PAPERWORK REDUCTION ACT SUBMISSION Please read the instructions before completing this form. For additional forms or assistance in completing this form, contact your agency's Paperwork Clearance Officer. Send two copies of this form, the collection instrument to be reviewed, the Supporting Statement and any additional documentation to: Office of Information and Regulatory Affairs, Office of Management and Budget, Docket Library, Room 10102, 725 17th Street NW Washington, DC 20503.

1. Agency/ Subagency originating request EPA/ OAR/ OAP/ CPPD 2. OMB control number b. X None a__ __ __ __  __ __ __ __ _ 2 _ 0_ 6 _ 0_ __

3. Type of information collection ( check one) a. x New collection b. G Revision of a currently approved collection c. G Extension of a currently approved collection d. G Reinstatement, without change, of a previously approved collection for which approval has expired e. G Reinstatement, with change, of a previously approved collection for which approval has expired f. G Existing collection in use without an OMB control number 4. Type of review requested ( check one) a. x Regular b. G Emergency  Approval requested by: / / c. G Delegated 5. Small entities Will this information collection have a significant economic impact on a substantial number of small entities? G Yes X No For b f, note item A2 of Supporting Statement Instructions 6. Requested expiration date a. x Three years from approval date b. G Other Specify: / /___

7. Title Reporting Requirements under EPA's Climate Leaders Program 8. Agency form number( s) 2100.01 9. Keywords Climate Change Voluntary Program 10. Abstract EPA has developed this ICR to ensure that the new voluntary program " Climate Leaders" is able to obtain greenhouse gas emissions data from companies that choose to participate in the program. EPA will develop reporting forms and a letter of intent for companies to submit. Larger companies will join Climate Leaders, and therefore the impact of this program on small businesses is limited.

11. Affected public ( Mark primary with " P" and all others that apply with " X") a. Individuals or households d. Farms b. P Business or other for profit e. Federal Government c. Not for profit institutions f. State, Local or Tribal Government 12. Obligation to respond ( Mark primary with " P" and all others that apply with " X") a. P Voluntary b. G Required to obtain or retain benefits c. G Mandatory 13. Annual reporting and recordkeeping hour burden a. Number of respondents 70 b. Total annual responses 70 1. Percentage of these responses collected electronically 80 % c. Total hours requested 5,114 d. Current OMB inventory 0 e. Difference 5,114 f. Explanation of difference 1. Program Change 5,114 2. Adjustment 0 14. Annual reporting and recordkeeping cost burden ( in thousands of dollars) a. Total annualized capital/ startup costs $ 6 b. Total annual costs ( O& M) 0 c. Total annualized cost requested $ 6 d. Current OMB inventory 0 e. Difference $ 6 f. Explanation of difference 1. Program change $ 6 2. Adjustment 0 15. Purpose of information collection ( Mark Primary With " P" and all others that apply with " X") a. __ Application for benefits e. __ Program planning or management b. P Program evaluation f. __ Research c. __ General purpose statistics g. __ Regulatory or compliance d. __ Audit 16. Frequency of recordkeeping or reporting ( check all that apply) a. Q Recordkeeping b. Q Third party disclosure c. X Reporting 1. Q On occasion 2. Q Weekly 3. Q Monthly 4. Q Quarterly 5. Q Semi annually 6. X Annually 7. Q Biannually 8. Q Other ( describe)

17. Statistical methods Does this information collection employ statistical methods?

Q Yes X No 18. Agency contact ( person who can best answer questions regarding the content of this submission) Name: Tom Kerr Phone: 202 564 0047 OMB 83 I 10/ 95 19. Certification for Paperwork Reduction Act Submissions On behalf of this Federal agency, 1 certify that the collection of information encompassed by this request complies with' 5 CFR 1320.9.

NOTE: The text of 5 CFR 1320.9, and the related provisions of 5 CFR 1320.8( b)( 3), appear at the end of the instructions. The certification is to be made with reference to those regulatory provisions as set forth in the instructions.

The following is a summary of the topics, regarding the proposed collection of information, that the certification covers:

( a) It is necessary for the proper performance of agency functions;

( b) It avoids unnecessary duplication;

( c) It reduces burden on small entities;

( d) It uses plain, coherent, and unambiguous terminology that is understandable to respondents;

( e) Its implementation will be consistent and compatible with current reporting and recordkeeping practices;

( f) It indicates the retention periods for recordkeeping requirements;

( g) It informs respondents of the information called for under 5 CFR 1320.8( b)( 3): ( I) Why the information is being collected' ( ii) Use of information; ( iii) Burden estimate; ( iv) Nature of response ( voluntary, required for a benefit, or mandatory); ( v) Nature and extent of confidentiality; and ( vi) Need to display currently valid OMB control number;

( h) It was developed by an office that has planned and allocated resources for the efficient and effective management and use of the information to be collected ( see note in Item 19 of the instructions);

( I) It uses effective and efficient statistical survey methodology; and ( j) It makes appropriate use of information technology.

If you are unable to certify compliance with any of these provisions, identify the item below and explain the reason in Item 18 of the Supporting Statement.

Signature of Program Official Kathleen Hogan, Director, Climate Protection Partnerships Division Date Signature of Senior Official or designee Oscar Morales, Director Collection Strategies Division Office of Environmental Information Date OMB 83 I 10/ 95


[Federal Register Volume 76, Number 205 (Monday, October 24, 2011)]
[Notices]
[Page 65718]
[FR Doc No: 2011-27317]

-----------------------------------------------------------------------

DEPARTMENT OF ENERGY

Federal Energy Regulatory Commission

[Docket No. ER12-60-000]

Tenaska Power Management, LLC; Supplemental Notice That Initial
Market-Based Rate Filing Includes Request for Blanket Section 204
Authorization

    This is a supplemental notice in the above-referenced proceeding of
Tenaska Power Management, LLC's application for market-based rate
authority, with an accompanying rate tariff, noting that such
application includes a request for blanket authorization, under 18 CFR
part 34, of future issuances of securities and assumptions of
liability.
    Any person desiring to intervene or to protest should file with the
Federal Energy Regulatory Commission, 888 First Street, NE.,
Washington, DC 20426, in accordance with Rules 211 and 214 of the
Commission's Rules of Practice and Procedure (18 CFR 385.211 and
385.214). Anyone filing a motion to intervene or protest must serve a
copy of that document on the Applicant.
    Notice is hereby given that the deadline for filing protests with
regard to the applicant's request for blanket authorization, under 18
CFR part 34, of future issuances of securities and assumptions of
liability, is November 1, 2011.
    The Commission encourages electronic submission of protests and
interventions in lieu of paper, using the FERC Online links at http://www.ferc.gov. To facilitate electronic service, persons with Internet
access who will eFile a document and/or be listed as a contact for an
intervenor must create and validate an eRegistration account using the
eRegistration link. Select the eFiling link to log on and submit the
intervention or protests.
    Persons unable to file electronically should submit an original and
14 copies of the intervention or protest to the Federal Energy
Regulatory Commission, 888 First Street, NE., Washington, DC 20426.
    The filings in the above-referenced proceeding are accessible in
the Commission's eLibrary system by clicking on the appropriate link in
the above list. They are also available for review in the Commission's
Public Reference Room in Washington, DC. There is an eSubscription link
on the Web site that enables subscribers to receive e-mail notification
when a document is added to a subscribed dockets(s). For assistance
with any FERC Online service, please e-mail<EMAIL_ADDRESS>
or call<PHONE_NUMBER> (toll free). For TTY, call<PHONE_NUMBER>.

    Dated: October 17, 2011.
Nathaniel J. Davis, Sr.,
Deputy Secretary.
[FR Doc. 2011-27317 Filed 10-21-11; 8:45 am]
BILLING CODE 6717-01-P


[Federal Register: May 6, 2010 (Volume 75, Number 87)]
[Notices]
[Page 25013-25014]
[DOCID:fr06my10-109]

-----------------------------------------------------------------------

SECURITIES AND EXCHANGE COMMISSION

[Release No. 34-62004; File No. SR-NYSEArca-2010-27]

Self-Regulatory Organizations; NYSE Arca, Inc.; Notice of Filing
and Immediate Effectiveness of Proposed Rule Change Amending Its Mid-
Point Passive Liquidity Order

April 29, 2010.
    Pursuant to Section 19(b)(1) \1\ of the Securities Exchange Act of
1934 (the ``Act'') \2\ and Rule 19b-4 thereunder,\3\ notice is hereby
given that, on April 21, 2010, NYSE Arca, Inc. (``NYSE Arca'' or the
``Exchange'') filed with the Securities and Exchange Commission (the
``Commission'') the proposed rule change as described in Items I, II,
and III below, which Items have been prepared by the self-regulatory
organization. The Commission is publishing this notice to solicit
comments on the proposed rule change from interested persons.
---------------------------------------------------------------------------

    \1\ 15 U.S.C. 78s(b)(1).
    \2\ 15 U.S.C. 78a.
    \3\ 17 CFR 240.19b-4.
---------------------------------------------------------------------------

I. Self-Regulatory Organization's Statement of the Terms of Substance
of the Proposed Rule Change

    The Exchange proposes to amend the operation of its Mid-Point
Passive Liquidity Order (``MPL Order''). The text of the proposed rule
change is available on the Exchange's Web site at http://www.nyse.com,
at the Exchange's principal office, on the Commission's Web site at
http://www.sec.gov and at the Commission's Public Reference Room.

II. Self-Regulatory Organization's Statement of the Purpose of, and
Statutory Basis for, the Proposed Rule Change

    In its filing with the Commission, the self-regulatory organization
included statements concerning the purpose of, and basis for, the
proposed rule change and discussed any comments it received on the
proposed rule change. The text

of those statements may be examined at the places specified in Item IV
below. The Exchange has prepared summaries, set forth in sections A, B,
and C below, of the most significant parts of such statements.

