63.1283(d)(3)(i)(H)(1).
    (2) A pilot flame shall be present at all times of operation. The
pilot flame shall be monitored in accordance with Sec.
63.1283(d)(3)(i)(H)(2).
    (3) Devices shall be operated with no visible emissions, except for
periods not to exceed a total of 2 minutes during any hour. A visible
emissions test using Method 22, 40 CFR part 60, Appendix A, shall be
performed each calendar quarter. The observation period shall be 1 hour
and shall be conducted according to EPA Method 22, 40 CFR part 60,
Appendix A.
    (4) Compliance with the operating parameter limit is achieved when
the following criteria are met:
    (i) The inlet gas flowrate monitored under paragraph (h)(1) of this
section is equal to or below the maximum established by the
manufacturer; and
    (ii) The pilot flame is present at all times; and
    (iii) During the visible emissions test performed under paragraph
(h)(3) of this section the duration of visible emissions does not
exceed a total of 2 minutes during the observation period. Devices
failing the visible emissions test shall follow manufacturers repair
instructions, if available, or best combustion engineering practice as
outlined in the unit inspection and maintenance plan, to return the
unit to compliant operation. All repairs and maintenance activities for
each unit shall be recorded in a maintenance and repair log and shall
be available on site for inspection.
    (iv) Following return to operation from maintenance or repair
activity, each device must pass a Method 22 visual observation as
described in paragraph (h)(3) of this section.

0
30. Section 63.1283 is amended by:
0
a. Adding paragraph (b);
0
b. Revising paragraph (d)(1) introductory text;
0
c. Revising paragraph (d)(1)(ii) and adding paragraphs (d)(1)(iii) and
(iv);
0
d. Revising paragraph (d)(2);
0
e. Revising paragraph (d)(3)(i)(A);
0
f. Revising paragraph (d)(3)(i)(D);
0
g. Revising paragraph (d)(3)(i)(G);
0
h. Adding paragraph (d)(3)(i)(H);
0
i. Revising paragraph (d)(4);
0
j. Revising paragraph (d)(5)(i);
0
k. Revising paragraphs (d)(5)(ii)(A) through (C);
0
l. Revising paragraph (d)(6) introductory text;
0
m. Revising paragraph (d)(6)(ii);
0
n. Adding paragraph (d)(6)(v);
0
o. Revising paragraph (d)(7); and
0
p. Removing and reserving paragraph (d)(8).
    The additions and revisions read as follows:

Sec.  63.1283  Inspection and monitoring requirements.

