating
Limits.

B. PRC-004-WECC-1--Protection System and Remedial Action Scheme
Misoperation

Background--Currently-Effective PRC-STD-001-1 and PRC-STD-003-1
    25. Currently-effective WECC PRC-STD-001-1 applies to transmission
operators or transmission owners of 40 specified transmission paths.
The regional Reliability Standard requires these entities to certify to
WECC that all (1) protective relay applications and (2) protective
relay settings and logic are appropriate for the specified transmission
paths. It also requires that these entities, once every three years,
certify that information is updated and accurate.
    26. WECC PRC-STD-001-1 corresponds with NERC PRC-001-1, which
addresses protection systems, requires transmission operators and
generator operators to notify appropriate entities of relay or
equipment failures and to coordinate when installing new or modified
protection systems.
    27. Currently-effective WECC PRC-STD-003-1 applies to transmission
operators and owners of the same 40 specified transmission paths as
Reliability Standard PRC-STD-001-1. WECC PRC-STD-003-1 requires
applicable transmission operators and owners to ensure all transmission
and generation protection system misoperations affecting the
reliability of the bulk electric system are analyzed and mitigated.
    28. WECC PRC-STD-003-1 corresponds to NERC PRC-003-1, which also
relates to protection system misoperations.
WECC and NERC Proposal
    29. NERC states that proposed PRC-004-WECC-1 is intended to replace
two currently-effective WECC Reliability Standards, PRC-STD-001-1 and
PRC-STD-003-1. NERC recommends approval of PRC-004-WECC-1, explaining
that it is more stringent than the corresponding NERC PRC-004-1.
Specifically, NERC explains that PRC-004-WECC-1 requires that all
transmission and generation protection system and remedial action
scheme misoperations on major WECC transfer paths be analyzed and
mitigated within a specific timeframe. In contrast, NERC PRC-003-1
requires Regional Entities to establish procedures for review,
analysis, reporting, and mitigation of transmission and generation
Protection System Misoperations, but it does not specifically address
the owners of the transmission and generation facilities. NERC also
explains that NERC PRC-004-1 has requirements for protection system
misoperations, but does not provide for the additional requirements
included in PRC-004-WECC-1.\23\
---------------------------------------------------------------------------

    \23\ See NERC Petition at 11, 19-20.
---------------------------------------------------------------------------

    30. Proposed PRC-004-WECC-1 contains three main provisions.
Requirement R1 provides that ``System Operators and System Protection
Personnel'' of transmission owners and generator owners must analyze
all protection system and remedial action scheme operations.
Requirements R1.1 and R1.2 identify time limits for the review and
analysis of transmission element tripping, remedial action scheme
operations and protection systems. Requirement R2 and the associated
sub-requirements identify actions expected to be performed by
transmission owners and generator owners for each protection system or
remedial action scheme misoperation, including identifying timelines
for removing the equipment that failed from service. Requirement R3
states that transmission owners and generator owners are to submit
incident reports for any misoperation or repair of equipment that
misoperated.
    31. Like the approved regional Reliability Standard, the proposed
regional Reliability Standard is applicable to transmission owners and
transmission operators, but it also is applicable to the generator
owners that own facilities listed in the WECC Transfer Path Table and
the WECC Remedial Action Schemes Table, which are available on WECC's
Web site.\24\ In addition, WECC proposes four new regional definitions
for Functionally Equivalent Protection System, Functionally Equivalent
Remedial Action Scheme, Security-Based Misoperation and Dependability
Based Misoperation.
---------------------------------------------------------------------------

    \24\ See proposed regional Reliability Standard PRC-004-WECC-1,
Section 4 (Applicability).
---------------------------------------------------------------------------

NOPR Proposal
    32. The Commission proposes to approve PRC-004-WECC-1 as just,
reasonable, not unduly discriminatory or preferential, and in the
public interest. The Commission also proposes to approve NERC's
petition to withdraw currently-effective WECC PRC-STD-001-1 and WECC
PRC-STD-003-1. As NERC explains above, it appears that the proposed
PRC-004-WECC-1 is more stringent than the corresponding NERC PRC-004-1.
Moreover, the proposed PRC-004-WECC-1 addresses Commission directives
to develop modifications to the currently-effective regional
Reliability Standards.
    33. Specifically, in approving the currently-effective WECC PRC-
STD-001-1 and WECC PRC-STD-003-1, the Commission directed WECC to make
certain modifications in developing replacement Reliability Standards.
To address these directives, in the proposed Standard, WECC no longer
references any WECC forms, and the text regarding the compliance
monitoring period has been removed from the proposed Standard. In
addition, the proposed regional Reliability Standard no longer
references the regional definition of Disturbance, which did not match
the NERC definition of Disturbance in the NERC Glossary. The proposed
regional Reliability Standard also would remove the definition for
Business Day. Since these terms are not included in any of the existing
or proposed regional Reliability Standards, the Commission proposes to
direct the ERO to remove these regional definitions from the NERC
Glossary, upon approval of the PRC-004-WECC-1. The proposed regional
Reliability Standard also removes the sanctions table and includes
violation risk factors, violation severity levels, measures and time
horizons. The Commission commends WECC for addressing these directives.
    34. Nevertheless, the Commission has concerns regarding several
provisions of the proposed regional Reliability Standard, and seeks
additional comments, as discussed below.
WECC Transfer Path Table
    35. Similar to the discussion above regarding proposed FAC-501-
WECC-1, we are concerned regarding the removal of the list of major
transmission paths from proposed PRC-004-WECC-1 and the replacement
with a link to the WECC Web site. Currently-effective WECC PRC-STD-003-
1 is applicable to transmission owners or operators that maintain
transmission paths listed in an attachment to the Reliability Standard.
The attachment identifies 40 major transmission paths in the Western
Interconnection. By contrast, the proposed PRC-004-WECC-1 removes
attachment A and, instead, directs transmission owners to the most
current WECC Transfer Path Table, which is available on the WECC Web
site. Although the table posted on the WECC Web site lists the same 40
major paths as the attachment to the approved regional Reliability
Standard, the Commission is concerned that by referencing the WECC
Transfer Path Table posted on the WECC Web site, WECC could modify the
document without Commission and industry notice and opportunity to
respond.
    36. The possibility for the applicability of the Reliability
Standard