A. Self-Regulatory Organization's Statement of the Purpose of, and the
Statutory Basis for, the Proposed Rule Change

1. Purpose
    Currently, pursuant to NYSE Arca Equities Rule 7.31(h)(5), when the
market is locked, an MPL Order will trade at the locked price, but
where the market is crossed, the MPL Order will wait for the market to
uncross before becoming eligible to trade again. By this proposal, the
Exchange seeks to have MPL Orders wait to execute while the market is
locked, before becoming eligible to trade again when the market is no
longer locked. The Exchange believes that this change, based on
feedback from customers, is a minor adjustment to an existing order
type.
2. Statutory Basis
    The proposed rule change is consistent with Section 6(b) \4\ of the
Securities Exchange Act of 1934 (the ``Act''), in general, and furthers
the objectives of Section 6(b)(5) \5\ in particular in that it is
designed to prevent fraudulent and manipulative acts and practices, to
promote just and equitable principles of trade, to foster cooperation
and coordination with persons engaged in facilitating transactions in
securities, and to remove impediments to and perfect the mechanism of a
free and open market and a national market system. Specifically, the
proposed rule change is a minor adjustment to an existing order type.
---------------------------------------------------------------------------

    \4\ 15 U.S.C. 78f(b).
    \5\ 15 U.S.C. 78f(b)(5).
---------------------------------------------------------------------------

B. Self-Regulatory Organization's Statement on Burden on Competition

    The Exchange does not believe that the proposed rule change will
impose any burden on competition that is not necessary or appropriate
in furtherance of the purposes of the Act.

C. Self-Regulatory Organization's Statement on Comments on the Proposed
Rule Change Received From Members, Participants, or Others

    No written comments were solicited or received with respect to the
proposed rule change.

III. Date of Effectiveness of the Proposed Rule Change and Timing for
Commission Action

    The Exchange has filed the proposed rule change pursuant to Section
19(b)(3)(A)(iii) of the Act \6\ and Rule 19b-4(f)(6) thereunder.\7\
Because the proposed rule change does not: (i) Significantly affect the
protection of investors or the public interest; (ii) impose any
significant burden on competition; and (iii) become operative prior to
30 days from the date on which it was filed, or such shorter time as
the Commission may designate, if consistent with the protection of
investors and the public interest, the proposed rule change has become
effective pursuant to Section 19(b)(3)(A) of the Act \8\ and Rule 19b-
4(f)(6)(iii) thereunder.\9\
---------------------------------------------------------------------------

    \6\ 15 U.S.C. 78s(b)(3)(A)(iii).
    \7\ 17 CFR 240.19b-4(f)(6).
    \8\ 15 U.S.C. 78s(b)(3)(A).
    \9\ 17 CFR 240.19b-4(f)(6). In addition, Rule 19b-4(f)(6)(iii)
requires the Exchange to give the Commission written notice of the
Exchange's intent to file the proposed rule change along with a
brief description and text of the proposed rule change, at least
five business days prior to the date of filing of the proposed rule
change, or such shorter time as designated by the Commission. The
Exchange has satisfied the pre-filing requirement.
---------------------------------------------------------------------------

    At any time within 60 days of the filing of the proposed rule
change, the Commission may summarily abrogate such rule change if it
appears to the Commission that such action is necessary or appropriate
in the public interest, for the protection of investors, or otherwise
in furtherance of the purposes of the Act.

IV. Solicitation of Comments

    Interested persons are invited to submit written data, views, and
arguments concerning the foregoing, including whether the proposed rule
change is consistent with the Act. Comments may be submitted by any of
the following methods:

Electronic Comments

     Use the Commission's Internet comment form (http://
www.sec.gov/rules/sro.shtml); or
     Send an e-mail to<EMAIL_ADDRESS>Please include
File Number SR-NYSEArca-2010-27 on the subject line.

Paper Comments

     Send paper comments in triplicate to Elizabeth M. Murphy,
Secretary, Securities and Exchange Commission, 100 F Street, NE.,
Washington, DC 20549-1090.

All submissions should refer to File Number SR-NYSEArca-2010-27. This
file number should be included on the subject line if e-mail is used.
To help the Commission process and review your comments more
efficiently, please use only one method. The Commission will post all
comments on the Commission's Internet Web site (http://www.sec.gov/
rules/sro.shtml). Copies of the submission, all subsequent amendments,
all written statements with respect to the proposed rule change that
are filed with the Commission, and all written communications relating
to the proposed rule change between the Commission and any person,
other than those that may be withheld from the public in accordance
with the provisions of 5 U.S.C. 552, will be available for Web site
viewing and printing in the Commission's Public Reference Section, 100
F Street, NE., Washington, DC 20549-1090 on official business days
between the hours of 10 a.m. and 3 p.m. Copies of the filing will also
be available for inspection and copying at NYSE Arca's principal office
and on its Internet Web site at http://www.nyse.com. All comments
received will be posted without change; the Commission does not edit
personal identifying information from submissions. You should submit
only information that you wish to make available publicly. All
submissions should refer to File Number SR-NYSEArca-2010-27 and should
be submitted on or before May 27, 2010.
---------------------------------------------------------------------------

    \10\ 17 CFR 200.30-3(a)(12).

    For the Commission, by the Division of Trading and Markets,
pursuant to delegated authority.\10\
Florence E. Harmon,
Deputy Secretary.
[FR Doc. 2010-10599 Filed 5-5-10; 8:45 am]
BILLING CODE 8011-01-P


[Federal Register: September 13, 2006 (Volume 71, Number 177)]
[Notices]
[Page 54043]
[DOCID:fr13se06-64]

-----------------------------------------------------------------------

DEPARTMENT OF ENERGY

Federal Energy Regulatory Commission

[Docket No. CP06-433-000]

Northern Natural Gas Company; Notice of Application

September 6, 2006.
    Take notice that on August 29, 2006, Northern Natural Gas Company
(Northern), 1111 South 103rd Street, Omaha, Nebraska 68124, filed in
Docket No. CP06-433-000, an application pursuant to sections 7 (b) and
(c) of the Natural Gas Act (NGA) and Part 157 of the Commission's
Regulations, for authorization to: (1) Construct, modify and operate
certain compression, pipeline, and town border station (TBS)
facilities, with appurtenances all located in various counties in Iowa,
Nebraska and South Dakota; and (2) abandon certain compression
facilities in Clay County, Kansas, in order to expand the capacity of
Northern's West Leg pipeline segment of its Market Area facilities, all
as more fully set forth in the application which is on file with the
Commission and open to public inspection. This filing is accessible on-
line at http://www.ferc.gov, using the ``eLibrary'' link and is

available for review in the Commission's Public Reference Room in
Washington, DC. There is an ``eSubscription'' link on the Web site that
enables subscribers to receive e-mail notification when a document is
added to a subscribed docket(s). For assistance with any FERC Online
service, please e-mail<EMAIL_ADDRESS>or call (866) 208-
3676 (toll free). For TTY, call<PHONE_NUMBER>.
    In its application, Northern asserts that the installation of the
proposed facilities will provide approximately 32,100 Dth/day of
incremental peak day entitlement that has been subscribed to by its
customers. Northern also states that the facilities proposed will
result in capacity greater than currently subscribed by its customers
and that any excess capacity created will be posted on Northern's Web
site as generally available and offered to shippers on a
nondiscriminatory basis. Northern further states that the proposal
herein is a result of an analysis conducted following Open Seasons
soliciting interest for an expansion project in its Market Area that
would be effective beginning November 1, 2007. In addition, Northern is
requesting approval for rolled-in rate treatment of the expansion
costs. The facilities proposed constitute the second discrete stand-
alone project under the umbrella of the Northern Lights expansion
project.\1\ The estimated capital cost for the facilities proposed
herein is $8,083,331.
---------------------------------------------------------------------------

    \1\ Northern Lights is a multi-year commitment to expand
Northern's Market Area capacity in response to its customer's future
requirements through 2026. On June 23, 2006, Northern filed an
application with the Commission under Docket No. CP06-403-000
requesting authorization to construct, modify and operate facilities
for the first discrete stand-alone Northern Lights project.
---------------------------------------------------------------------------

    Any questions regarding this application should be directed to
Michael T. Loeffler, Director, Certificates and Government Affairs for
Northern, 1111 South 103rd Street, Omaha, Nebraska 68124, at (402) 398-
7103 or Donna Martens, Senior Regulatory Analyst, at<PHONE_NUMBER>.
    There are two ways to become involved in the Commission's review of
this project. First, any person wishing to obtain legal status by
becoming a party to the proceedings for this project should, on or
before the comment date stated below, file with the Federal Energy
Regulatory Commission, 888 First Street, NE., Washington, DC 20426, a
motion to intervene in accordance with the requirements of the
Commission's Rules of Practice and Procedure (18 CFR 385.214 or
385.211) and the Regulations under the NGA (18 CFR 157.10). A person
obtaining party status will be placed on the service list maintained by
the Secretary of the Commission and will receive copies of all
documents filed by the applicant and by all other parties. A party must
submit 14 copies of filings made with the Commission and must mail a
copy to the applicant and to every other party in the proceeding. Only
parties to the proceeding can ask for court review of Commission orders
in the proceeding.
    However, a person does not have to intervene in order to have
comments considered. The second way to participate is by filing with
the Secretary of the Commission, as soon as possible, an original and
two copies of comments in support of or in opposition to this project.
The Commission will consider these comments in determining the
appropriate action to be taken, but the filing of a comment alone will
not serve to make the filer a party to the proceeding. The Commission's
rules require that persons filing comments in opposition to the project
provide copies of their protests only to the party or parties directly
involved in the protest.
    Persons who wish to comment only on the environmental review of
this project should submit an original and two copies of their comments
to the Secretary of the Commission. Environmental commentors will be
placed on the Commission's environmental mailing list, will receive
copies of the environmental documents, and will be notified of meetings
associated with the Commission's environmental review process.
Environmental commentors will not be required to serve copies of filed
documents on all other parties. However, the non-party commentors will
not receive copies of all documents filed by other parties or issued by
the Commission (except for the mailing of environmental documents
issued by the Commission) and will not have the right to seek court
review of the Commission's final order.
    Comments, protests and interventions may be filed electronically
via the Internet in lieu of paper. See 18 CFR 385.2001(a) (1) (iii) and
the instructions on the Commission's web site under the ``e-Filing''
link at http://www.ferc.gov. The Commission strongly encourages

intervenors to file electronically. Persons unable to file
electronically should submit an original and 14 copies of the protest
or intervention to the Federal Energy Regulatory Commission, 888 First
Street, NE., Washington, DC 20426.
    Comment Date: September 27, 2006.