* * * * *
    (b) The owner or operator of a control device whose model was
tested under 63.1282(g) shall develop an inspection and maintenance
plan for each control device. At a minimum, the plan shall contain the
control device manufacturer's recommendations for ensuring proper
operation of the device. Semi-annual inspections shall be conducted for
each control device with maintenance and replacement of control device
components made in accordance with the plan.
* * * * *
    (d) Control device monitoring requirements. (1) For each control
device except as provided for in paragraph (d)(2) of this section, the
owner or operator shall install and operate a continuous parameter
monitoring system in accordance with the requirements of paragraphs
(d)(3) through (7) of this section. Owners or operators that install
and operate a flare in accordance with Sec.  63.1281(d)(1)(iii) or
(f)(1)(iii) are exempt from the requirements of paragraphs (d)(4) and
(5) of this section. The continuous monitoring system shall be designed
and operated so that a determination can be made on whether the control
device is achieving the applicable performance requirements of Sec.
63.1281(d), (e)(3), or (f)(1). Each continuous parameter monitoring
system shall meet the following specifications and requirements:
* * * * *
    (ii) A site-specific monitoring plan must be prepared that
addresses the monitoring system design, data collection, and the
quality assurance and quality control elements outlined in paragraph
(d) of this section and in Sec.  63.8(d). Each CPMS must be installed,
calibrated, operated, and maintained in accordance with the procedures
in your approved site-specific monitoring plan. Using the process
described in Sec.  63.8(f)(4), you may request approval of monitoring
system quality assurance and quality control procedures alternative to
those specified in paragraphs (d)(1)(ii)(A) through (E) of this section
in your site-specific monitoring plan.
    (A) The performance criteria and design specifications for the
monitoring system equipment, including the sample interface, detector
signal analyzer, and data acquisition and calculations;
    (B) Sampling interface (e.g., thermocouple) location such that the
monitoring system will provide representative measurements;
    (C) Equipment performance checks, system accuracy audits, or other
audit procedures;
    (D) Ongoing operation and maintenance procedures in accordance with
provisions in Sec.  63.8(c)(1) and (c)(3); and
    (E) Ongoing reporting and recordkeeping procedures in accordance
with provisions in Sec.  63.10(c), (e)(1), and (e)(2)(i).
    (iii) The owner or operator must conduct the CPMS equipment
performance checks, system accuracy audits, or other audit procedures
specified in the site-specific monitoring plan at least once every 12
months.
    (iv) The owner or operator must conduct a performance evaluation of
each CPMS in accordance with the site-specific monitoring plan.
    (2) An owner or operator is exempted from the monitoring
requirements specified in paragraphs (d)(3) through (7) of this section
for the following types of control devices:
    (i) Except for control devices for small glycol dehydration units,
a boiler or process heater in which all vent streams are introduced
with the primary fuel or are used as the primary fuel;
    (ii) Except for control devices for small glycol dehydration units,
a boiler or process heater with a design heat input capacity equal to
or greater than 44 megawatts.
    (3) * * *
    (i) * * *
    (A) For a thermal vapor incinerator that demonstrates during the
performance test conducted under Sec.  63.1282(d) that combustion zone
temperature is an accurate indicator of performance, a temperature
monitoring device equipped with a continuous recorder. The monitoring
device shall have a minimum accuracy of 2 percent of the
temperature being monitored in [deg]C, or 2.5 [deg]C,
whichever value is greater. The temperature sensor shall be installed
at a location representative of the combustion zone temperature.
* * * * *
    (D) For a boiler or process heater, a temperature monitoring device
equipped with a continuous recorder. The temperature monitoring device
shall have a minimum accuracy of 2 percent of the
temperature being monitored in [deg]C, or 2.5 [deg]C,
whichever value is greater. The temperature sensor shall be installed
at a location representative of the combustion zone temperature.
* * * * *
    (G) For a nonregenerative-type carbon adsorption system, the owner
or operator shall monitor the design carbon replacement interval
established using a performance test performed in accordance with Sec.
63.1282(d)(3) and shall be based on the total carbon working capacity
of the control device and source operating schedule.
    (H) For a control device whose model is tested under Sec.
63.1282(g):
    (1) The owner or operator shall determine actual average inlet
waste gas flowrate using the model GRI-GLYCalc\TM\, Version 3.0 or
higher, ProMax, or AspenTech HYSYS. Inputs to the models shall be
representative of actual operating conditions of the controlled unit.
The determination shall be performed to coincide with the visible
emissions test under Sec.  63.1282(h)(3);
    (2) A heat sensing monitoring device equipped with a continuous
recorder that indicates the continuous ignition of the pilot flame.
* * * * *
    (4) Using the data recorded by the monitoring system, except for
inlet gas flowrate, the owner or operator must calculate the daily
average value for each monitored operating parameter for each operating
day. If the emissions unit operation is continuous, the operating day
is a 24-hour period. If the emissions unit operation is not continuous,
the operating day is the total number of hours of control device
operation per 24-hour period. Valid data points must be available for
75 percent of the operating hours in an operating day to compute the
daily average.
    (5) * * *
    (i) The owner or operator shall establish a minimum operating
parameter value or a maximum operating parameter value, as appropriate
for the control device, to