to change at any time could create confusion for entities that need to
comply as well as any compliance enforcement staff trying to determine
which entities are responsible for complying with the Reliability
Standard. Accordingly, the Commission seeks comment on how NERC and
WECC intend to develop and provide notice of proposed changes to the
WECC Transfer Path Table. We also seek comment on how NERC and WECC
will ensure that changes to the applicability of the Reliability
Standard will not undermine its effectiveness. We propose to direct
WECC to develop a modification to the Reliability Standard to address
our concern. For example, WECC could include its criterion for
identifying and modifying major transmission paths listed in the WECC
Transfer Path Table and make an informational filing each time it makes
a modification to the table. Another option would be for WECC to file
its criterion with the Commission and post revised transfer path tables
and referenced catalogs on its Web site before they become effective
with concurrent notification to NERC and the Commission. Alternatively,
the Regional Entity could include the WECC Transfer Path Table as an
attachment to the modified Reliability Standard. In this way, the
Commission would be able to verify that the Regional Entity is applying
the requirements of the regional Reliability Standard in a just and
reasonable manner.
Proposed Regional Definitions
    37. The proposed regional Reliability Standard includes four new
regional definitions meant to apply only in WECC. Two of the proposed
definitions (Functionally Equivalent Protection System and Functionally
Equivalent Remedial Action Scheme) have added ``functionally
equivalent'' to terms that already exist in the NERC Glossary.\25\ The
NERC Glossary definition of Protection System lists the types of
equipment that can be used as protection systems (i.e. protective
relays, associated communication systems, voltage and current sensing
devices, station batteries and DC control circuitry). By contrast, the
proposed WECC definition of Functionally Equivalent Protection System
is not limited to any specific components or operating characteristics
but, instead, defines Functionally Equivalent Protection Systems based
on what they can do: ``[e]ach Protection System can detect the same
faults within the zone of protection and provide the clearing times and
coordination needed to comply with all Reliability Standards.'' In
addition, the NERC Glossary defines Remedial Action Scheme, or Special
Protection System, as ``[a]n automatic protection system designed to
detect abnormal or predetermined system conditions, and take corrective
actions other than and/or in addition to the isolation of faulted
components to maintain system reliability.'' \26\ By contrast, WECC
proposes to define Functionally Equivalent RAS as ``[a] Remedial Action
Scheme that provides the same performance as follows: Each [Remedial
Action Scheme] can detect the same conditions and provide mitigation to
comply with all Reliability Standards. Each [Remedial Action Scheme]
may have different components and operating characteristics.''
---------------------------------------------------------------------------

    \25\ See NERC Glossary definitions for Protection System and
Remedial Action Scheme.
    \26\ NERC Glossary definition of Special Protection System
(Remedial Action Scheme), available at http://www.nerc.com/docs/standards/rs/Glossary_of_Terms_2010April20.pdf.
---------------------------------------------------------------------------

    38. The Commission has expressed concern about the unnecessary
proliferation of glossary terms and has directed the ERO to be vigilant
in assuring that a regional definition is consistent with both NERC
Glossary terms and other approved Regional Entity glossary terms.\27\
In the instant proceeding, we are concerned that the proposed
definitions of Functionally Equivalent Protection System and
Functionally Equivalent RAS do not add any further clarity to the NERC
Glossary terms. Accordingly, we seek an explanation from WECC and other
interested commenters regarding whether these new terms are more
inclusive than the corresponding NERC Glossary definitions and, if so,
how.
---------------------------------------------------------------------------

    \27\ Order No. 723, 74 FR 25,442 at P 37-40.
---------------------------------------------------------------------------

    39. WECC proposes to define Functionally Equivalent Protection
System as ``[a] Protection System that provides performance as follows:
Each Protection System can detect the same faults within the zone of
protection * * *.'' \28\ It is unclear what the phrase ``detect the
same faults'' means within this definition. For example, this phrase
could refer to the ability of one protection system to act as a back-up
for another protection system. Alternatively, this phrase could imply
that a protection system should be able to detect a fault within in a
different sub-area of the same zone of protection. Accordingly, we seek
comment on the meaning of the phrase ``the same faults'' within the
definition.
---------------------------------------------------------------------------

    \28\ See Proposed Reliability Standard PRC-004-WECC-1, proposed
definition of Functionally Equivalent Protection System.
---------------------------------------------------------------------------

    40. In addition, the current NERC Glossary definition of
Misoperation includes: (1) Failure of a protection system to operate;
(2) protection system operation for a fault outside of the planned zone
of protection; and (3) unintentional operation of a protection system.
Instead of using this NERC Glossary definition, WECC has developed two
new terms: Security-Based Misoperations and Dependability-Based
Misoperations. The proposed WECC definitions address: (1) Incorrect
operation of a protection system (Security-Based Misoperation); and (2)
absence of a protection system to operate (Dependability-Based
Misoperation). The bifurcation of the term Misoperation may be
confusing because at least some of the requirements for each type of
misoperation appear to overlap. We seek an explanation from WECC and
other interested commenters regarding why these two new regional terms
are necessary or desirable within the context of the proposed regional
Reliability Standard, and how they will enhance reliability.
Summary
    41. The Commission proposes to approve PRC-004-WECC-1 as just,
reasonable, not unduly discriminatory or preferential, and in the
public interest. The Commission also proposes to approve NERC's
petition to withdraw currently-effective WECC PRC-STD-001-1 and WECC
PRC-STD-003-1. In addition, the Commission requests comment on three
issues discussed above regarding (1) the Major WECC Transfer Path
table; (2) whether the proposed regional terms, Functionally Equivalent
Protection System and Functionally Equivalent RAS, are more inclusive
than the corresponding NERC Glossary definitions; and, (3) the
necessity of the proposed regional terms, Security-Based Misoperations
and Dependability-Based Misoperations.

C. VAR-002-WECC-1--Automatic Voltage Regulators

Background
    42. Applicable to all generator operators and generator owners,
NERC VAR-002-1.1b is meant to ensure that generators provide reactive
and voltage control necessary to ensure voltage levels, reactive flows,
and reactive resources are maintained within applicable facility
ratings to protect equipment and the reliable operation of the
Interconnection. Unless exempted by the transmission operator, each

generator operator must maintain the generator voltage or reactive
power output (within applicable facility ratings) \29\ as directed by
the transmission operator. Thus, the NERC Reliability Standard does not
require generator operators to operate in automatic voltage control
mode when they are operating outside of their facility rating, e.g.,
generators that are starting-up or generators used to serve peak load
that typically run at low megawatt levels.
---------------------------------------------------------------------------

    \29\ NERC defines ``facility rating'' as the maximum or minimum
voltage, current, frequency, or real or reactive power flow through
a facility that does not violate the applicable equipment rating of
any equipment comprising the facility.
---------------------------------------------------------------------------

    43. On June 8, 2007, the Commission approved WECC VAR-STD-002a-1,
which applies to generator operators of synchronous generating units
equipped with automatic voltage regulators in the Western
Interconnection. The stated purpose of the regional Reliability
Standard is to ensure that automatic voltage control equipment on
synchronous generators shall be kept in service at all times, except in
specified circumstances, and that outages of such equipment must be
coordinated. It requires that generator operators must normally operate
automatic voltage control equipment in voltage control mode and set to
respond effectively to voltage deviations. Nevertheless, the levels of
non-compliance associated with the approved regional Reliability
Standard permit generator operators to operate without automatic
voltage control equipment for two percent of the operating hours in a
calendar year without penalty. The Commission approved the current
regional Reliability Standard as more stringent than the NERC
Reliability Standard because the WECC regional Reliability Standard
requires synchronous generators to have their automatic voltage
regulators in service at all times with exceptions limited to specific
circumstances. In contrast, the NERC Reliability Standard does not
specify a list of exceptions, which could mean that transmission
operators may, upon request of the generator operators, permit outages
of automatic voltage regulators for a broader range of reasons.\30\
---------------------------------------------------------------------------