Magalie R. Salas,
Secretary.
[FR Doc. E6-15169 Filed 9-12-06; 8:45 am]

BILLING CODE 6717-01-P


ÿWPCw7
øgç…
¦§mYÄ™‚ü<¿…†U	mš•r\Yxðã¸èa„B™Ì|~Î·šÜ.ép¬(/[Í¤.ìQÜþ<|ï’Ñ7½œF—?oÌ/ÖÂVîÓ#?§(Æë“¤©Ikçœ5ŸíŸÛÔ¼½áÂ¢Tã(4s”¼f1»q@éâ¾Îá6æ"c
o2„µ§RÕ÷
~³Z›/lPerçHÑ;Ö›ºõt³Üg‚–cÄ¾˜¨½Æ;T2N=7g•"ÃÜè_”Ua'¼Ï¿\ƒŠB
	,I
œáÊÀÎ.yú<ÜË§¼‘’¬–|v&S.À…#>1CY±íGý¨ÒìVÌ#GÝ¯Æe9ÊÄƒ§îtP”¯ LŽMGD,-Ò¯iúÞêùdåV/”µ-øe9Ë
3I(ËâúB)+xµ‰^‰«ŒR®RíK¶l<{`.Óä‚1ÍžÔ.S/…&¦Üñ+‰ú±lOµªPK$Ç÷bõÞõŒ¦ÿ#.h³)eæ{HòN5@dÔ…¬UÖ4Ãe“Î<‹8‰†Ygº¬ŒÿÜ+¢ÇPÚº¡Û¹2:°©†5´kÁpU¨úâw–yÁ9CTÊ«ä¯_XÅµN=ª\²h”Ê4ür^àjQÝ´;°‘ZÌ/ÔU>˜
~Ö
0¾T0p0p‚0pò0pb0pÒ0pB0p²0p"0<’0VÎ0V$0Vz0tÐ0ùD0ˆ=0óÅ0í¸0–¥0R;0Ñ0„^0Žâ0*p		Bš	B·	BÔ	Bñ	D3
	CA
	D!+[
0š†
0j 0œŠ0‹& 0‹± 0¾<!0Žú!fˆ"aŠ"	Bž"	B»"	BØ"	Bõ"	B#	B/#	BL#	Bi#	B†#	B£#	BÀ#	BÝ#	Bú#	B$	B4$	BQ$	Bn$	B‹$	B¨$	BÅ$	Bâ$	Bÿ$	B	%	B9%	BV%	Bs%	B%	B%	BÊ%	Bç%	B&	B!&	B>&	B[&	Bx&	B•&	B²&	BÏ&	Bì&	B	'	B&'	BC'	B`'	B}'	Bš'	B·'	BÔ'	Bñ'	B(	B+(	BH(	Be(	B‚(	BŸ(	B¼(	BÙ(	Bö(	B)	B0)	BM)	Bj)	B‡)	B¤)	BÁ)	BÞ)	Bû)	B*	B5*	BR*	Bo*	BŒ*	B©*	BÆ*	Bã*	B+	B+	B:+	BW+	Bt+	B‘+	B®+	BË+	Bè+	B,	B",	B?,	B\,	By,	B–,	B³,	BÐ,	Bí,	B
-	B'-	BD-	Ba-	B~-	B›-	B¸-	BÕ-	Bò-	B.	B,.	BI.	Bf.	Bƒ.	B .	B½.	BÚ.	B÷.	B/	B1/	BN/^k/	Bw/	B”/	B±/	BÎ/	Bë/U,0	B40	BQ0	Bn0	B‹0	B¨0	BÅ0	Bâ0	Bÿ0	B	1	B91	BV1	Bs1	B1	B1	BÊ1	Bç1	B2	B!2	B>2	B[2	Bx2	B•2	B²2	BÏ2	Bì2	B	3	B&3	BC3	B`3	B}3	Bš3	B·3	BÔ3	Bñ3	B4	B+4	BH4e40Žu4#Á5UNÄ6	%7M7(	7ND7wF74J7^7	m`7ô\		`‹&Times New Roman'December 19 Meeting
EPA0EPA
.

6D
7ÿÿ4Heading 1Ó
ÈÓÔ€XXXÔòòÓÓÔ

ÔÔ

ÔÓÓóóÓ
ÈÓÔ€XXXÔ6
ÿÿ4Heading 2Ó
ÈÓÔ

ÔÔ

ÔÓ
ÈÓ6
ÿÿ4Heading 3Ó
ÈÓÔ

ÔÔ

ÔÓ
ÈÓ6
ÿÿ4Heading 4Ó
ÈÓÔ

ÔÔ

ÔÓ
ÈÓ6
ÿÿ4Heading 5Ó
ÈÓÔ

ÔÔ

ÔÓ
ÈÓ6
ÿÿ4Heading 6Ó
ÈÓÔ

ÔÔ

ÔÓ
ÈÓ6
ÿÿ4Heading 7Ó
ÈÓÔ

ÔÔ

ÔÓ
ÈÓ6
ÿÿ4Heading 8Ó
ÈÓÔ

ÔÔ

ÔÓ
ÈÓ6
ÿÿ4Heading 9Ó
ÈÓÔ

ÔÔ

ÔÓ
ÈÓ<ÿÿ:Default Para6ÿÿ4Body TextÓ
ÈÓÓ
ÈÓ:ÿÿ8Body Text 2ÓÓÓÓ:ÿÿ8Body Text 3Ó€ÓÓÓ<		ÿÿ:Body Text F1Ó
ÈÓÓXÓÓ
ÈÓÓXÓ<]`ÿÿ:Body Text I2Ó
ÈÓÓXÓÓ
XÓÓ5+
`	¸hÀpÈ 	x
Ð 5ÓÓÓÓ
ÓÓ8.°°`	¸hÀpÈ 	x
Ð (#8ÓÓ
ÈÓ<&&ÿÿ:Body Text FiÓXÓÓ
XÓÓÓÓ
ÓÓÓÓXÓ<W`ÿÿ:Body Text I1Ó
ÈÓÓ°ÓÓ
°ÓÓ/%`	`	`	¸hÀpÈ 	x
/ÓÓÓÓ
ÓÓ8.°°`	¸hÀpÈ 	x
Ð (#8ÓÓ
ÈÓ<Q`ÿÿ:Body Text InÓ
ÈÓÓÓÓ
ÓÓ)¸	¸¸hÀpÈ 	)ÓÓÓÓ
ÓÓ8.°°`	¸hÀpÈ 	x
Ð (#8ÓÓ
ÈÓ2 Dÿÿ0ClosingÓhÓÓ
(#ÓÓÓÓ8.°°`	¸hÀpÈ 	x
Ð (#8Ó<ÿÿ:E-mail SignaÓÓÓÓ<FOÿÿ:Envelope AddÓ`	ÓÓÓÓ/%hÀpÈ 	x
Ð (#/ÓÓÓÓÓÓ8.°°`	¸hÀpÈ 	x
Ð (#8Ó<$$ÿÿ:Envelope RetÔ€ôôôÔÓÓÓÓÔ€XXXÔ<))ÿÿ:Footnote TexÓ
8šdÓÔ€ôôôÔÔ€XXXÔÓ
8šdÓ<wwÿÿ:Message HeadÓ7€ (€X7ÓÓÓÓ5+°
°`	¸hÀpÈ 	x
Ð 5ÓÓ7€!(€X7ÓÓÓÓ5+°
°`	¸hÀpÈ 	x
Ð 5Ódddd
'ÿÿdxdÿÿÿÿÿd'dxd6 Dÿÿ4SignatureÓhÓÓ
(#ÓÓÓÓ8.°°`	¸hÀpÈ 	x
Ð (#8Ó4ÿÿ2SubtitleÓ
ÈÓÓÓÓÓÓ
ÈÓ.77ÿÿ,TitleÓ
ð62ÓÔ€¼¼¼ÔòòÓÓÓÓÔ€XXXÔóóÓ
ð62Ó0Aÿÿ.HeaderÓ°°ÀÐ (#ÓÓA7°X°`	¸hÀpÈ 	x
Ð (#AÓ0Aÿÿ.FooterÓ°°ÀÐ (#ÓÓA7°X°`	¸hÀpÈ 	x
Ð (#AÓ</Sÿÿ:1 TOC - RICHÓ
ÈÓÔ-ÔÓ
°°(#ÓÓ8.°°`	¸hÀpÈ 	x
Ð (#8ÓÔ-ÔÓ
ÈÓ<8ÿÿ:1 Dot LeaderÓ°°x
Ð (#ÓÓ8.°°`	¸hÀpÈ 	x
Ð (#8ÓTable_AdddddddddddddddddddddddddddddddddddddddddddddddddddddddddddddddddddddddddddddddddddddddddddddddddddddddddddddddddÂ{j/s	ddddd $‹Tahomaddddddddddddddddddddddddddddddddddddd#|x(f•Á$¡¡Ô
..ÔÔÔÔÔÔ€ËX==XXËXÔÔ€X==XXËX==Ô˜\\US_EPA\pq_ccw_hp4050_6210bÈÈÈÈÈÈÈÈ0(Ö
Ã9	Z‹6Times New Roman RegularËX‰ŒW/llmineÿU‹ÿÀÀÀÝ
ƒÉ•Á!ÝÔ
..ÔÔÔÔÔÔ€ËX==XXËXÔÔ€X==XXËX==ÔÝÝÔ_ÔÔ€ôÙœòXX==ÔAs€of€12/16/02€1:15€p.m.Ð	° ÐÔ*’ƒ)*°ddd Xdd Xdd X°(#°(#’ÔÔ,þbZÔÔ,z
bbÔÔ+