define the conditions at which the control device must be operated to
continuously achieve the applicable performance requirements of Sec.
63.1281(d)(1), (e)(3)(ii), or (f)(1). Each minimum or maximum operating
parameter value shall be established as follows:
    (A) If the owner or operator conducts performance tests in
accordance with the requirements of Sec.  63.1282(d)(3) to demonstrate
that the control device achieves the applicable performance
requirements specified in Sec.  63.1281(d)(1), (e)(3)(ii), or (f)(1),
then the minimum operating parameter value or the maximum operating
parameter value shall be established based on values measured during
the performance test and supplemented, as necessary, by a condenser
design analysis or control device manufacturer's recommendations or a
combination of both.
    (B) If the owner or operator uses a condenser design analysis in
accordance with the requirements of Sec.  63.1282(d)(4) to demonstrate
that the control device achieves the applicable performance
requirements specified in Sec.  63.1281(d)(1), (e)(3)(ii), or (f)(1),
then the minimum operating parameter value or the maximum operating
parameter value shall be established based on the condenser design
analysis and may be supplemented by the condenser manufacturer's
recommendations.
    (C) If the owner or operator operates a control device where the
performance test requirement was met under Sec.  63.1282(g) to
demonstrate that the control device achieves the applicable performance
requirements specified in Sec.  63.1281(d)(1), (e)(3)(ii) or (f)(1),
then the maximum inlet gas flowrate shall be established based on the
performance test and supplemented, as necessary, by the manufacturer
recommendations.
    (ii) * * *
    (A) If the owner or operator conducts a performance test in
accordance with the requirements of Sec.  63.1282(d)(3) to demonstrate
that the condenser achieves the applicable performance requirements in
Sec.  63.1281(d)(1), (e)(3)(ii), or (f)(1), then the condenser
performance curve shall be based on values measured during the
performance test and supplemented as necessary by control device design
analysis, or control device manufacturer's recommendations, or a
combination or both.
    (B) If the owner or operator uses a control device design analysis
in accordance with the requirements of Sec.  63.1282(d)(4)(i) to
demonstrate that the condenser achieves the applicable performance
requirements specified in Sec.  63.1281(d)(1), (e)(3)(ii), or (f)(1),
then the condenser performance curve shall be based on the condenser
design analysis and may be supplemented by the control device
manufacturer's recommendations.
    (C) As an alternative to paragraph (d)(5)(ii)(B) of this section,
the owner or operator may elect to use the procedures documented in the
GRI report entitled, ``Atmospheric Rich/Lean Method for Determining
Glycol Dehydrator Emissions'' (GRI-95/0368.1) as inputs for the model
GRI-GLYCalc\TM\, Version 3.0 or higher, to generate a condenser
performance curve.
    (6) An excursion for a given control device is determined to have
occurred when the monitoring data or lack of monitoring data result in
any one of the criteria specified in paragraphs (d)(6)(i) through
(d)(6)(v) of this section being met. When multiple operating parameters
are monitored for the same control device and during the same operating
day, and more than one of these operating parameters meets an excursion
criterion specified in paragraphs (d)(6)(i) through (d)(6)(v) of this
section, then a single excursion is determined to have occurred for the
control device for that operating day.
* * * * *
    (ii) For sources meeting Sec.  63.1281(d)(1)(ii), an excursion
occurs when average condenser efficiency calculated according to the
requirements specified in Sec.  63.1282(f)(2)(iii) is less than 95.0
percent, as specified in Sec.  63.1282(f)(3). For sources meeting Sec.
63.1281(f)(1), an excursion occurs when the 30-day average condenser
efficiency calculated according to the requirements of Sec.
63.1282(f)(2)(iii) is less than the identified 30-day required percent
reduction.
* * * * *
    (v) For control device whose model is tested under Sec.  63.1282(g)
an excursion occurs when:
    (A) The inlet gas flowrate exceeds the maximum established during
the test conducted under Sec.  63.1282(g).
    (B) Failure of the quarterly visible emissions test conducted under
Sec.  63.1282(h)(3) occurs.
    (7) For each excursion, the owner or operator shall be deemed to
have failed to have applied control in a manner that achieves the
required operating parameter limits. Failure to achieve the required
operating parameter limits is a violation of this standard.
    (8) [Reserved]
* * * * *

0
31. Section 63.1284 is amended by:
0
a. Revising paragraph (b)(3) introductory text;
0
b. Removing and reserving paragraph (b)(3)(ii);
0
c. Revising paragraph (b)(4)(ii);
0
d. Revising paragraph (b)(4)(iii);
0
e. Adding paragraph (b)(7)(ix); and
0
f. Adding paragraphs (f), (g) and (h).
    The revisions and additions read as follows:

Sec.  63.1284  Recordkeeping requirements.

* * * * *
    (b) * * *
    (3) Records specified in Sec.  63.10(c) for each monitoring system
operated by the owner or operator in accordance with the requirements
of Sec.  63.1283(d). Notwithstanding the previous sentence, monitoring
data recorded during periods identified in paragraphs (b)(3)(i) through
(iv) of this section shall not be included in any average or percent
leak rate computed under this subpart. Records shall be kept of the
times and durations of all such periods and any other periods during
process or control device operation when monitors are not operating or
failed to collect required data.
* * * * *
    (ii) [Reserved]
* * * * *
    (4) * * *
    (ii) Records of the daily average value of each continuously
monitored parameter for each operating day determined according to the
procedures specified in Sec.  63.1283(d)(4) of this subpart, except as
specified in paragraphs (b)(4)(ii)(A) through (C) of this section.
    (A) For flares, the records required in paragraph (e) of this
section.
    (B) For condensers installed to comply with Sec.  63.1275, records
of the annual 30-day rolling average condenser efficiency determined
under Sec.  63.1282(f) shall be kept in addition to the daily averages.
    (C) For a control device whose model is tested under Sec.
63.1282(g), the records required in paragraph (g) of this section.
    (iii) Hourly records of the times and durations of all periods when
the vent stream is diverted from the control device or the device is
not operating.
* * * * *
    (7) * * *
    (ix) Records identifying the carbon replacement schedule under
Sec.  63.1281(d)(5) and records of each carbon replacement.
* * * * *
    (f) The owner or operator of an affected source subject to this
subpart shall maintain records of the occurrence and duration of each
malfunction of

operation (i.e., process equipment) or the air pollution control
equipment and monitoring equipment. The owner or operator shall
maintain records of actions taken during periods of malfunction to
minimize emissions in accordance with Sec.  63.1274(h), including
corrective actions to restore malfunctioning process and air pollution
control and monitoring equipment to its normal or usual manner of
operation.
    (g) Record the following when using a control device whose model is
tested under Sec.  63.1282(g) to comply with Sec.  63.1281(d),
(e)(3)(ii) and (f)(1):
    (1) All visible emission readings and flowrate calculations made
during the compliance determination required by Sec.  63.1282(h); and
    (2) All hourly records and other recorded periods when the pilot
flame is absent.
    (h) The date the semi-annual maintenance inspection required under
Sec.  63.1283(b) is performed. Include a list of any modifications or
repairs made to the control device during the inspection and other
maintenance performed such as cleaning of the fuel nozzles.