    \30\ North American Electric Reliability Corp., 119 FERC ]
61,260 at P 116.
---------------------------------------------------------------------------

WECC and NERC Proposal
    44. NERC requests approval of VAR-002-WECC-1 (Automatic Voltage
Regulators) and requests the concurrent retirement of WECC VAR-STD-
002a-1. Proposed VAR-002-WECC-1 would be applicable to all generator
operators and transmission operators that operate synchronous
condensers. It would only apply to synchronous generators and
synchronous condensers that are connected to the bulk electric system.
    45. Proposed VAR-002-WECC-1 contains two requirements. Requirement
R1 provides that each generator operator and transmission operator
shall have automatic voltage regulators in service and in automatic
voltage control mode for synchronous generators and synchronous
condensers during 98 percent of all operating hours unless exempted by
the transmission operator. Sub-requirements R1.1 through R1.10 detail
the type of exemptions that the transmission operator may grant to the
generator operator to excuse the generator from operating the automatic
voltage regulator in automatic voltage control mode. Requirement R2
states that each generator operator and transmission operator must have
documentation identifying the number of hours excluded for each sub-
requirement R1.1 through R1.10.
    46. WECC also proposes to replace the sanctions table with
violation risk factors, violation severity levels, measures and time
horizons. Finally, WECC proposes a new glossary term, Commercial
Operation, to be applicable only in the Western Interconnection.
    47. During the standards development process, NERC expressed
concern that proposed Requirement R1 was less stringent than the
current NERC Reliability Standard.\31\ WECC responded that, although
Requirement R1 appears to decrease the number of operating hours that a
generator operator and transmission operator must keep automatic
voltage regulators in service and in automatic voltage control mode
from 100 percent to 98 percent, the 98 percent requirement is a
translation of the limits set in the levels of non-compliance
associated with the current regional Reliability Standard.\32\ In
addition, WECC explained that the two percent allowance provides more
time to start up generating facilities when the automatic voltage
regulators are not yet in voltage control mode and allows for
evaluation when a generator operator responds to an unforeseen
event.\33\ WECC also pointed out that NERC VAR-002-1a does not place
any restrictions on the length of time or range of acceptable reasons
for operating in modes other than automatic voltage control mode. By
contrast, WECC pointed out that the proposed VAR-002-WECC-1 limits the
range of acceptable reasons and time for operating a generator without
the automatic voltage regulator in service and controlling voltage.\34\
---------------------------------------------------------------------------

    \31\ NERC Petition at 34.
    \32\ The levels of non-compliance assigned to the currently-
effective regional Reliability Standard specify that there shall be
a level 1 non-compliance if automatic voltage regulators are in
service less than 98 percent but at least 96 percent or more of all
hours during which the synchronous generating unit is on line for
each calendar quarter.
    \33\ Specifically, WECC explains ``[t]he two percent allowance
provides for time to start up generating facilities when the
[automatic voltage regulators] are not yet in voltage control mode.
It also allows for evaluation when the Generator Operators respond
to unforeseen events.'' WECC further explains ``[p]eaking units
often operate, for short periods, at low megawatt levels (below
where manufactures recommend placing the [automatic voltage
regulators] in-service). The exclusion below the five percent
threshold during a calendar quarter permits the continued practice
of allowing the operation of peaking units without penalty for
having an out-of-service [automatic voltage control regulators] per
the manufacturer recommendations.'' NERC Petition at 34-35.
    \34\ Id.
---------------------------------------------------------------------------

    48. NERC also notes that, during the Reliability Standards
development process, it expressed concern regarding sub-requirement
R1.1, which includes an exemption for units operating less than five
percent of all hours during a calendar quarter. NERC explains that it
raised a concern that the proposed sub-requirement ``excludes the hours
attributed to the synchronous generator or condenser that operates for
less than five percent of all hours during any calendar quarter.'' \35\
WECC responded by explaining that there is no change in the basic five
percent threshold between the existing regional Reliability Standard
and the proposed regional Reliability Standard. WECC further explained
that peaking units often operate, for short periods, at low megawatt
levels (below where manufacturers recommend placing the automatic
voltage regulators in-service). WECC states that the exclusion below
the five percent threshold during a calendar quarter permits the
continued practice of allowing the operation of peaking units without
penalty for having an out-of-service automatic voltage regulator per
the manufacturer's recommendations.\36\
---------------------------------------------------------------------------

    \35\ Id. at 34-35.
    \36\ Id. at 35.
---------------------------------------------------------------------------

    49. NERC states that, whereas NERC VAR-002-1a requires only that a
generator operator notify its transmission operator when it either
removes or operates the automatic voltage regulator in a condition
other than automatic voltage control mode and does not limit the amount
of time for such operations, the proposed WECC regional Reliability
Standard sets only very limited circumstances for when a generator's
automatic voltage regulator should be operated in a mode other than

the automatic voltage control mode and further limits the cumulative
timeframe for doing so. Thus, NERC represents that the proposed
regional Reliability Standard is more stringent than the NERC
Reliability Standard.\37\
---------------------------------------------------------------------------

    \37\ Id. at 29.
---------------------------------------------------------------------------

NOPR Proposal
    50. The Commission proposes to approve VAR-002-WECC-1 as just,
reasonable, not unduly discriminatory or preferential, and in the
public interest. Further, the Commission proposes the concurrent
retirement of currently-effective WECC VAR-STD-002a-1. As represented
by NERC, it appears that proposed VAR-002-WECC-1 is more stringent than
the corresponding NERC Reliability Standard.
    51. Moreover, in approving the currently-effective WECC VAR-STD-
002a-1, the Commission directed WECC to make certain modifications in
developing a replacement Reliability Standard. To address these
directives, WECC has added violation risk factors, violation severity
levels, measures and time horizons, and has removed the sanctions
table. WECC also has re-written Requirement WR1 so that it does not
include more than one main topic, removed language suggested to move to
the Additional Compliance Information section, and removed the
reference to Form A.5 to address recommendations made by NERC to modify
WECC VAR-STD-002a-1.\38\ Thus, it appears that proposed VAR-002-WECC-1
maintains stringencies above the corresponding NERC Reliability
Standard while providing additional clarity and conformity. Thus, the
Commission proposes to approve the regional Reliability Standard.
---------------------------------------------------------------------------

    \38\ See id. at 31.
---------------------------------------------------------------------------