ÔÐ>€+,-+o¿o¿ €€‚‚ƒƒ„@„……>ÐÓÓÓB.°°`	¸hÀpÈ 	x
Ð (#°œXBÓÔ€
òôÙœÔòòFuture€EPA€ELG€ProgramÐ	wÇ ÐMeeting€December€19,€2002,€10:30€a.m.Ð	©ù ÐÔ€ôÙœò
 ÔÐV€./G/Û+@

+,-		 €€‚‚ƒƒ„@„VÐÓK€!(€X¢òKÓÔ€¼H!»òôÙœÔName/AddressÐ
<EMAIL_ADDRESS>„@„?ÐE„mailÐS€34D,¢ò@

012 €€‚‚ƒƒ„@„SÐÔ€X==X»¼H!ÔóóÓK€!(€X¶	KÓGeoff€GrubbsÐ	¶	 ÐEPAÐ
?€567,!œ
ì@34 „@„?ÐÐS€89D,¶		@

567 €€‚‚ƒƒ„@„SÐÓK€!(€XŠÚKÓSheila€Ô_ÔFraceÔ_ÔÐ	ŠÚ
 ÐEPAÐ
?€:;<,!pÀ@89 „@„?ÐÐS€=>D,ŠÚ@

:;< €€‚‚ƒƒ„@„SÐÓK€!(€X^
®KÓTom€WallÐ	^
®
 ÐEPAÐ
?€?@A,!D”	@=> „@„?ÐÐS€BCD,^
®@

?@A €¹€‚‚ƒƒ„@„SÐÓK€!(€X2‚
KÓÐ
?€DEF,!2‚
@BC „@„?ÐÐS€GHD,2‚
@

¹DEF €€‚‚ƒƒ„@„SÐÓK€!(€Xë;KÓÔ_ÔFredricÔ_Ô€P.€Andes,€Esq.Ð	ë; ÐBarnes€&€Ô_ÔThornburgÔ_ÔÐ	Ñ!
 ÐÐ
?€IJK,!·@GH „<EMAIL_ADDRESS>S€LMD,ë;@

IJK €€‚‚ƒƒ„@„SÐÓK€!(€X¥õKÓJeffrey€S.€Ô_ÔLongsworthÔ_Ô,€Esq.Ð	¥õ ÐBarnes€&€Ô_ÔThornburgÔ_ÔÐ	‹Û ÐÐ
?€NOP,!qÁ@LM „<EMAIL_ADDRESS>S€QRD,¥õ@

NOP €€‚‚ƒƒ„@„SÐÓK€!(€X_¯KÓMs.€Ô_ÔKristyÔ_Ô€Ô_ÔBulleitÔ_Ô€Ð	_¯ ÐHunton€&€WilliamsÐ	E• ÐÐ
?€STU,!+{	@QR „<EMAIL_ADDRESS>S€VWD,_¯@

STU €€‚‚ƒƒ„@„SÐÓK€!(€XiKÓRoger€ClaffÐ	i
 ÐAmerican€Petroleum€InstituteÐ	ÿO ÐÔ_Ô(BringingÔ_Ô€Terry€Ô_ÔTwymanÔ_Ô,€Tom€Purcell€listedÐ	å5  Ðbelow)Ð	Ë! ÐÐ
?€XYZ,!±	"@VW „<EMAIL_ADDRESS>i# Ð€ÐS€[\D,ÿO$@

XYZ €€‚‚ƒƒ„@„SÐÓK€!(€XŸïKÓDavid€D.€Ô_ÔDunlapÔ_Ô,€DirectorÐ	Ÿï% ÐEnvironmental€Affairs€&€Information€TechnologyÐ	…
Õ& ÐUniform€and€Textile€Service€Association€(Ô_ÔUTSAÔ_Ô)Ð	k»' ÐÐ
?€]^_,!Q ¡(@[\ „<EMAIL_ADDRESS>S€`aD,Ÿï)@

]^_ €€‚‚ƒƒ„@„SÐÓK€!(€X?!		KÓAlexandra€Ô_ÔDapolitoÔ_Ô€DunnÐ	?!	* ÐGeneral€CounselÐ	%"u+ ÐAssociation€of€Metropolitan€Sewerage€AgenciesÐ	#[
, ÐÐ
?€bcd,!ñ#A-@`a „@„?Ðadunn@amsa„cleanwater.org,Ð	?!	. ÐSee€also:Ð	%"u/ ÐChris€HornbackÐS€efD,#[
0@

bcd €€‚‚ƒƒ„@„SÐÓK€!(€Xß$/
KÓMr.€Russ€Ô_ÔFurnariÔ_ÔÐ	ß$/ 1 ÐÔ_ÔPSEGÔ_ÔÐ	Å%!2 ÐNew€JerseyÐ	«&û!3 ÐÐ
?€ghi,!‘'á"4@ef „@„?ÐÐS€jkD,ß$/ 5@

ghi €€‚‚ƒƒ„@„SÐÓK€!(€X(Ï#KÓKaren€G.€HaynesÐ	(Ï#6 ÐÔ_ÔEquilonTechÔ_ÔÐ	e)µ$7 ÐÐ
?€lmn,!K*›%8@jk „<EMAIL_ADDRESS>S€opD,(Ï#9@

lmn €€‚‚ƒƒ„@„SÐÓK€!(€X9+‰&KÓMr.€Cliff€Ô_ÔHarvisonÔ_ÔÐ	9+‰&: ÐPresidentÐ	,o'; ÐNational€Tank€Truck€Carriers,€IncÐ	-U(< ÐÐ
?€qrs,!ë-;)=@op „@„?Ðâ

<EMAIL_ADDRESS>S€tuD,9+‰&>@

qrs €€‚‚ƒƒ„@„SÐÓK€!(€X÷
KÓChris€HornbackÐ	÷ Ðâ

âDirector,€Regulatory€Affairs€Ð	Ý	î ÐAssociation€of€Metropolitan€Sewerage€AgenciesÐ	Ã
Ô ÐÓÓ*€Bringing€1€person€from€his€staff€alsoÐ	©º ÐÐ
?€vwx,! @tu „<EMAIL_ADDRESS>S€yzD,÷@

vwx €€‚‚ƒƒ„@„SÐÓK€!(€X}
ŽKÓMr.€Mark€Ô_ÔKieserÔ_ÔÐ	}
Ž ÐSenior€ScientistÐ	ct ÐÔ_ÔKieserÔ_Ô€&€AssociatesÐ	IZ	 ÐÐ
?€{|},!/@
@yz „<EMAIL_ADDRESS>S€~D,}
Ž@

{|} €€‚‚ƒƒ„@„SÐÓK€!(€X.KÓMeg€McCarthyÐ	. ÐAmerican€Forest€&€Paper€AssociationÐ
 ÐCoordinator,€Regulatory€AffairsÐ	éú	 ÐÐ
?€€‚,!Ïà
@~ „<EMAIL_ADDRESS>S€ƒ„D,.@

€‚ €€‚‚ƒƒ„@„SÐÓK€!(€X½ÎKÓJennie€MeekeròòóóÐ	½Î ÐÔ_ÔCapitolinkÔ_Ô,€LLCÐ	£´ Ð(Attending€for€Mark€Ô_ÔDoppÔ_Ô€of€AMI)Ð	‰š
 ÐÐ
?€…†‡,!o€@ƒ„ „<EMAIL_ADDRESS>S€ˆ‰D,½Î@

…†‡ €€‚‚ƒƒ„@„SÐÓK€!(€X]nKÓMr.€Gary€MorrisÐ	]n ÐWater€AdvisorÐ	CT ÐÔ_ÔExxonMobilÔ_ÔÐ	): ÐÐ
?€Š‹Œ,! @ˆ‰ „<EMAIL_ADDRESS>]n ÐÐS€ŽD,CT@

Š‹Œ €€‚‚ƒƒ„@„SÐÓK€!(€XýKÓMr.€Don€Ô_ÔParrishÔ_ÔÐ	ý	 ÐAmerican€Farm€Bureau€FederationÐ	ã	ô ÐÐ
?€‘,!ÉÚ
@Ž „<EMAIL_ADDRESS>S€’“D,ý@

‘ €€‚‚ƒƒ„@„SÐÓK€!(€X·
ÈKÓThomas€Purcell,€Ph.D.Ð	·
È  ÐAmerican€Petroleum€InstituteÐ	®! ÐÐ
?€”•–,!ƒ ”"@’“ „<EMAIL_ADDRESS>·
È# Ðsee€also:Ð	®$ ÐRoger€Claff,€Ð	ƒ ”% ÐTerry€Ô_ÔTwymanÔ_ÔÐS€—˜D,i!z&@