0
32. Section 63.1285 is amended by:
0
a. Revising paragraph (b)(1);
0
b. Revising paragraph (b)(6);
0
c. Removing paragraph (b)(7);
0
d. Revising paragraph (d) introductory text;
0
e. Revising paragraph (d)(1) introductory text;
0
f. Revising paragraph (d)(1)(i);
0
g. Revising paragraph (d)(1)(ii) introductory text;
0
h. Revising paragraph (d)(2) introductory text;
0
i. Revising paragraph (d)(4) introductory text;
0
j. Revising paragraph (d)(4)(ii);
0
k. Adding paragraph (d)(4)(iv);
0
l. Revising paragraph (d)(10);
0
m. Adding paragraphs (d)(11) and (d)(12);
0
n. Revising paragraph (e)(2) introductory text;
0
o. Revising paragraph (e)(2)(ii)(B);
0
p. Adding paragraphs (e)(2)(ii)(D) and (E);
0
q. Adding paragraphs (e)(2)(x) through (xiii); and
0
r. Adding paragraph (g).

The revisions and additions read as follows:

Sec.  63.1285  Reporting requirements.

* * * * *
    (b) * * *
    (1) The initial notifications required for existing affected
sources under Sec.  63.9(b)(2) shall be submitted as provided in
paragraphs (b)(1)(i) and (ii) of this section.
    (i) Except as otherwise provided in paragraph (b)(1)(ii) of this
section, the initial notification shall be submitted by 1 year after an
affected source becomes subject to the provisions of this subpart or by
June 17, 2000, whichever is later. Affected sources that are major
sources on or before June 17, 2000 and plan to be area sources by June
17, 2002 shall include in this notification a brief, nonbinding
description of a schedule for the action(s) that are planned to achieve
area source status.
    (ii) An affected source identified under Sec.  63.1270(d)(3) shall
submit an initial notification required for existing affected sources
under Sec.  63.9(b)(2) within 1 year after the affected source becomes
subject to the provisions of this subpart or by October 15, 2013,
whichever is later. An affected source identified under Sec.
63.1270(d)(3) that plans to be an area source by October 15, 2015,
shall include in this notification a brief, nonbinding description of a
schedule for the action(s) that are planned to achieve area source
status.
* * * * *
    (6) If there was a malfunction during the reporting period, the
Periodic Report specified in paragraph (e) of this section shall
include the number, duration, and a brief description for each type of
malfunction which occurred during the reporting period and which caused
or may have caused any applicable emission limitation to be exceeded.
The report must also include a description of actions taken by an owner
or operator during a malfunction of an affected source to minimize
emissions in accordance with Sec.  63.1274(h), including actions taken
to correct a malfunction.
* * * * *
    (d) Each owner or operator of a source subject to this subpart
shall submit a Notification of Compliance Status Report as required
under Sec.  63.9(h) within 180 days after the compliance date specified
in Sec.  63.1270(d). In addition to the information required under
Sec.  63.9(h), the Notification of Compliance Status Report shall
include the information specified in paragraphs (d)(1) through (12) of
this section. This information may be submitted in an operating permit
application, in an amendment to an operating permit application, in a
separate submittal, or in any combination of the three. If all of the
information required under this paragraph have been submitted at any
time prior to 180 days after the applicable compliance dates specified
in Sec.  63.1270(d), a separate Notification of Compliance Status
Report is not required. If an owner or operator submits the information
specified in paragraphs (d)(1) through (12) of this section at
different times, and/or different submittals, subsequent submittals may
refer to previous submittals instead of duplicating and resubmitting
the previously submitted information.
    (1) If a closed-vent system and a control device other than a flare
are used to comply with Sec.  63.1274, the owner or operator shall
submit the information in paragraph (d)(1)(iii) of this section and the
information in either paragraph (d)(1)(i) or (ii) of this section.
    (i) The condenser design analysis documentation specified in Sec.
63.1282(d)(4) of this subpart if the owner or operator elects to
prepare a design analysis; or
    (ii) If the owner or operator is required to conduct a performance
test, the performance test results including the information specified
in paragraphs (d)(1)(ii)(A) and (B) of this section. Results of a
performance test conducted prior to the compliance date of this subpart
can be used provided that the test was conducted using the methods
specified in Sec.  63.1282(d)(3), and that the test conditions are
representative of current operating conditions. If the owner or
operator operates a combustion control device model tested under Sec.
63.1282(g), an electronic copy of the performance test results shall be
submitted via email to<EMAIL_ADDRESS>unless the test
results for that model of combustion control device are posted at the
following Web site: epa.gov/airquality/oilandgas/.
* * * * *
    (2) If a closed-vent system and a flare are used to comply with
Sec.  63.1274, the owner or operator shall submit performance test
results including the information in paragraphs (d)(2)(i) and (ii) of
this section. The owner or operator shall also submit the information
in paragraph (d)(2)(iii) of this section.
* * * * *
    (4) For each control device other than a flare used to meet the
requirements of Sec.  63.1274, the owner or operator shall submit the
information specified in paragraphs (d)(4)(i) through (iv) of this
section for each operating parameter required to be monitored in
accordance with the requirements of Sec.  63.1283(d).
* * * * *
    (ii) An explanation of the rationale for why the owner or operator
selected each of the operating parameter values established in Sec.
63.1283(d)(5) of this subpart. This explanation shall include