    52. In addition, the Commission seeks comments on several issues
posed by the WECC proposal, as discussed below.
Automatic Voltage Regulators
    53. Requirement R1 of proposed VAR-002-WECC-1 provides that
``Generator Operators and Transmission Operators shall have [automatic
voltage regulators] in service and in automatic voltage control mode
98% of all operating hours for synchronous generators or synchronous
condensers.'' \39\ Requirement R1 then identifies ten circumstances in
which a generator operator or transmission operator is excused from
this requirement. By specifying the circumstances in which a generator
operator or transmission operator is excused from operating in
automatic voltage regulator mode, the proposed requirement appears to
be more stringent than the requirement in NERC VAR-002-1.1b.
---------------------------------------------------------------------------

    \39\ Proposed regional Reliability Standard VAR-002-WECC-1,
Requirement R1.
---------------------------------------------------------------------------

    54. The Commission believes that, where installed, automatic
voltage regulators should be in-service at all times except in
circumstances when the generator is operating at an output level that
is not within the design parameters of the automatic voltage regulator
or operations of the automatic voltage regulator would result in
instability. Automatic voltage regulators are intended to assist in
maintaining the reliability of the Bulk-Power System by controlling
system voltages. In addition, System Operating Limits for transmission
paths in the bulk electric system in the Western Interconnection assume
that automatic voltage regulators are in service to control voltage to
support the transfer capability.\40\ When automatic voltage regulators
are out of service, the time required to appropriately respond to
disturbances that cause voltage deviations would increase due to the
time required to take manual action. If not corrected in sufficient
time, these voltage deviations could lead to instability, uncontrolled
separation and cascading outages.
---------------------------------------------------------------------------

    \40\ See NERC Petition at 29.
---------------------------------------------------------------------------

    55. Although the proposed regional Reliability Standard would limit
the circumstances in which a transmission operator or generator
operator is excused from keeping automatic voltage regulators in
automatic voltage control mode, it also provides a blanket exemption
for two percent of all operating hours. In its petition, NERC explains
that this exemption would accommodate generating facilities when they
are starting up and when the automatic voltage regulators are not yet
in voltage control mode. NERC also explains that this exemption allows
for evaluation when the generator operators respond to unforeseen
events.\41\ These limitations identified by NERC in its petition are
not explicit in the requirements of the proposed regional Reliability
Standard.
---------------------------------------------------------------------------

    \41\ NERC Petition at 34-35.
---------------------------------------------------------------------------

    56. We are concerned that the proposed provision is written more
broadly than necessary. We believe it is appropriate to exempt
automatic voltage regulators from being in-service during times when
the generator is operating outside of applicable facility ratings.
However, as proposed, Requirement R1 would provide generators with a
blanket exemption--equal to two percent of all operating hours--from
the requirement to maintain automatic voltage regulators in-service. We
seek comment on whether the Commission should direct WECC to develop a
modification to the proposed regional Reliability Standard to address
our concern. For example, consistent with NERC's explanation, NERC
could develop a modification replacing the blanket two percent
exemption with a list of specific exemptions that would accommodate
generating units that are starting up or responding to unforeseen
events and are operating outside of applicable facility ratings.
    57. The purpose of NERC VAR-002-1.1b is to ensure appropriate
reactive and voltage control are provided to maintain voltage levels,
reactive flows, and reactive resources are within applicable facility
ratings for Reliable Operation. Requirement R1 of VAR-002-1.1b states
that the ``Generator Operator shall operate each generator connected to
the interconnected transmission system in the automatic voltage control
mode (automatic voltage regulator in service and controlling voltage)
unless the Generator Operator has notified the Transmission Operator.''
Requirement R2 continues that ``[u]nless exempted by the Transmission
Operator, each Generator Operator shall maintain the generator voltage
or Reactive Power output (within applicable Facility Ratings) as
directed by the Transmission Operator.'' Based on the same rationale
articulated regarding the two percent exemption in the regional
Reliability Standard, we have a concern regarding the corresponding
NERC Reliability Standard. In particular, we seek comment on whether it
would provide additional support for Bulk-Power System reliability to
propose to direct the ERO to develop a modification to NERC VAR-002-
1.1b. Specifically to clarify that, if a generator has an automatic
voltage regulator installed, it must be in-service and controlling
voltage at all times, equipment and facility ratings permitting, unless
exempted by the transmission operator. We believe that such a
modification could be consistent with Commission precedent.\42\ The
Commission's concerns regarding the NERC Reliability Standard are
introduced here as they correspond with certain elements of the WECC
standards that are the subject of the immediate proceeding. However,
any proposal to direct the development of modifications to the NERC
Reliability

Standards would be addressed in a separate proceeding.
---------------------------------------------------------------------------

    \42\ Order on Reliability Standard Interpretation, 132 FERC ]
61,220, at P 27 (2010) (VAR Interpretation Order).
---------------------------------------------------------------------------

Exclusion of Synchronous Generators that Operate for Less Than Five
Percent of All Hours During a Calendar Quarter
    58. Requirement R1.1 of proposed VAR-002-WECC-1 would allow
exclusion of any synchronous generator or synchronous condenser that
``operates for less than five percent of all hours during any calendar
quarter'' from operating with automatic voltage regulator in service
and in automatic voltage control mode. During the Reliability Standard
development process of the proposed regional Reliability Standard, NERC
expressed concern regarding the exclusion of these hours.\43\ WECC
responded by explaining that the ``exclusion below the five percent
threshold during a calendar quarter permits the continued practice of
allowing the operation of peaking units without penalty for having an
out-of-service [automatic voltage regulator] per the manufacturer
recommendations'' since ``[p]eaking units often operate, for short
periods, at low megawatt levels (below where manufacture[r]s recommend
placing the [automatic voltage regulators] in-service).'' \44\ Thus, it
appears that WECC developed the five percent threshold provision to
account for out-of-service automatic voltage regulators per the
manufacturer recommendations regarding automatic voltage regulator
design limitations.
---------------------------------------------------------------------------

    \43\ NERC Petition at 34-35.
    \44\ Id. at 35.
---------------------------------------------------------------------------

    59. We are concerned, however, that the provision is written more
broadly than necessary. It appears inefficient to allow an exemption
for any synchronous generator or synchronous condenser that ``operates
for less than five percent of all hours during any calendar quarter''
in order to address concerns about operation limits based on
manufacture recommendations, and could potentially exempt other
generator operators and transmission operators. The Commission seeks
comment on whether it is necessary or desirable to direct WECC to
develop a modification through its Reliability Standards development
process that addresses this concern. For example, one reasonable
solution would be to develop a replacement requirement that directly
addresses the need for an exemption for peaking units operating
automatic voltage regulators when necessary to satisfy manufacturer
recommendations regarding the operation of an automatic voltage
regulator.
Automatic Voltage Regulator Replacement
    60. Proposed sub-requirement R1.6 lengthens the automatic voltage
regulator replacement timeline due to component failure from 15 months
to 24 months ``to accommodate design and procurement especially for
nuclear units.'' \45\ The ERO supported the extension of the outage
time frame for the automatic voltage regulators. The Commission, giving
due weight to WECC and the ERO, proposes to accept the Reliability
Standard with the modification to this provision.
---------------------------------------------------------------------------