”•– €€‚‚ƒƒ„@„SÐÓK€!(€XW"hKÓJay€R.€Ô_ÔSpectorÔ_ÔÐ	W"h' ÐDirector€of€Federal€AffairsÐ	=#N( ÐNational€Association€of€Industrial€&€OfficeÐ	#$4) ÐPropertiesÐ		%	* ÐÐ
?€™š›,!ï%+@—˜ „<EMAIL_ADDRESS>W"h, ÐòòÔÿÔÐS€žD,=#N-@

™š› €€‚‚ƒƒ„@„SÐóóÔÿÔÓK€!(€XÝ&îKÓMr.€Bernie€Ô_ÔStrohmeyerÔ_ÔÐ	Ý&î. ÐHRSDÐ	Ã'Ô
/ ÐHampton€Roads€Sanitation€DistrictÐ	©(º0 ÐÐ
?€Ÿ ¡,!)  1@ž „<EMAIL_ADDRESS>Ý&î2 ÐÔ€¢XÌÕXXX==ÔòòÔÿÔÐS€£¤D,Ã'Ô
3@

Ÿ ¡ €€‚‚ƒƒ„@„SÐÔ€X==XX¢XÌÕÔóóÔÿÔÓK€!(€X}*Ž!KÓMr.€Claudio€Ô_ÔTerniedenÔ_ÔÐ	}*Ž!4 ÐDirector€of€Environmental€AffairsÐ	c+t"5 ÐAmerican€Association€of€Airport€ExecutivesÐ	I,Z#6 ÐÐ
?€¥¦§,!/-@$7@£¤ „@„?Ðâ

âclaudio.ternieden@airportnet.org,Ð
S€¨©D,}*Ž!8@

¥¦§ €€‚‚ƒƒ„@„SÐÓK€!(€X÷KÓTerry€Ô_ÔTwymanÔ_ÔÐ	÷ Ðâ

âAmerican€Petroleum€InstituteÐ	Ý	î ÐÐ
?€ª«¬,!Ã
Ô@¨© „<EMAIL_ADDRESS>S€®D,÷@

ª«¬ €€‚‚ƒƒ„@„SÐÓK€!(€X±ÂKÓTony€WagnerÐ	±Â ÐÔ_ÔACCÔ_ÔÐ	—¨ ÐÐ
?€¯°±,!}
Ž@® „<EMAIL_ADDRESS>±Â ÐmÐS€²³D,—¨	@

¯°± €€‚‚ƒƒ„@„SÐÓK€!(€Xk|KÓJack€DillonÐ
?€´µ¶,!k|
@²³ „<EMAIL_ADDRESS>k| ÐÔ_ÔÐS€·¸D,Qb@

´µ¶ €€‚‚ƒƒ„@„SÐÓK€!(€X?PKÓKeith€Ô_ÔHanssenÔ_Ô€(sp?)Ð	?P
 ÐMinnesota€PowerÐ	%6 ÐÐ
?€¹º»,!		@·¸ „<EMAIL_ADDRESS>S€¼½D,?P@

¹º» €€‚‚ƒƒ„@„SÐÓK€!(€Xù

KÓMr.€Jack€HughesÐ	ù

 ÐEnvironmental€AffairsÐ	ßð
 ÐKraft€FoodsÐ	ÅÖ ÐÐ
?€¾¿À,!«¼@¼½ „<EMAIL_ADDRESS>U€ÁÂÃD,ù

@

¾¿À €€‚‚ƒƒ„@„UÐÓK€!(€X™ª
	KÓMax€WilliamsÐ	™ª
 ÐÐ
?€ÄÅÆÇ,!@ÁÂÃ „<EMAIL_ADDRESS>@

ÄÅÆÇ <ÐÓK€!(€Xm~KÓÌÌ


Nielsen et al., 2007. Nielsen, O.J., Javadi, M.S., Sulbaek Andersen,
M.P., Hurley, M.D., Wallington, T.J., Singh, R. (2007). Atmospheric
chemistry of CF3CF=CH2: Kinetics and mechanisms of gas-phase
reactions with Cl atoms, OH radicals, and O3. Chemical Physics
Letters 439, 18-22. Available online at http://www.lexissecuritiesmosaic.com/gateway/FedReg/network_OJN_174_CF3CF=CH2.pdf.
Shecco, 2013a. HCs Gaining Market Prominence in US--View from the
NAFEM Show--Part 1, February 18, 2013.
Shecco, 2013b. HCs Gaining Market Prominence in US--View from the
NAFEM Show--Part 2, February 25, 2013.
Shecco, 2015. New Regulations Inspire Hydrocarbon Displays at U.S.
NAFEM Show, February 24, 2015.
Sherwood et. al. 2018. Sherwood, S. C, Vishal, D., and Salomez, C.
(2018) The global warming potential of near-surface emitted water
vapour. Environ. Res. Lett.,13 104006. Available online at https://iopscience.iop.org/article/10.1088/1748-9326/aae018/pdf.
UL 60335-2-40, 2019. Household And Similar Electrical Appliances--
Safety--Part 2-40: Particular Requirements for Electrical Heat
Pumps, Air-Conditioners and Dehumidifiers. Third Edition. November
1, 2019.

List of Subjects in 40 CFR Part 82

    Environmental protection, Administrative practice and procedure,
Air pollution control, Incorporation by reference, Reporting and
recordkeeping requirements, Stratospheric ozone layer.

Andrew Wheeler,
Administrator.

    For the reasons set forth in the preamble, EPA proposes to amend 40
CFR part 82 as follows:

PART 82--PROTECTION OF STRATOSPHERIC OZONE

0
1. The authority citation for part 82 continues to read as follows:

    Authority:  42 U.S.C. 7414, 7601, 7671-7671q.

Subpart G--Significant New Alternatives Policy Program

0
2. Appendix O to subpart G of part 82 is amended by removing in the
table the entry ``Total flooding; Powdered Aerosol E
(FirePro[supreg])''.
0
3. In appendix U to subpart G of part 82:
0
a. Revise the appendix U to subpart G of part 82 heading.
0
b. Revise in the table entitled ``Unacceptable Substitutes'' the entry
``Polystyrene: Extruded Boardstock and Billet''.
    The revisions read as follows:

Appendix U to Subpart G of Part 82--Unacceptable Substitutes and
Substitutes Subject to Use Restrictions Listed in the July 20, 2015
Final Rule, Effective August 19, 2015 and in the [Date of publication
of the final rule in the Federal Register] Final Rule, Effective [Date
30 Days After Date of Publication of the Final Rule in the Federal
Register]

* * * * *

                                            Unacceptable Substitutes
----------------------------------------------------------------------------------------------------------------
               End-use                        Substitute                Decision           Further information
----------------------------------------------------------------------------------------------------------------

                                                  * * * * * * *
Polystyrene: Extruded Boardstock and   HFC-134a, HFC-245fa,     Unacceptable as of       These foam blowing
 Billet.                                HFC-365mfc, and blends   January 1, 2021 except   agents have GWPs
                                        thereof; Formacel TI,    where allowed under a    ranging from higher
                                        Formacel B, and          narrowed use limit or    than 140 to
                                        Formacel Z-6.            where a blend is         approximately 1,500.
                                                                 specifically listed as   Other substitutes will
                                                                 acceptable.              be available for this
                                                                                end-use with lower
                                                                                overall risk to human
                                                                                health and the
                                                                                environment by the
                                                                                status change date.

                                                  * * * * * * *
----------------------------------------------------------------------------------------------------------------

* * * * *
0
4. Add appendix W to subpart G of part 82 to read as follows:

Appendix W to Subpart G of Part 82--Substitutes Listed in the [Date of
Publication of the Final Rule in the Federal Register] Final Rule--
Effective [Date 30 Days After Date of Publication of the Final Rule in
the Federal Register]

                       Refrigerants--Substitutes Acceptable Subject to Narrowed Use Limits
----------------------------------------------------------------------------------------------------------------
            End-use                Substitute         Decision       Narrowed use limits    Further information
----------------------------------------------------------------------------------------------------------------
Retail food refrigeration--     R-448A, R-449A,   Acceptable        Acceptable only for    Users are required to
 medium- temperature stand-      R-449B.           Subject to        use in new medium-     document and retain
 alone units (new only).                           Narrowed Use      temperature stand-     the results of their
                                                   Limits.           alone units where      technical
                                                                     reasonable efforts     investigation of
                                                                     have been made to      alternatives for the
                                                                     ascertain that other   purpose of
                                                                     alternatives are not   demonstrating
                                                                     technically feasible   compliance.
                                                                     due to the inability   Information should
                                                                     to meet ADA            include descriptions
                                                                     requirements.          of:
                                                                                Process or
                                                                                product in which the
                                                                                substitute is
                                                                                needed;
                                                                                Substitutes
                                                                                examined and
                                                                                rejected;
                                                                                Reason for
                                                                                rejection of other
                                                                                alternatives, e.g.,
                                                                                performance,
                                                                                technical or safety
                                                                                standards, ADA
                                                                                requirements; and/or
                                                                                Anticipated
                                                                                date other
                                                                                substitutes will be
                                                                                available and
                                                                                projected time for
                                                                                switching.
----------------------------------------------------------------------------------------------------------------