any data and calculations used to develop the value, and a description
of why the chosen value indicates that the control device is operating
in accordance with the applicable requirements of Sec.  63.1281(d)(1),
(e)(3)(ii), or (f)(1).
* * * * *
    (iv) For each carbon adsorber, the predetermined carbon replacement
schedule as required in Sec.  63.1281(d)(5)(i).
* * * * *
    (10) The owner or operator shall submit the analysis prepared under
Sec.  63.1281(e)(2) to demonstrate that the conditions by which the
facility will be operated to achieve the HAP emission reduction of 95.0
percent, or the BTEX limit in Sec.  63.1275(b)(1)(iii) through process
modifications or a combination of process modifications and one or more
control devices.
    (11) If the owner or operator installs a combustion control device
model tested under the procedures in Sec.  63.1282(g), the data listed
under Sec.  63.1282(g)(8).
    (12) For each combustion control device model tested under Sec.
63.1282(g), the information listed in paragraphs (d)(12)(i) through
(vi) of this section.
    (i) Name, address and telephone number of the control device
manufacturer.
    (ii) Control device model number.
    (iii) Control device serial number.
    (iv) Date the model of control device was tested by the
manufacturer.
    (v) Manufacturer's HAP destruction efficiency rating.
    (vi) Control device operating parameters, maximum allowable inlet
gas flowrate.
* * * * *
    (e) * * *
    (2) The owner or operator shall include the information specified
in paragraphs (e)(2)(i) through (xiii) of this section, as applicable.
* * * * *
    (ii) * * *
    (B) For each excursion caused when the 30-day average condenser
control efficiency is less than the value, as specified in Sec.
63.1283(d)(6)(ii), the report must include the 30-day average values of
the condenser control efficiency, and the date and duration of the
period that the excursion occurred.
* * * * *
    (D) For each excursion caused when the maximum inlet gas flowrate
identified under Sec.  63.1282(g) is exceeded, the report must include
the values of the inlet gas identified and the date and duration of the
period that the excursion occurred.
    (E) For each excursion caused when visible emissions determined
under Sec.  63.1282(h) exceed the maximum allowable duration, the
report must include the date and duration of the period that the
excursion occurred, repairs affected to the unit, and date the unit was
returned to service.
* * * * *
    (x) The results of any periodic test as required in Sec.
63.1282(d)(3) conducted during the reporting period.
    (xi) For each carbon adsorber used to meet the control device
requirements of Sec.  63.1281(d)(1), records of each carbon replacement
that occurred during the reporting period.
    (xii) For combustion control device inspections conducted in
accordance with Sec.  63.1283(b) the records specified in Sec.
63.1284(h).
    (xiii) Certification by a responsible official of truth, accuracy,
and completeness. This certification shall state that, based on
information and belief formed after reasonable inquiry, the statements
and information in the document are true, accurate, and complete.
* * * * *
    (g) Electronic reporting. (1) Within 60 days after the date of
completing each performance test (defined in Sec.  63.2) as required by
this subpart you must submit the results of the performance tests
required by this subpart to EPA's WebFIRE database by using the
Compliance and Emissions Data Reporting Interface (CEDRI) that is
accessed through EPA's Central Data Exchange (CDX)(www.epa.gov/cdx).
Performance test data must be submitted in the file format generated
through use of EPA's Electronic Reporting Tool (ERT) (see http://www.epa.gov/ttn/chief/ert/index.html). Only data collected using test
methods on the ERT Web site are subject to this requirement for
submitting reports electronically to WebFIRE. Owners or operators who
claim that some of the information being submitted for performance
tests is confidential business information (CBI) must submit a complete
ERT file including information claimed to be CBI on a compact disk or
other commonly used electronic storage media (including, but not
limited to, flash drives) to EPA. The electronic media must be clearly
marked as CBI and mailed to U.S. EPA/OAPQS/CORE CBI Office, Attention:
WebFIRE Administrator, MD C404-02, 4930 Old Page Rd., Durham, NC 27703.
The same ERT file with the CBI omitted must be submitted to EPA via CDX
as described earlier in this paragraph. At the discretion of the
delegated authority, you must also submit these reports, including the
confidential business information, to the delegated authority in the
format specified by the delegated authority.
    (2) All reports required by this subpart not subject to the
requirements in paragraph (g)(1) of this section must be sent to the
Administrator at the appropriate address listed in Sec.  63.13. The
Administrator or the delegated authority may request a report in any
form suitable for the specific case (e.g., by commonly used electronic
media such as Excel spreadsheet, on CD or hard copy). The Administrator
retains the right to require submittal of reports subject to paragraph
(g)(1) of this section in paper format.