    \45\ NERC Petition at Exhibit C, ``Consideration of Comments for
VAR-002-WECC-1--Automatic Voltage Regulator Comments were due
January 2, 2008.''
---------------------------------------------------------------------------

    61. We are concerned that allowing an additional nine months of
non-operation of automatic voltage regulator is not necessary for many,
if not most, units. The additional replacement time could lead to a
decrease in generation that can react in automatic voltage regulator
mode. In the event of a contingency, this could have an impact on bulk
electric system reliability. We believe that it may be appropriate to
direct WECC to develop a modification to this provision to address our
concern. For example, WECC could allow fifteen months for replacement
with an opportunity to seek an extension up to nine months where
justified. Alternatively, WECC could retain a fifteen month replacement
period for non-nuclear generator units, and a twenty-four month
replacement period for nuclear generator units. The Commission seeks
comment from WECC, NERC and other interested commenters regarding the
historical replacement period for nuclear and non-nuclear units, and
the appropriateness of the Commission proposal. For example, comments
could include documentation and timeline summary of previous ``design
and procurement'' for automatic voltage regulator component failures
demonstrating that automatic voltage regulator outages frequently last
more than 15 months in order to support extending the replacement
period.
Responding to Voltage Deviations
    62. The current regional Reliability Standard provides that ``[a]ll
synchronous generators with automatic voltage control equipment shall
normally be operated in voltage control mode and set to respond
effectively to voltage deviations.'' The proposed regional Reliability
Standard removes this requirement but the NERC Petition does not
provide any explanation why, or potential impact of, removing the
provision.
    63. We seek further explanation from WECC, NERC, and public
comment, on the impact of removing this provision from the currently-
effective WECC regional Reliability Standard. We are concerned that, by
removing the requirement for automatic voltage regulators to respond
effectively to voltage deviations, the proposed regional Reliability
Standard would not require entities to assess the performance of the
automatic voltage regulators to ensure they are appropriately
responding to voltage deviations to support reliability of the Bulk-
Power System.
Summary
    64. The Commission proposes to approve VAR-002-WECC-1 as just,
reasonable, not unduly discriminatory or preferential, and in the
public interest. Further, the Commission proposes the concurrent
retirement of currently-effective WECC VAR-STD-002a-1. In addition, the
Commission requests comment on issues discussed above regarding whether
the Commission should direct WECC to develop modifications to the
proposed regional Reliability Standard that would: (1) Replace the
blanket two percent exemption with a list of specific exemptions; and
(2) more narrowly tailor the exemption for any synchronous generator or
synchronous conductor that operates less than five percent of all
operating hours during any calendar quarter. The Commission also seeks
comment on the historical replacement period for nuclear and non-
nuclear units and whether the Commission should direct WECC to modify
the regional Reliability Standard to limit the acceptable duration of
automatic voltage regulator outages. Finally, the Commission seeks
comment on the impact of removing the requirement that all generators
with automatic voltage control equipment be operated in automatic
voltage control mode and set to respond to voltage deviations.

D. VAR-501-WECC-1--Power System Stabilizer

Background
    65. Currently-effective WECC VAR-STD-002b-1 applies to generator
operators with generators equipped with power system stabilizers. The
current regional Reliability Standard requires that generator operators
keep power system stabilizers in service at all times, except in
specified circumstances. Further, currently-effective WECC VAR-

STD-002b-1 requires that power system stabilizers are properly tuned in
accordance with WECC Criterion, referenced in the standard. This
regional Reliability Standard does not have a corresponding NERC
Reliability Standard. The Commission approved the current regional
Reliability Standard because it addresses matters that are not
addressed by a NERC Reliability Standard.\46\
---------------------------------------------------------------------------

    \46\ See North American Electric Reliability Corp., 119 FERC ]
61,260 at P 122.
---------------------------------------------------------------------------

WECC and NERC Proposal
    66. NERC requests approval of VAR-501-WECC-1 and asks for the
concurrent retirement of the current WECC VAR-STD-002b-1. Proposed VAR-
501-WECC-1 would apply to generator operators. Its purpose is to ensure
that power system stabilizer on synchronous generators are kept in
service.
    67. Proposed VAR-501-WECC-1 contains two requirements. Requirement
R1 provides that each generator operator with a synchronous generator
equipped with a power system stabilizer must have the power system
stabilizer in service during 98 percent of all operating hours. NERC
explains that a power system stabilizer is part of the excitation
control system of a generator used to increase power transfer levels by
improving power system dynamic performance. Sub-requirements R1.1
through R1.12 set forth exceptions to the operating requirement in
Requirement R1. Requirement R2 states that each generator operator must
have documentation identifying the number of hours excluded for each
sub-requirement R1.1 through R1.12.
    68. In the Petition, NERC and WECC explain that the purpose of VAR-
501-WECC-1 is to ensure that power system stabilizers on synchronous
generators are kept in service. NERC and WECC state that the
corresponding NERC VAR-002-1.1b requires only that a generator operator
notify its transmission operator when it removes the power system
stabilizer from service and does not limit the amount of time for
operating generators without power system stabilizers in service.\47\
NERC and WECC explain that, in contrast, proposed VAR-501-WECC-1
requires power system stabilizers to be in service except for specific
conditions and for a cumulative time limit per quarter. Thus, according
to NERC and WECC, the proposed regional Reliability Standard is more
stringent than the corresponding NERC Reliability Standard.
---------------------------------------------------------------------------

    \47\ NERC Petition at 36.
---------------------------------------------------------------------------

    69. In addition, the Petition explains that the proposed regional
Reliability Standard includes modifications to address the Commission's
directives in the June 2007 order that accepted WECC's currently-
effective standards.\48\ In particular, WECC proposes to replace the
current sanctions table with violation risk factors, violation severity
levels, measures and time horizons. Proposed VAR-501-WECC-1 removes the
definition of ``disturbance'' and makes certain directed formatting
revisions. WECC also proposes a new glossary term, Commercial
Operation, to be applicable only in the Western Interconnection.\49\
---------------------------------------------------------------------------

    \48\ North American Electric Reliability Corp., 119 FERC ]
61,260 at P 123.
    \49\ Pursuant to WECC's proposal, ``Commercial Operation'' is
defined as ``* * * receiving all approvals necessary for operation
after completion of initial start-up testing.'' Requirement R1.1 of
VAR-501-WECC-1 excludes a unit from compliance when ``the
synchronous generator has not achieved Commercial Operation.''
---------------------------------------------------------------------------

    70. In the Petition, NERC notes that, during the Reliability
Standards development process, NERC expressed concern that the proposed
regional Reliability Standard appears less stringent than the current
regional Reliability Standard because it would reduce the number of
hours that generator operators must keep power system stabilizers in
service from 100 percent to 98 percent of all operating hours.\50\ WECC
responded to NERC's concerns by explaining that the requirement had not
been modified but rather was a translation of the existing levels of
non-compliance into the requirements of the proposed regional
Reliability Standard.\51\ WECC further explained that the levels of
non-compliance for the current regional Reliability Standard allow
generator operators to operate without power system stabilizers in
service for two percent of all operating hours without penalty.\52\
---------------------------------------------------------------------------