                         Refrigerants--Substitutes Acceptable Subject to Use Conditions
----------------------------------------------------------------------------------------------------------------
            End-use                Substitute         Decision          Use conditions      Further information
----------------------------------------------------------------------------------------------------------------
I. Residential and light        R-452B, R-454A,   Acceptable        These refrigerants     Applicable OSHA
 commercial air conditioning     R-454B, R-454C    Subject to Use    may be used only in    requirements at 29
 and heat pumps (new only).      and R-457A.       Conditions.       new equipment          CFR part 1910 must
                                                                     specifically           be followed,
                                                                     designed and clearly   including those at
                                                                     identified for the     29 CFR 1910.94
                                                                     refrigerants (i.e.,    (ventilation) and
                                                                     none of these          1910.106 (flammable
                                                                     substitutes may be     and combustible
                                                                     used as a conversion   liquids), 1910.110
                                                                     or ``retrofit''        (storage and
                                                                     refrigerant for        handling of
                                                                     existing equipment     liquefied petroleum
                                                                     designed for other     gases), and
                                                                     refrigerants).         1910.1000 (toxic and
                                                                                hazardous
                                                                                substances).
                                                                    These substitutes may  Proper ventilation
                                                                     only be used in air    should be maintained
                                                                     conditioning           at all times during
                                                                     equipment that meets   the manufacture and
                                                                     all requirements in    storage of equipment
                                                                     UL 60335-2-40.1 2 3    containing
                                                                     In cases where this    hydrocarbon
                                                                     appendix includes      refrigerants through
                                                                     requirements more      adherence to good
                                                                     stringent than those   manufacturing
                                                                     of UL 60335-2-40,      practices as per 29
                                                                     the appliance must     CFR 1910.106. If
                                                                     meet the               refrigerant levels
                                                                     requirements of this   in the air
                                                                     appendix in place of   surrounding the
                                                                     the requirements in    equipment rise above
                                                                     UL 60335-2-40.         one-fourth of the
                                                                                lower flammability
                                                                                limit, the space
                                                                                should be evacuated
                                                                                and reentry should
                                                                                occur only after the
                                                                                space has been
                                                                                properly ventilated.
                                                                    The charge size for    Technicians and
                                                                     the equipment must     equipment
                                                                     not exceed the         manufacturers should
                                                                     maximum refrigerant    wear appropriate
                                                                     mass determined        personal protective
                                                                     according to UL        equipment, including
                                                                     60335-2-40 for the     chemical goggles and
                                                                     room size where the    protective gloves,
                                                                     air conditioner is     when handling
                                                                     used.                  flammable
                                                                                refrigerants.
                                                                                Special care should
                                                                                be taken to avoid
                                                                                contact with the
                                                                                skin which, like
                                                                                many refrigerants,
                                                                                can cause freeze
                                                                                burns on the skin.
                                                                    The following          A class B dry powder
                                                                     markings must be       type fire
                                                                     attached at the        extinguisher should
                                                                     locations provided     be kept nearby.
                                                                     and must be           Technicians should
                                                                     permanent:             only use spark-proof
                                                                    (a) On the outside of   tools when working
                                                                     the air conditioning   on air conditioning
                                                                     equipment:             equipment with
                                                                     ``WARNING--Risk of     flammable
                                                                     Fire. Flammable        refrigerants.
                                                                     Refrigerant Used. To
                                                                     Be Repaired Only By
                                                                     Trained Service
                                                                     Personnel. Do Not
                                                                     Puncture Refrigerant
                                                                     Tubing.''.

                                                                    (b) On the outside of  Any recovery
                                                                     the air conditioning   equipment used
                                                                     equipment:             should be designed
                                                                     ``WARNING--Risk of     for flammable
                                                                     Fire. Dispose of       refrigerants. Any
                                                                     Properly In            refrigerant releases
                                                                     Accordance With        should be in a well-
                                                                     Federal Or Local       ventilated area,
                                                                     Regulations.           such as outside of a
                                                                     Flammable              building. Only
                                                                     Refrigerant Used.''    technicians
                                                                                specifically trained
                                                                                in handling
                                                                                flammable
                                                                                refrigerants should
                                                                                service
                                                                                refrigeration
                                                                                equipment containing
                                                                                this refrigerant.
                                                                                Technicians should
                                                                                gain an
                                                                                understanding of
                                                                                minimizing the risk
                                                                                of fire and the
                                                                                steps to use
                                                                                flammable
                                                                                refrigerants safely.
                                                                    (c) On the inside of   Room occupants should
                                                                     the air conditioning   evacuate the space
                                                                     equipment near the     immediately
                                                                     compressor:            following the
                                                                     ``WARNING--Risk of     accidental release
                                                                     Fire. Flammable        of this refrigerant.
                                                                     Refrigerant Used.     Personnel
                                                                     Consult Repair         commissioning,
                                                                     Manual/Owner's Guide   maintaining,
                                                                     Before Attempting To   repairing,
                                                                     Service This           decommissioning and
                                                                     Product. All Safety    disposing of
                                                                     Precautions Must be    appliances with
                                                                     Followed.''            these refrigerants
                                                                                should obtain
                                                                                training and follow
                                                                                practices consistent
                                                                                with Annex HH of UL
                                                                                260355-2-40, 3rd
                                                                                edition.
                                                                    (d) For any equipment  CAA section 608(c)(2)
                                                                     pre-charged at the     prohibition on
                                                                     factory, on the        knowingly venting or
                                                                     equipment              otherwise knowingly
                                                                     packaging``WARNING--   releasing or
                                                                     Risk of Fire due to    disposing of
                                                                     Flammable              substitute
                                                                     Refrigerant Used.      refrigerants in the
                                                                     Follow Handling        course of
                                                                     Instructions           maintaining,
                                                                     Carefully in           servicing, repairing
                                                                     Compliance with        or disposing of an
                                                                     National               appliance or
                                                                     Regulations''          industrial process
                                                                    (e) On the indoor       refrigeration.
                                                                     unit near the         Department of
                                                                     nameplate:.            Transportation
                                                                                requirements for
                                                                                transport of
                                                                                flammable gases must
                                                                                be followed.
                                                                       a. At the top of    Mildly flammable
                                                                        the marking:        refrigerants being
                                                                        ``Minimum           recovered or
                                                                        Installation        otherwise disposed
                                                                        height, X m (W      of from residential
                                                                        ft)''. This         and light commercial
                                                                        marking is only     air conditioning
                                                                        required if         appliances are
                                                                        required by UL      likely to be
                                                                        60335-2-40. The     hazardous waste
                                                                        terms ``X'' and     under the Resource
                                                                        ``W'' shall be      Conservation and
                                                                        replaced by the     Recovery Act (RCRA)
                                                                        numeric height as   (see 40 CFR parts
                                                                        calculated per UL   260-270).
                                                                        60335-2-40. Note
                                                                        that the
                                                                        formatting here
                                                                        is slightly
                                                                        different than UL
                                                                        60335-2-40;
                                                                        specifically, the
                                                                        height in Inch-
                                                                        Pound units is
                                                                        placed in
                                                                        parentheses and
                                                                        the word ``and''
                                                                        has been replaced
                                                                        by the opening
                                                                        parenthesis..
                                                                       b. Immediately      .....................
                                                                        below the
                                                                        markings
                                                                        described in
                                                                        I.(a) or at the
                                                                        top of the
                                                                        marking if (a) is
                                                                        not required:
                                                                        ``Minimum room
                                                                        area (operating
                                                                        or storage), Y
                                                                        m\2\ (Z ft\2\)''.
                                                                        The terms ``Y''
                                                                        and ``Z'' shall
                                                                        be replaced by
                                                                        the numeric area
                                                                        as calculated per
                                                                        UL 60335-2-40.
                                                                        Note that the
                                                                        formatting here
                                                                        is slightly
                                                                        different than UL
                                                                        60335-2-40;
                                                                        specifically, the
                                                                        area in Inch-
                                                                        Pound units is
                                                                        placed in
                                                                        parentheses and
                                                                        the word ``and''
                                                                        has been replaced
                                                                        by the opening
                                                                        parenthesis..
                                                                    (f) For non-fixed      .....................
                                                                     equipment, including
                                                                     portable air
                                                                     conditioners, window
                                                                     air conditioners,
                                                                     packaged terminal
                                                                     air conditioners and
                                                                     packaged terminal
                                                                     heat pumps, on the
                                                                     outside of the
                                                                     product: ``WARNING--
                                                                     Risk of Fire or
                                                                     Explosion--Store in
                                                                     a well ventilated
                                                                     room without
                                                                     continuously
                                                                     operating flames or
                                                                     other potential
                                                                     ignition.''
                                                                    (g) For fixed          .....................
                                                                     equipment, including
                                                                     rooftop units and
                                                                     split air
                                                                     conditioners,
                                                                     ``WARNING--Risk of
                                                                     Fire--Auxiliary
                                                                     devices which may be
                                                                     ignition sources
                                                                     shall not be
                                                                     installed in the
                                                                     ductwork, other than
                                                                     auxiliary devices
                                                                     listed for use with
                                                                     the specific
                                                                     appliance. See
                                                                     instructions.''
                                                                    (h) All of these       .....................
                                                                     markings must be in
                                                                     letters no less than
                                                                     6.4 mm (\1/4\ inch)
                                                                     high.