0
33. Section 63.1287 is amended by revising paragraph (a) to read as
follows:

Sec.  63.1287  Alternative means of emission limitation.

    (a) If, in the judgment of the Administrator, an alternative means
of emission limitation will achieve a reduction in HAP emissions at
least equivalent to the reduction in HAP emissions from that source
achieved under the applicable requirements in Sec. Sec.  63.1274
through 63.1281, the Administrator will publish a notice in the Federal
Register permitting the use of the alternative means for purposes of
compliance with that requirement. The notice may condition the
permission on requirements related to the operation and maintenance of
the alternative means.
* * * * *

0
34. Appendix to Subpart HHH of Part 63--Table is amended by revising
Table 2 to read as follows:

Appendix to Subpart HHH of Part 63--Tables

* * * * *

   Table 2 to Subpart HHH of Part 63--Applicability of 40 CFR Part 63
                    General Provisions to Subpart HHH
------------------------------------------------------------------------
     General provisions           Applicable to
          reference                subpart HHH           Explanation
------------------------------------------------------------------------
Sec.   63.1(a)(1)...........  Yes.                  ....................
Sec.   63.1(a)(2)...........  Yes.                  ....................
Sec.   63.1(a)(3)...........  Yes.                  ....................
Sec.   63.1(a)(4)...........  Yes.                  ....................
Sec.   63.1(a)(5)...........  No..................  Section reserved.
Sec.   63.1(a)(6) through     Yes.                  ....................
 (a)(8).
Sec.   63.1(a)(9)...........  No..................  Section reserved.
Sec.   63.1(a)(10)..........  Yes.                  ....................
Sec.   63.1(a)(11)..........  Yes.                  ....................
Sec.   63.1(a)(12)..........  Yes.                  ....................
Sec.   63.1(b)(1)...........  No..................  Subpart HHH
                                                     specifies
                                                     applicability.
Sec.   63.1(b)(2)...........  Yes.                  ....................
Sec.   63.1(b)(3)...........  No.                   ....................
Sec.   63.1(c)(1)...........  No..................  Subpart HHH
                                                     specifies
                                                     applicability.
Sec.   63.1(c)(2)...........  No.                   ....................
Sec.   63.1(c)(3)...........  No..................  Section reserved.
Sec.   63.1(c)(4)...........  Yes.                  ....................
Sec.   63.1(c)(5)...........  Yes.                  ....................
Sec.   63.1(d)..............  No..................  Section reserved.
Sec.   63.1(e)..............  Yes.                  ....................
Sec.   63.2.................  Yes.................  Except definition of
                                                     major source is
                                                     unique for this
                                                     source category and
                                                     there are
                                                     additional
                                                     definitions in
                                                     subpart HHH.
Sec.   63.3(a) through (c)..  Yes.                  ....................
Sec.   63.4(a)(1)...........  Yes.................
Sec.   63.4(a)(2)...........  Yes.................
Sec.   63.4(a)(3)...........  No..................  Section reserved.
Sec.   63.4(a)(4)...........  No..................  Section reserved.
Sec.   63.4(a)(5)...........  No..................  Section reserved.
Sec.   63.4(b)..............  Yes.                  ....................
Sec.   63.4(c)..............  Yes.                  ....................
Sec.   63.5(a)(1)...........  Yes.                  ....................
Sec.   63.5(a)(2)...........  No..................  Preconstruction
                                                     review required
                                                     only for major
                                                     sources that
                                                     commence
                                                     construction after
                                                     promulgation of the
                                                     standard.
Sec.   63.5(b)(1)...........  Yes.                  ....................
Sec.   63.5(b)(2)...........  No..................  Section reserved.
Sec.   63.5(b)(3)...........  Yes.                  ....................
Sec.   63.5(b)(4)...........  Yes.                  ....................
Sec.   63.5(b)(5)...........  No..................  Section reserved.
Sec.   63.5(b)(6)...........  Yes.                  ....................
Sec.   63.5(c)..............  No..................  Section reserved.
Sec.   63.5(d)(1)...........  Yes.                  ....................
Sec.   63.5(d)(2)...........  Yes.                  ....................
Sec.   63.5(d)(3)...........  Yes.                  ....................
Sec.   63.5(d)(4)...........  Yes.                  ....................
Sec.   63.5(e)..............  Yes.                  ....................
Sec.   63.5(f)(1)...........  Yes.                  ....................
Sec.   63.5(f)(2)...........  Yes.                  ....................
Sec.   63.6(a)..............  Yes.                  ....................
Sec.   63.6(b)(1)...........  Yes.                  ....................
Sec.   63.6(b)(2)...........  Yes.                  ....................
Sec.   63.6(b)(3)...........  Yes.                  ....................
Sec.   63.6(b)(4)...........  Yes.                  ....................
Sec.   63.6(b)(5)...........  Yes.                  ....................
Sec.   63.6(b)(6)...........  No..................  Section reserved.
Sec.   63.6(b)(7)...........  Yes.                  ....................
Sec.   63.6(c)(1)...........  Yes.                  ....................
Sec.   63.6(c)(2)...........  Yes.                  ....................
Sec.   63.6(c)(3) and (c)(4)  No..................  Section reserved.
Sec.   63.6(c)(5)...........  Yes.                  ....................
Sec.   63.6(d)..............  No..................  Section reserved.
Sec.   63.6(e)..............  Yes.                  ....................
Sec.   63.6(e)..............  Yes.................  Except as otherwise
                                                     specified.
Sec.   63.6(e)(1)(i)........  No..................  See Sec.
                                                     63.1274(h) for
                                                     general duty
                                                     requirement.
Sec.   63.6(e)(1)(ii).......  No.                   ....................
Sec.   63.6(e)(1)(iii)......  Yes.                  ....................
Sec.   63.6(e)(2)...........  No..................  Section reserved.
Sec.   63.6(e)(3)...........  No.                   ....................
Sec.   63.6(f)(1)...........  No.                   ....................
Sec.   63.6(f)(2)...........  Yes.                  ....................
Sec.   63.6(f)(3)...........  Yes.                  ....................
Sec.   63.6(g)..............  Yes.                  ....................