    \50\ NERC Petition at 40.
    \51\ Id.
    \52\ The levels of non-compliance assigned to the currently-
effective regional Reliability Standard specify that there shall be
a level 1 non-compliance if power system stabilizers are in service
less than 98 percent but at least 96 percent or more of all hours
during which the synchronous generating unit is on line for each
calendar quarter.
---------------------------------------------------------------------------

    71. NERC also notes that, during the regional Reliability Standards
development process, NERC expressed concern that sub-requirement R1.1
of the proposed regional Reliability Standard excludes the hours for
power system stabilizer operation attributed to the synchronous
generator that operates for less than five percent of all hours during
any calendar quarter. WECC responded that there is no change in the
basic five percent threshold between the current and the proposed
regional Reliability Standards. WECC further explained that peaking
units often operate, for short periods, at low megawatt levels where
manufacturers do not recommend using a power system stabilizer. WECC
stated that the exclusion below the five percent threshold during a
calendar quarter permits the continued practice of allowing the
operation of peaking units without penalty for having an out-of-service
power system stabilizer per the manufacturer recommendations.
NOPR Proposal
    72. The Commission proposes to approve VAR-501-WECC-1 as just,
reasonable, not unduly discriminatory or preferential, and in the
public interest. The Commission also proposes to approve NERC's
proposed retirement of currently-effective WECC VAR-STD-002b-1.
    73. As explained by NERC and WECC, proposed VAR-501-WECC-1 is more
stringent than the corresponding NERC VAR-002-1.1b. Unlike the NERC
Reliability Standard, proposed VAR-501-WECC-1 requires power system
stabilizers to be in service except for specific conditions and for a
cumulative time limit per quarter. Further, the proposed regional
Reliability Standard reflects modifications to address the Commission's
concerns in the June 2007 order.\53\ As discussed above, WECC has added
violation risk factors, violation severity levels, measures and time
horizons and has removed the reliability management system sanctions
table. WECC also made formatting changes, removed the definition for
``Disturbance,'' and included a definition of ``Commercial Operation.''
Accordingly, the Commission proposes to approve proposed VAR-501-WECC-1
because it appears to be more stringent than the requirements of the
applicable NERC Reliability Standards while providing additional
clarity and conformity over the current regional Reliability Standard.
---------------------------------------------------------------------------

    \53\ See North American Electric Reliability Corp., 119 FERC ]
61,260 at P 123.
---------------------------------------------------------------------------

    74. In addition to the modifications that address the Commission's
earlier directives, WECC's proposal includes further modifications
about which the Commission seeks comment.
    75. The language of proposed VAR-501-WECC-1 is similar to the
proposed VAR-002-WECC-1, addressed above. As a result, the Commission
discusses below several similar issues as discussed above regarding
VAR-002-WECC-1. In particular, the same items

discussed above regarding the requirement that generator operators meet
the requirements of the proposed regional Reliability Standard only 98
percent of the time, and the exclusion of hours for generators that
operate less than five percent of all hours during a calendar quarter,
apply to this proposed regional Reliability Standard as well.
In-Service Requirement
    76. As proposed, Requirement R1 of VAR-501-WECC-1 provides that
``Generator Operators shall have [power system stabilizers] in service
98 [percent] of all operating hours for synchronous generators equipped
with [power system stabilizers].'' \54\ Requirement R1 also sets forth
twelve circumstances in which a generator operator is excused from this
requirement. By specifying the circumstances in which a generator
operator is excused from keeping its power system stabilizer in
service, the proposed requirement appears to be more stringent than the
currently-effective requirement in NERC VAR-002-1.1b, which requires
only that a generator operator notify its transmission operator when
there is a change in status of its power system stabilizer.
---------------------------------------------------------------------------

    \54\ Proposed regional Reliability Standard VAR-501-WECC-1,
Requirement R1.
---------------------------------------------------------------------------

    77. The Commission believes that, where installed, power system
stabilizers should be in-service at all times, equipment and facility
ratings permitting, unless exempted by the transmission operator. Power
system stabilizers are designed to ensure that the generator provides
the proper damping to maintain system stability when generation and
transmission outages occur.\55\ As NERC explains, in the Western
Interconnection System, Operating Limits for transmission paths in the
bulk electric system assume that power system stabilizers are in
service to enhance system damping. When power system stabilizers are
out of service, generators may not be able to dampen oscillations
occurring on the system, which could lead to instability, uncontrolled
separation and cascading outages.
---------------------------------------------------------------------------

    \55\ Id. at 35.
---------------------------------------------------------------------------

    78. Although the proposed regional Reliability Standard would limit
the circumstances in which a generator operator is excused from keeping
power system stabilizers in-service, it also provides a blanket
exemption for two percent of all operating hours. Similar to our
discussion above on VAR-002-WECC-1, we believe that an exemption might
be appropriate to accommodate generating facilities when they are
starting up or operating outside of their facility ratings. However,
proposed regional Reliability Standard provides no limitation as to
when generating units may use the two percent exemption.
    79. We are concerned that the proposed provision is written more
broadly than necessary. We believe it is appropriate to exempt power
system stabilizers from being in-service during times when the
generator is operating outside of applicable facility ratings. However,
as proposed, Requirement R1 would provide a blanket exemption for
generators to maintain power system stabilizers in-service for two
percent of all operating hours without qualification. We seek comment
on whether the Commission should direct WECC to develop a modification
to the proposed regional Reliability Standard that would address our
concern. For example, WECC could develop a modification to replace the
blanket two percent exemption with a more specific exemption that would
accommodate generating units that are starting up or are operating
outside of applicable facility ratings.
    80. Requirement R3 and R3.1 of VAR-002-1.1b require a generator
operator to inform the transmission operator as soon as possible, but
within 30 minutes, whenever there is a change in status or capability,
and the expected duration of this change, of any reactive power
resource including power system stabilizers. Based on similar concerns
articulated above regarding the regional Reliability Standard, we have
concerns about the NERC Reliability Standard and whether it adequately
addresses power system stabilizer in-service obligations. In
particular, we seek comment on whether it would be appropriate to
propose to direct the ERO to develop a modification to NERC VAR-002-
1.1b to clarify that, if a generator has a power system stabilizer
installed, it must be in-service at all times, equipment and facility
ratings permitting, unless exempted by the transmission operator. The
Commission's concerns regarding the NERC Reliability Standard are
introduced here as they correspond with certain elements of the WECC
standards that are the subject of the immediate proceeding. However,
any proposal to direct the development of modifications to the NERC
Reliability Standards would be addressed in a separate proceeding.
Exclusion of Synchronous Generators That Operate for Less Than Five
Percent of All Hours During a Calendar Quarter
    81. Requirement R1.1 of proposed VAR-501-WECC-1 would allow
exclusion of any synchronous generator that operates for less than five
percent of all hours during any calendar quarter from operating with
power system stabilizer in service. During the Reliability Standard
development process of the proposed regional Reliability Standard, NERC
expressed concern regarding the exclusion of these hours.\56\ WECC
responded by explaining that the ``exclusion below the five percent
threshold during a calendar quarter permits the continued practice of
allowing the operation of peaking units without penalty for having an
out-of-service power system stabilizer per the manufacturer
recommendations'' since ``[p]eaking units often operate, for short
periods, at low megawatt levels (below where manufacture[r]s recommend
placing the [power system stabilizer] in-service).'' \57\ Thus, it
appears that WECC developed the five percent threshold provision to
account for out-of-service power system stabilizer per the manufacturer
recommendations.
---------------------------------------------------------------------------