                                                                    The equipment must     .....................
                                                                     have red Pantone
                                                                     Matching System
                                                                     (PMS) #185 or RAL
                                                                     3020 marked pipes,
                                                                     hoses, or other
                                                                     devices through
                                                                     which the
                                                                     refrigerant passes,
                                                                     to indicate the use
                                                                     of a flammable
                                                                     refrigerant. This
                                                                     color must be
                                                                     applied at all
                                                                     service ports and
                                                                     other parts of the
                                                                     system where service
                                                                     puncturing or other
                                                                     actions creating an
                                                                     opening from the
                                                                     refrigerant circuit
                                                                     to the atmosphere
                                                                     might be expected
                                                                     and must extend a
                                                                     minimum of one (1)
                                                                     inch (25mm) in both
                                                                     directions from such
                                                                     locations and shall
                                                                     be replaced if
                                                                     removed.
----------------------------------------------------------------------------------------------------------------
II. Residential and light       R-32............  Acceptable        This refrigerant may   Applicable OSHA
 commercial air conditioning                       Subject to Use    be used only in new    requirements at 29
 and heat pumps (new only),                        Conditions.       equipment              CFR part 1910 must
 excluding self-contained room                                       specifically           be followed,
 air conditioners.                                                   designed and clearly   including those at
                                                                     identified for the     29 CFR 1910.94
                                                                     refrigerants (i.e.,    (ventilation) and
                                                                     none of these          1910.106 (flammable
                                                                     substitutes may be     and combustible
                                                                     used as a conversion   liquids), 1910.110
                                                                     or ``retrofit''        (storage and
                                                                     refrigerant for        handling of
                                                                     existing equipment     liquefied petroleum
                                                                     designed for other     gases), and
                                                                     refrigerants).         1910.1000 (toxic and
                                                                                hazardous
                                                                                substances).
                                                                    These substitutes may  Proper ventilation
                                                                     only be used in air    should be maintained
                                                                     conditioning           at all times during
                                                                     equipment that meets   the manufacture and
                                                                     all requirements in    storage of equipment
                                                                     UL 60335-2-40.1 2 3    containing
                                                                     In cases where this    hydrocarbon
                                                                     appendix includes      refrigerants through
                                                                     requirements more      adherence to good
                                                                     stringent than those   manufacturing
                                                                     of UL 60335-2-40,      practices as per 29
                                                                     the appliance must     CFR 1910.106. If
                                                                     meet the               refrigerant levels
                                                                     requirements of this   in the air
                                                                     appendix in place of   surrounding the
                                                                     the requirements in    equipment rise above
                                                                     UL 60335-2-40          one-fourth of the
                                                                                lower flammability
                                                                                limit, the space
                                                                                should be evacuated
                                                                                and reentry should
                                                                                occur only after the
                                                                                space has been
                                                                                properly ventilated.
                                                                    The charge size for    Technicians and
                                                                     the equipment must     equipment
                                                                     not exceed the         manufacturers should
                                                                     maximum refrigerant    wear appropriate
                                                                     mass determined        personal protective
                                                                     according to UL        equipment, including
                                                                     60335-2-40 for the     chemical goggles and
                                                                     room size where the    protective gloves,
                                                                     air conditioner is     when handling
                                                                     used.                  flammable
                                                                    The following           refrigerants.
                                                                     markings must be       Special care should
                                                                     attached at the        be taken to avoid
                                                                     locations provided     contact with the
                                                                     and must be            skin which, like
                                                                     permanent:.            many refrigerants,
                                                                                can cause freeze
                                                                                burns on the skin.
                                                                                A class B dry powder
                                                                                type fire
                                                                                extinguisher should
                                                                                be kept nearby.
                                                                                Technicians should
                                                                    (a) On the outside of   only use spark-proof
                                                                     the air conditioning   tools when working
                                                                     equipment:             on air conditioning
                                                                     ``WARNING--Risk of     equipment with
                                                                     Fire. Flammable        flammable
                                                                     Refrigerant Used. To   refrigerants.
                                                                     Be Repaired Only By
                                                                     Trained Service
                                                                     Personnel. Do Not
                                                                     Puncture Refrigerant
                                                                     Tubing.''.
                                                                    (b) On the outside of  Any recovery
                                                                     the air conditioning   equipment used
                                                                     equipment:             should be designed
                                                                     ``WARNING--Risk of     for flammable
                                                                     Fire. Dispose of       refrigerants. Any
                                                                     Properly In            refrigerant releases
                                                                     Accordance With        should be in a well-
                                                                     Federal Or Local       ventilated area,
                                                                     Regulations.           such as outside of a
                                                                     Flammable              building. Only
                                                                     Refrigerant Used.''    technicians
                                                                    (c) On the inside of    specifically trained
                                                                     the air conditioning   in handling
                                                                     equipment near the     flammable
                                                                     compressor:            refrigerants should
                                                                     ``WARNING--Risk of     service
                                                                     Fire. Flammable        refrigeration
                                                                     Refrigerant Used.      equipment containing
                                                                     Consult Repair         this refrigerant.
                                                                     Manual/Owner's Guide   Technicians should
                                                                     Before Attempting To   gain an
                                                                     Service This           understanding of
                                                                     Product. All Safety    minimizing the risk
                                                                     Precautions Must be    of fire and the
                                                                     Followed.''.           steps to use
                                                                                flammable
                                                                                refrigerants safely.
                                                                    (d) For any equipment  Room occupants should
                                                                     pre-charged at the     evacuate the space
                                                                     factory, on the        immediately
                                                                     equipment packaging:   following the
                                                                     ``WARNING--Risk of     accidental release
                                                                     Fire due to            of this refrigerant.
                                                                     Flammable             Personnel
                                                                     Refrigerant Used.      commissioning,
                                                                     Follow Handling        maintaining,
                                                                     Instructions           repairing,
                                                                     Carefully in           decommissioning and
                                                                     Compliance with        disposing of
                                                                     National               appliances with this
                                                                     Regulations''          refrigerant should
                                                                    (e) On the indoor       obtain training and
                                                                     unit near the          follow practices
                                                                     nameplate:.            consistent with
                                                                                Annex HH of UL
                                                                                260355-2-40, 3rd
                                                                                edition.

                                                                       a. At the top of    CAA section 608(c)(2)
                                                                        the marking:        prohibition on
                                                                        ``Minimum           knowingly venting or
                                                                        Installation        otherwise knowingly
                                                                        height, X m (W      releasing or
                                                                        ft)''. This         disposing of
                                                                        marking is only     substitute
                                                                        required if         refrigerants in the
                                                                        required by UL      course of
                                                                        60335-2-40. The     maintaining,
                                                                        terms ``X'' and     servicing, repairing
                                                                        ``W'' shall be      or disposing of an
                                                                        replaced by the     appliance or
                                                                        numeric height as   industrial process
                                                                        calculated per UL   refrigeration.
                                                                        60335-2-40. Note   Department of
                                                                        that the            Transportation
                                                                        formatting here     requirements for
                                                                        is slightly         transport of
                                                                        different than UL   flammable gases must
                                                                        60335-2-40;         be followed.
                                                                        specifically, the
                                                                        height in Inch-
                                                                        Pound units is
                                                                        placed in
                                                                        parentheses and
                                                                        the word ``and''
                                                                        has been replaced
                                                                        by the opening
                                                                        parenthesis..
                                                                       b. Immediately      Mildly flammable
                                                                        below the marking   refrigerants being
                                                                        specified in        recovered or
                                                                        II.(a) or at the    otherwise disposed
                                                                        top of the          of from residential
                                                                        marking if (a) is   and light commercial
                                                                        not required:       air conditioning
                                                                        ``Minimum room      appliances are
                                                                        area (operating     likely to be
                                                                        or storage), Y      hazardous waste
                                                                        m\2\ (Z ft\2\)''.   under the Resource
                                                                        The terms ``Y''     Conservation and
                                                                        and ``Z'' shall     Recovery Act (RCRA)
                                                                        be replaced by      (see 40 CFR parts
                                                                        the numeric area    260-270).
                                                                        as calculated per
                                                                        UL 60335-2-40.
                                                                        Note that the
                                                                        formatting here
                                                                        is slightly
                                                                        different than UL
                                                                        60335-2-40;
                                                                        specifically, the
                                                                        area in Inch-
                                                                        Pound units is
                                                                        placed in
                                                                        parentheses and
                                                                        the word ``and''
                                                                        has been replaced
                                                                        by the opening
                                                                        parenthesis..
                                                                    (f) For fixed          .....................
                                                                     equipment, including
                                                                     rooftop units and
                                                                     split air
                                                                     conditioners,
                                                                     ``WARNING--Risk of
                                                                     Fire--Auxiliary
                                                                     devices which may be
                                                                     ignition sources
                                                                     shall not be
                                                                     installed in the
                                                                     ductwork, other than
                                                                     auxiliary devices
                                                                     listed for use with
                                                                     the specific
                                                                     appliance. See
                                                                     instructions.''
                                                                    (g) All of these       .....................
                                                                     markings must be in
                                                                     letters no less than
                                                                     6.4 mm (\1/4\ inch)
                                                                     high.
                                                                    The equipment must     .....................
                                                                     have red Pantone
                                                                     Matching System
                                                                     (PMS) #185 or RAL
                                                                     3020 marked pipes,
                                                                     hoses, or other
                                                                     devices through
                                                                     which the
                                                                     refrigerant passes,
                                                                     to indicate the use
                                                                     of a flammable
                                                                     refrigerant. This
                                                                     color must be
                                                                     applied at all
                                                                     service ports and
                                                                     other parts of the
                                                                     system where service
                                                                     puncturing or other
                                                                     actions creating an
                                                                     opening from the
                                                                     refrigerant circuit
                                                                     to the atmosphere
                                                                     might be expected
                                                                     and must extend a
                                                                     minimum of one (1)
                                                                     inch (25mm) in both
                                                                     directions from such
                                                                     locations and shall
                                                                     be replaced if
                                                                     removed.
----------------------------------------------------------------------------------------------------------------
\1\ The Director of the Federal Register approves this standard for incorporation by reference under 5 U.S.C.
  552(a) and 1 CFR part 51. You may inspect a copy at U.S. EPA's Air and Radiation Docket; EPA West Building,
  Room 3334, 1301 Constitution Ave. NW, Washington DC or at the National Archives and Records Administration
  (NARA). For questions regarding access to these standards, the telephone number of EPA's Air and Radiation
  Docket is<PHONE_NUMBER>. For information on the availability of this material at NARA, call<PHONE_NUMBER>, or go
  to: www.archives.gov/federal-register/cfr/ibr-locations.html.
\2\ You may obtain this standard from: Underwriters Laboratories Inc. (UL) COMM 2000; 151 Eastern Avenue;
exception occurred on : 2020-11990.htm
  Bensenville, IL 60106; 2000.com">[email protected]2000.com; 1-888-853-3503 in the U.S. or Canada (other countries dial +1-415-
  352-2168); http://ulstandards.ul.com/ or www.comm-2000.com.
\3\ UL 60335-2-40, Standard for Household And Similar Electrical Appliances--Safety--Part 2- 40: Particular
  Requirements for Electrical Heat Pumps, Air-Conditioners and Dehumidifiers, 3rd edition, Dated November 1,
  2019.