Sec.   63.6(h)(1)...........  No.                   ....................
Sec.   63.6(h)(2)...........  Yes.                  ....................
Sec.   63.6(h)(3)...........  No..................  Section reserved.
Sec.   63.6(h)(4) through     Yes.                  ....................
 (h)(9).
Sec.   63.6(i)(1) through     Yes.                  ....................
 (i)(14).
Sec.   63.6(i)(15)..........  No..................  Section reserved.
Sec.   63.6(i)(16)..........  Yes.                  ....................
Sec.   63.6(j)..............  Yes.                  ....................
Sec.   63.7(a)(1)...........  Yes.                  ....................
Sec.   63.7(a)(2)...........  Yes.................  But the performance
                                                     test results must
                                                     be submitted within
                                                     180 days after the
                                                     compliance date.
Sec.   63.7(a)(3)...........  Yes.                  ....................
Sec.   63.7(a)(4)...........  Yes.                  ....................
Sec.   63.7(b)..............  Yes.                  ....................
Sec.   63.7(c)..............  Yes.                  ....................
Sec.   63.7(d)..............  Yes.                  ....................
Sec.   63.7(e)(1)...........  No.                   ....................
Sec.   63.7(e)(2)...........  Yes.                  ....................
Sec.   63.7(e)(3)...........  Yes.                  ....................
Sec.   63.7(e)(4)...........  Yes.                  ....................
Sec.   63.7(f)..............  Yes.                  ....................
Sec.   63.7(g)..............  Yes.                  ....................
Sec.   63.7(h)..............  Yes.                  ....................
Sec.   63.8(a)(1)...........  Yes.                  ....................
Sec.   63.8(a)(2)...........  Yes.                  ....................
Sec.   63.8(a)(3)...........  No..................  Section reserved.
Sec.   63.8(a)(4)...........  Yes.                  ....................
Sec.   63.8(b)(1)...........  Yes.                  ....................
Sec.   63.8(b)(2)...........  Yes.                  ....................
Sec.   63.8(b)(3)...........  Yes.                  ....................
Sec.   63.8(c)(1)...........  Yes.                  ....................
Sec.   63.8(c)(1)(i)........  No.
Sec.   63.8(c)(1)(ii).......  Yes.
Sec.   63.8(c)(1)(iii)......  No.                   ....................
Sec.   63.8(c)(2)...........  Yes.                  ....................
Sec.   63.8(c)(3)...........  Yes.                  ....................
Sec.   63.8(c)(4)...........  No.                   ....................
Sec.   63.8(c)(5) through     Yes.                  ....................
 (c)(8).
Sec.   63.8(d)(1)...........  Yes.                  ....................
Sec.   63.8(d)(2)...........  Yes.                  ....................
Sec.   63.8(d)(3)...........  Yes.................  Except for last
                                                     sentence, which
                                                     refers to an SSM
                                                     plan. SSM plans are
                                                     not required.
Sec.   63.8(e)..............  Yes.................  Subpart HHH does not
                                                     specifically
                                                     require continuous
                                                     emissions monitor
                                                     performance
                                                     evaluations,
                                                     however, the
                                                     Administrator can
                                                     request that one be
                                                     conducted.
Sec.   63.8(f)(1) through     Yes.                  ....................
 (f)(5).
Sec.   63.8(f)(6)...........  No..................  Subpart HHH does not
                                                     require continuous
                                                     emissions
                                                     monitoring.
Sec.   63.8(g)..............  No..................  Subpart HHH
                                                     specifies
                                                     continuous
                                                     monitoring system
                                                     data reduction
                                                     requirements.
Sec.   63.9(a)..............  Yes.                  ....................
Sec.   63.9(b)(1)...........  Yes.                  ....................
Sec.   63.9(b)(2)...........  Yes.................  Existing sources are
                                                     given 1 year
                                                     (rather than 120
                                                     days) to submit
                                                     this notification.
Sec.   63.9(b)(3)...........  No..................  Section reserved.
Sec.   63.9(b)(4)...........  Yes.                  ....................
Sec.   63.9(b)(5)...........  Yes.                  ....................
Sec.   63.9(c)..............  Yes.                  ....................
Sec.   63.9(d)..............  Yes.                  ....................
Sec.   63.9(e)..............  Yes.                  ....................
Sec.   63.9(f)..............  Yes.                  ....................
Sec.   63.9(g)..............  Yes.                  ....................
Sec.   63.9(h)(1) through     Yes.                  ....................
 (h)(3).
Sec.   63.9(h)(4)...........  No..................  Section reserved.
Sec.   63.9(h)(5) and (h)(6)  Yes.                  ....................
Sec.   63.9(i)..............  Yes.                  ....................
Sec.   63.9(j)..............  Yes.                  ....................
Sec.   63.10(a).............  Yes.                  ....................
Sec.   63.10(b)(1)..........  Yes.................  Section
                                                     63.1284(b)(1)
                                                     requires sources to
                                                     maintain the most
                                                     recent 12 months of
                                                     data on-site and
                                                     allows offsite
                                                     storage for the
                                                     remaining 4 years
                                                     of data.
Sec.   63.10(b)(2)..........  Yes.                  ....................