    \56\ Id. at 40.
    \57\ Id.
---------------------------------------------------------------------------

    82. We seek comment on whether the proposed provision is written
more broadly than necessary. Comments should address why it is
appropriate to allow an exemption for any synchronous generator that
``operates for less than five percent of all hours during any calendar
quarter'' to address concerns about limitations based on manufacturer
recommendations, and could potentially exempt other generator
operators. Based on the comments received, the Commission may propose
to direct WECC to develop a modification through its Reliability
Standards development process that addresses this concern. It appears
that one reasonable solution would be to develop a replacement
requirement that directly addresses the need for an exemption for
peaking units that may not operate with power system stabilizers to
satisfy manufacturer recommendations.
Power System Stabilizer Replacement
    83. Proposed sub-requirement R1.10 lengthens the power system
stabilizer replacement timeline due to component failure from 15 months
to 24 months ``to accommodate design and procurement

especially for nuclear units.'' \58\ The Commission notes that no other
evidence was provided in the record to support the extension of the
outage time frame for the power system stabilizers from 15 months to 24
months. The Commission proposes to accept the Reliability Standard with
this modification.
---------------------------------------------------------------------------

    \58\ NERC Petition at Exhibit C, ``Consideration of Comments for
VAR-501-WECC-1--Power System Stabilizer Comments were due January 2,
2008.''
---------------------------------------------------------------------------

    84. However, since the rationale provided for the increased
replacement period is based on the needs of nuclear power generators,
we are concerned whether the additional nine months is necessary for
many, if not most, units. The additional replacement time could lead to
a decrease in generation units operating with the power system
stabilizers. In the event of a contingency, this could have an impact
on bulk electric system reliability. Accordingly, the Commission seeks
comment from WECC, NERC and other interested commenters regarding the
historical replacement period for nuclear and non-nuclear units, and
the appropriateness of the Commission proposal. For example, comments
could include documentation and timeline summary of previous ``design
and procurement'' for power system stabilizer component failures
demonstrating that power system stabilizer outages frequently last more
than 15 months in order to support extending the replacement period.
Power System Stabilizer Tuning
    85. The current regional Reliability Standard requires all
generators with power system stabilizers to be properly tuned in
accordance with the WECC requirements.\59\ The proposed regional
Reliability Standard removes the tuning requirement without explanation
or analysis of the potential impact of removing the provision. The
Commission believes that, if the power system stabilizer is in service,
it must be properly tuned to enhance system damping and maintain system
stability. The Commission, therefore, seeks further explanation from
WECC and NERC, and public comment on, the impact of removing the tuning
requirement.
---------------------------------------------------------------------------

    \59\ Id. Requirement WR1 of the currently-effective regional
Reliability Standard provides: ``Power System Stabilizers on
generators shall be kept in service at all times, unless one of the
exemptions listed in Section C (Measures) applies, and shall be
properly tuned in accordance with WECC requirements.''
---------------------------------------------------------------------------

    86. This highlights another concern. Currently, no NERC Reliability
Standard addresses power system stabilizer tuning. As explained above,
a properly tuned power system stabilizer is necessary to enhance system
damping. If a power system stabilizer is installed, periodic review of
the power system stabilizer tuning is a significant component of
maintaining system stability to ensure that system changes have not
impacted the performance of the power system stabilizer in supporting
system stability. Accordingly, the Commission seeks comment on whether
it should propose to direct the ERO to develop a continent-wide
Reliability Standard to address this concern. In particular, we seek
comment on directing the ERO to develop a Reliability Standard with the
purpose of ensuring that, if a power system stabilizer is installed,
the power system stabilizer must be properly tuned for operation. Such
a Reliability Standard would not require installation of a power system
stabilizer, but would ensure that power system stabilizer that are in
service would need to be tuned prior to service and the settings must
be reviewed periodically to ensure the power system stabilizer operates
properly to support the reliability of the Bulk-Power System. The
Commission's concerns regarding the NERC Reliability Standard are
introduced here as they correspond with certain elements of the WECC
standards that are the subject of the immediate proceeding. However,
any proposal to direct the development of modifications to the NERC
Reliability Standards would be addressed in a separate proceeding.
Summary
    87. The Commission proposes to approve VAR-501-WECC-1 as just,
reasonable, not unduly discriminatory or preferential, and in the
public interest. Further, the Commission proposes the concurrent
retirement of currently-effective WECC VAR-STD-002b-1. In addition, the
Commission requests comment on issues discussed above regarding whether
the Commission should direct WECC to develop modifications to the
proposed regional Reliability Standard that would: (1) Replace the
blanket two percent exemption with a list of specific exemptions; and
(2) more narrowly tailor the exemption for any synchronous generator or
synchronous conductor that operates less than five percent of all
operating hours during any calendar quarter. The Commission also seeks
comment on the historical replacement period for nuclear and non-
nuclear units and whether the Commission should direct WECC to modify
the regional Reliability Standard to limit the acceptable duration of
power system stabilizer outages. Finally, the Commission seeks comment
on whether it should propose to direct the ERO to develop a continent-
wide Reliability Standard that ensures that, if a power system
stabilizer is installed, the power system stabilizer must be properly
tuned for operation.

IV. Information Collection Statement

    88. The Office of Management and Budget (OMB) regulations require
that OMB approve certain reporting and recordkeeping (collections of
information) imposed by an agency. The information contained here is
also subject to review under section 3507(d) of the Paperwork Reduction
Act of 1995. As stated above, the Commission previously approved the
current regional Reliability Standards that are proposed for
replacement in this rulemaking. In the event that the Commission, after
receiving comments, determines to adopt the four proposed Reliability
Standards, they would not substantially change the entities' current
reporting burdens under the five currently effective, approved
Reliability Standards.
    89. The four proposed WECC regional Reliability Standards (and the
five currently approved regional Reliability Standards they are
intended to replace) are designated as: FAC-501-WECC-1 (Transmission
Maintenance; to replace approved PRC-STD-005-1); PRC-004-WECC-1
(Protection System and Remedial Action Scheme Misoperation; to replace
approved WECC PRC-STD-001-1 and PRC-STD-003-1); VAR-002-WECC-1
(Automatic Voltage Regulators; to replace approved WECC VAR-STD-002a-
1); and VAR-501-WECC-1 (Power System Stabilizer; to replace approved
WECC VAR-STD-002b-1). The proposed standards do not modify or otherwise
affect the burdens related to the collection of information already in
place. Thus, the proposed replacement Reliability Standards will
neither increase the reporting burden nor impose any additional
information collection requirements.
    Burden Estimate: The Commission does not foresee any additional
impact on the reporting burden for small businesses, because the
proposed modifications do not increase the existing burdens. However,
we will submit this proposed rule to OMB for review.
    Title: Version One Regional Reliability Standard for Facilities
Design, Connections, and Maintenance; Protection and Control; and
Voltage and Reactive.
    Action: Proposed Collection FERC-725E.
    OMB Control No.: 1902-0246.