[FR Doc. 2020-11990 Filed 6-11-20; 8:45 am]
BILLING CODE 6560-50-P


[Federal Register Volume 88, Number 180 (Tuesday, September 19, 2023)]
[Notices]
[Pages 64425-64427]
[FR Doc No: 2023-20213]

=======================================================================
-----------------------------------------------------------------------

DEPARTMENT OF ENERGY

Federal Energy Regulatory Commission

Combined Notice of Filings #1

    Take notice that the Commission received the following exempt
wholesale generator filings:

    Docket Numbers: EG23-286-000.
    Applicants: Earp Solar, LLC.
    Description: Earp Solar, LLC submits Notice of Self-Certification
of Exempt Wholesale Generator Status.
    Filed Date: 9/13/23.
    Accession Number: 20230913-5047.
    Comment Date: 5 p.m. ET 10/4/23.

    Docket Numbers: EG23-287-000.

    Applicants: BCD 2023 Fund 1 Lessee, LLC.
    Description: BCD 2023 Fund 1 Lessee, LLC submits Notice of Self-
Certification of Exempt Wholesale Generator Status.
    Filed Date: 9/13/23.
    Accession Number: 20230913-5049.
    Comment Date: 5 p.m. ET 10/4/23.

    Take notice that the Commission received the following electric
rate filings:

    Docket Numbers: ER22-2721-002.
    Applicants: Union Electric Company.
    Description: Compliance filing: Compliance Filing to be effective
9/1/2023.
    Filed Date: 9/13/23.
    Accession Number: 20230913-5024.
    Comment Date: 5 p.m. ET 10/4/23.

    Docket Numbers: ER22-2721-003.
    Applicants: Union Electric Company.
    Description: Compliance filing: Compliance Filing to be effective
9/1/2022.
    Filed Date: 9/13/23.
    Accession Number: 20230913-5085.
    Comment Date: 5 p.m. ET 10/4/23.

    Docket Numbers: ER23-2020-001.
    Applicants: California Independent System Operator Corporation.
    Description: Compliance filing: 2023-09-13 Compliance Filing--
Market Parameters to be effective 9/13/2023.
    Filed Date: 9/13/23.
    Accession Number: 20230913-5064.
    Comment Date: 5 p.m. ET 10/4/23.

    Docket Numbers: ER23-2487-001.
    Applicants: Midcontinent Independent System Operator, Inc., Ameren
Services Company.
    Description: Tariff Amendment: Midcontinent Independent System
Operator, Inc. submits tariff filing per 35.17(b): 2023-09-13_Amendment
Ameren Companies Request for Transmission Rate Incentives to be
effective 9/25/2023.
    Filed Date: 9/13/23.
    Accession Number: 20230913-5082.
    Comment Date: 5 p.m. ET 10/4/23.

    Docket Numbers: ER23-2563-001.
    Applicants: PJM Interconnection, L.L.C.
    Description: Tariff Amendment: Amendment of WMPA, SA No. 7005;
Queue No. AG1-099 in Docket No. ER23-2563-000 to be effective 10/4/
2023.
    Filed Date: 9/13/23.
    Accession Number: 20230913-5072.
    Comment Date: 5 p.m. ET 10/4/23.

    Docket Numbers: ER23-2678-001.
    Applicants: PJM Interconnection, L.L.C.
    Description: Tariff Amendment: Amendment of ISA, SA No. 7041; Queue
No. AE2-092 in Docket ER23-2678-000 to be effective 7/20/2023.
    Filed Date: 9/13/23.
    Accession Number: 20230913-5052.
    Comment Date: 5 p.m. ET 10/4/23.

    Docket Numbers: ER23-2824-000.
    Applicants: PacifiCorp.
    Description: Sec.  205(d) Rate Filing: Ostrea Solar Affected System
Project Construction Agreement to be effective 9/14/2023.
    Filed Date: 9/13/23.
    Accession Number: 20230913-5042.
    Comment Date: 5 p.m. ET 10/4/23.

    Docket Numbers: ER23-2825-000.
    Applicants: Northstar Trading Ltd.
    Description: Baseline eTariff Filing: NorthStar Trading Ltd.
submits tariff filing per 35.12: Baseline new to be effective 9/14/
2023.
    Filed Date: 9/13/23.
    Accession Number: 20230913-5043.
    Comment Date: 5 p.m. ET 10/4/23.

    Docket Numbers: ER23-2826-000.
    Applicants: Sparta Northstar Ltd.
    Description: Baseline eTariff Filing: Baseline new to be effective
9/14/2023.
    Filed Date: 9/13/23.
    Accession Number: 20230913-5044.
    Comment Date: 5 p.m. ET 10/4/23.

    Docket Numbers: ER23-2827-000.
    Applicants: Battery Utility of Ohio, LLC.
    Description: Tariff Amendment: Notice of Cancellation of Market-
Based Rate Tariff and Request for Waiver to be effective 9/14/2023.
    Filed Date: 9/13/23.
    Accession Number: 20230913-5061.
    Comment Date: 5 p.m. ET 10/4/23.

    Docket Numbers: ER23-2828-000.
    Applicants: Southern California Edison Company.
    Description: Tariff Amendment: Termination of 5149 Lancaster Energy
DSA (GFID8469/SA No. 915) to be effective 11/13/2023.
    Filed Date: 9/13/23.
    Accession Number: 20230913-5053.
    Comment Date: 5 p.m. ET 10/4/23.

    Docket Numbers: ER23-2829-000.
    Applicants: Omnis Pleasants, LLC.
    Description: Compliance filing: Notice of Succession and Request
for Waiver to be effective 12/31/9998.
    Filed Date: 9/13/23.
    Accession Number: 20230913-5056.
    Comment Date: 5 p.m. ET 10/4/23.

    Docket Numbers: ER23-2830-000.
    Applicants: WSPP Inc.
    Description: Sec.  205(d) Rate Filing: List of Members Update 2023
to be effective 9/11/2023.
    Filed Date: 9/13/23.
    Accession Number: 20230913-5073.
    Comment Date: 5 p.m. ET 10/4/23.

    Docket Numbers: ER23-2831-000.
    Applicants: PJM Interconnection, L.L.C.
    Description: Sec.  205(d) Rate Filing: Designated Entity Agreement,
SA No. 7061 between PJM and JCP&L to be effective 8/14/2023.
    Filed Date: 9/13/23.
    Accession Number: 20230913-5096.
    Comment Date: 5 p.m. ET 10/4/23.

    Take notice that the Commission received the following electric
securities filings:

    Docket Numbers: ES23-68-000.
    Applicants: Old Dominion Electric Cooperative.
    Description: Application Under Section 204 of the Federal Power Act
for Authorization to Issue Securities of Old Dominion Electric
Cooperative.
    Filed Date: 9/12/23.
    Accession Number: 20230912-5211.
    Comment Date: 5 p.m. ET 10/3/23.

    Take notice that the Commission received the following public
utility holding company filings:

    Docket Numbers: PH23-16-000.
    Applicants: DTE Energy Company.
    Description: DTE Energy Company submits FERC 65-B Notice of Change
in Fact to Waiver Notification.
    Filed Date: 9/13/23.
    Accession Number: 20230913-5021.
    Comment Date: 5 p.m. ET 10/4/23.

    The filings are accessible in the Commission's eLibrary system
(https://elibrary.ferc.gov/idmws/search/fercgensearch.asp) by querying
the docket number.
    Any person desiring to intervene, to protest, or to answer a
complaint in any of the above proceedings must file in accordance with
Rules 211, 214, or 206 of the Commission's Regulations (18 CFR 385.211,
385.214, or 385.206) on or before 5:00 p.m. Eastern time on the
specified comment date. Protests may be considered, but intervention is
necessary to become a party to the proceeding.
    eFiling is encouraged. More detailed information relating to filing
requirements, interventions, protests, service, and qualifying
facilities filings can be found at: http://www.ferc.gov/docs-filing/efiling/filing-req.pdf. For other information, call<PHONE_NUMBER>
(toll free). For TTY, call<PHONE_NUMBER>.
    The Commission's Office of Public Participation (OPP) supports
meaningful public engagement and participation in Commission
proceedings. OPP can help members of the public, including landowners,
environmental justice communities, Tribal members and others, access
publicly available information and navigate Commission processes. For
public inquiries and assistance with making filings such as
interventions, comments, or requests for rehearing, the public is
encouraged to

contact OPP at<PHONE_NUMBER> or [email protected].

    Dated: September 13, 2023.
Debbie-Anne A. Reese,
Deputy Secretary.
[FR Doc. 2023-20213 Filed 9-18-23; 8:45 am]
BILLING CODE 6717-01-P