Sec.   63.10(b)(2)(i).......  No.                   ....................
Sec.   63.10(b)(2)(ii)......  No..................  See Sec.
                                                     63.1284(f) for
                                                     recordkeeping of
                                                     (1) occurrence and
                                                     duration and (2)
                                                     actions taken
                                                     during malfunction.
Sec.   63.10(b)(2)(iii).....  Yes.                  ....................
Sec.   63.10(b)(2)(iv)        No.                   ....................
 through (b)(2)(v).
Sec.   63.10(b)(2)(vi)        Yes.                  ....................
 through (b)(2)(xiv).
Sec.   63.10(b)(3)..........  No.                   ....................
Sec.   63.10(c)(1)..........  Yes.                  ....................
Sec.   63.10(c)(2) through    No..................  Sections reserved.
 (c)(4).
Sec.   63.10(c)(5) through    Yes.                  ....................
 (c)(8).
Sec.   63.10(c)(9)..........  No..................  Section reserved.
Sec.   63.10(c)(10) through   No..................  See Sec.
 (c)(11).                                            63.1284(f) for
                                                     recordkeeping of
                                                     malfunctions.
Sec.   63.10(c)(12) through   Yes.                  ....................
 (c)(14).
Sec.   63.10(c)(15).........  No.                   ....................
Sec.   63.10(d)(1)..........  Yes.                  ....................
Sec.   63.10(d)(2)..........  Yes.                  ....................
Sec.   63.10(d)(3)..........  Yes.                  ....................
Sec.   63.10(d)(4)..........  Yes.                  ....................
Sec.   63.10(d)(5)..........  No..................  See Sec.
                                                     63.1285(b)(6) for
                                                     reporting of
                                                     malfunctions.
Sec.   63.10(e)(1)..........  Yes.                  ....................
Sec.   63.10(e)(2)..........  Yes.                  ....................
Sec.   63.10(e)(3)(i).......  Yes.................  Subpart HHH requires
                                                     major sources to
                                                     submit Periodic
                                                     Reports semi-
                                                     annually.
Sec.   63.10(e)(3)(i)(A)....  Yes.                  ....................
Sec.   63.10(e)(3)(i)(B)....  Yes.                  ....................
Sec.   63.10(e)(3)(i)(C)....  No..................  Section reserved.
Sec.   63.10(e)(3)(i)(D)....  Yes.                  ....................
Sec.   63.10(e)(3)(ii)        Yes.                  ....................
 through (e)(3)(viii).
Sec.   63.10(f).............  Yes.                  ....................
Sec.   63.11(a) through (e).  Yes.                  ....................
Sec.   63.12(a) through (c).  Yes.                  ....................
Sec.   63.13(a) through (c).  Yes.                  ....................
Sec.   63.14(a) through (q).  Yes.                  ....................
Sec.   63.15(a) and (b).....  Yes.                  ....................
------------------------------------------------------------------------

[FR Doc. 2012-16806 Filed 8-15-12; 8:45 am]
BILLING CODE 6560-50-P