    Respondents: Businesses or other for-profit institutions; not-for-
profit institutions.
    Frequency of Responses: On occasion.
    Necessity of the Information: This proposed rule proposes to
approve four requested replacements (to five existing approved regional
Reliability Standards). The proposed regional Reliability Standards
help ensure the reliable operation of the Western Interconnection.
    Internal Review: The Commission proposes to approve FAC-501-WECC-1,
PRC-004-WECC-1, VAR-002-WECC-1, and VAR-501-WECC-1 as just, reasonable,
not unduly discriminatory or preferential, and in the public interest.
In addition, under section 215(d)(5) of the FPA and section 39.5(f) of
our regulations, the Commission proposes to direct the ERO to develop
certain modifications to further clarify the requirements of the
proposed WECC regional Reliability Standards.
    90. Interested persons may obtain information on the reporting
requirements by contacting the following: Federal Energy Regulatory
Commission, 888 First Street, NE., Washington, DC 20426 [Attention:
Ellen Brown, Office of the Executive Director, e-mail:
<EMAIL_ADDRESS>Phone:<PHONE_NUMBER>, fax:<PHONE_NUMBER>].
    91. For submitting comments concerning the collection(s) of
information and the associated burden estimate(s), please send your
comments to the Commission and to the Office of Management and Budget,
Office of Information and Regulatory Affairs, Washington, DC 20503
[Attention: Desk Officer for the Federal Energy Regulatory Commission,
phone<PHONE_NUMBER>, fax:<PHONE_NUMBER>]. For security reasons,
comments to OMB should be submitted by e-mail to<EMAIL_ADDRESS>Comments submitted to OMB should include Docket
Number RM09-14 and OMB Control Number 1902-0246.

V. Environmental Analysis

    92. The Commission is required to prepare an Environmental
Assessment or an Environmental Impact Statement for any action that may
have a significant adverse effect on the human environment.\60\ The
Commission has categorically excluded certain actions from this
requirement as not having a significant effect on the human
environment. Included in the exclusion are rules that are clarifying,
corrective, or procedural or that do not substantially change the
effect of the regulations being amended.\61\ The actions proposed
herein fall within this categorical exclusion in the Commission's
regulations.
---------------------------------------------------------------------------

    \60\ Regulations Implementing the National Environmental Policy
Act of 1969, Order No. 486, FERC Stats. & Regs. ] 30,783 (1987).
    \61\ 18 CFR 380.4(a)(2)(ii).
---------------------------------------------------------------------------

VI. Regulatory Flexibility Act Certification

    93. The Regulatory Flexibility Act of 1980 (RFA) \62\ generally
requires a description and analysis of final rules that will have
significant economic impact on a substantial number of small entities.
The RFA mandates consideration of regulatory alternatives that
accomplish the stated objectives of a proposed rule and that minimize
any significant economic impact on a substantial number of small
entities. The Small Business Administration's (SBA) Office of Size
Standards develops the numerical definition of a small business.\63\
The SBA has established a size standard for electric utilities, stating
that a firm is small if, including its affiliates, it is primarily
engaged in the transmission, generation and/or distribution of electric
energy for sale and its total electric output for the preceding twelve
months did not exceed four million megawatt hours.\64\ The RFA is not
implicated by this proposed rule because the modification discussed
herein will not have a significant economic impact on a substantial
number of small entities. Moreover, the proposed Reliability Standards
reflect a continuation of existing requirements for these reliability
entities. Accordingly, no regulatory flexibility analysis is required.
---------------------------------------------------------------------------

    \62\ 5 U.S.C. 601-612.
    \63\ 13 CFR 121.101.
    \64\ 13 CFR 121.201, Sector 22, Utilities & n. 1.
---------------------------------------------------------------------------

VII. Comment Procedures

    94. The Commission invites interested persons to submit comments on
the matters and issues proposed in this notice to be adopted, including
any related matters or alternative proposals that commenters may wish
to discuss. Comments are due February 22, 2011. Comments must refer to
Docket No. RM09-9-000, and must include the commenter's name, the
organization they represent, if applicable, and their address in their
comments.
    95. The Commission encourages comments to be filed electronically
via the eFiling link on the Commission's Web site at http://www.ferc.gov. The Commission accepts most standard word processing
formats. Documents created electronically using word processing
software should be filed in native applications or print-to-PDF format
and not in a scanned format. Commenters filing electronically do not
need to make a paper filing.
    96. Commenters unable to file comments electronically must mail or
hand-deliver an original copy of their comments to: Federal Energy
Regulatory Commission, Secretary of the Commission, 888 First Street,
NE., Washington, DC 20426. These requirements can be found on the
Commission's Web site, see, e.g., the ``Quick Reference Guide for Paper
Submissions,'' available at http://www.ferc.gov/docs-filing/efiling.asp
or via phone from FERC Online Support at<PHONE_NUMBER> or toll-free at
1-866-208-3676.
    97. All comments will be placed in the Commission's public files
and may be viewed, printed, or downloaded remotely as described in the
Document Availability section below. Commenters on this proposal are
not required to serve copies of their comments on other commenters.

VIII. Document Availability

    98. In addition to publishing the full text of this document in the
Federal Register, the Commission provides all interested persons an
opportunity to view and/or print the contents of this document via the
Internet through FERC's Home Page (http://www.ferc.gov) and in FERC's
Public Reference Room during normal business hours (8:30 a.m. to 5 p.m.
Eastern time) at 888 First Street, NE., Room 2A, Washington, DC 20426.
    99. From FERC's Home Page on the Internet, this information is
available on eLibrary. The full text of this document is available on
eLibrary in PDF and Microsoft Word format for viewing, printing, and/or
downloading. To access this document in eLibrary, type the docket
number excluding the last three digits of this document in the docket
number field.
    100. User assistance is available for eLibrary and the FERC's Web
site during normal business hours from FERC Online Support at (202)
502-6652 (toll free at 1-866-208-3676) or e-mail at
<EMAIL_ADDRESS>or the Public Reference Room at (202) 502-
8371, TTY<PHONE_NUMBER>. E-mail the Public Reference Room at
<EMAIL_ADDRESS>
    By direction of the Commission.

Kimberly D. Bose,
Secretary.
[FR Doc. 2010-32157 Filed 12-21-10; 8:45 am]
BILLING CODE 6717-01-P